# Survey on forced oscillations in power system

- 1.2k Downloads
- 3 Citations

## Abstract

The oscillations in a power system can be categorized into free oscillations and forced oscillations. Many algorithms have been developed to estimate the modes of free oscillations in a power system. Recently, forced oscillations have caught many researchers’ attentions. Techniques are proposed to detect forced oscillations and locate their sources. In addition, forced oscillations may have a negative impact on the estimation of mode and mode-shape if they are not properly accounted for. To improve the power system reliability and dynamic properties, it is important to first distinguish forced oscillations from free oscillations and then locate the sources of forced oscillations in a timely manner. The negative impact of forced oscillation can be mitigated when they are detected and located. This paper provides an overview of the analysis technique of forced oscillations in power systems. In addition, some future opportunities are discussed in forced oscillation studies.

## Keywords

Forced oscillation Self-coherence Phasor measurement unit Electromechanical oscillations## 1 Introduction

One of the major threats to the security and stability of power systems is low-frequency oscillations [1, 2]. If oscillations are negatively damped, the magnitude of oscillations will grow and consequently cause system breakup and power outages. These are known as the small signal stability problems. Analysis of low-frequency oscillations is critical to the reliable operation of power systems. Based on the cause of oscillations, low-frequency electromechanical oscillations can be categorized into two main categories: free oscillations and forced oscillations. Free oscillations result from the natural interaction among dynamic devices. In contrast, forced oscillations refer to system responses to an external periodic perturbation.

Methods to mitigate the free oscillations are totally different than those for forced oscillations. Power system stabilizer (PSS) is a simple and economical method to suppress the oscillations by increasing the damping ratio. Control strategies can be utilized to rectify lightly-damped or undamped free oscillations. In contrast, removing the source of oscillations can be considered a remedy for forced oscillations.

It is very important to get the accurate information about oscillations because it can help operate a power system reliably at its full capacity. To study free oscillations, modal properties of power systems provide principal information for control strategies. Basically, there are two approaches for estimating power system modes: the component-based approaches and the measurement-based approaches. Stable modes of the power system can guarantee that free oscillations will dampen. On the other hand, undamped modes can be hazardous for the power system. In past decades, remarkable efforts have been devoted to estimate the modal properties of a power system using component-based approaches and measurement-based approaches [3]. Numerous measurement-based modal analysis algorithms have been proposed. Valuable overviews of existing algorithms are presented in [4, 5].

With the application of phasor measurement unit (PMU) data, it is possible to record and monitor systems’ dynamic behaviors. PMU data have been widely used to study the forced and free oscillations because they have a typical sampling rate of 30-60 samples/second and are well synchronized with global positioning system (GPS) clock.

One of the primary identifications of forced oscillations goes back to 1966 [6]. Forced oscillations can be caused by an external periodic disturbance or a mistuned generator controller. Forced oscillations are reported as a sinusoidal signal originated at generator sites [7]. The resonance between forced oscillation and electromechanical mode can cause system break-down [8]. Sustained oscillation is imposed in power systems when forced oscillations exist around a well-damped mode. Forced oscillations have been observed several times in the western North American Power System (wNAPS) with a frequency range of 0.2 Hz to 2 Hz which, in some cases, caused moderately hazardous situations [9]. To analyze forced oscillations, one should initially study the source of forced oscillations in isolated and large systems. Identifying the possible sources of forced oscillations can help to attain a more reliable power system. To improve the power systems reliability and stability, detecting and locating the forced oscillations is important. In addition, amplitude, frequency and phase of forced oscillations are of interest.

- 1)
To provide a comprehensive overview of existing methods to detect and locate forced oscillations and study the impacts of forced oscillations in power systems.

- 2)
To identify the key open problems for detecting the forced oscillations.

- 3)
To introduce future opportunities that can be possible paths to study the forced oscillations.

Therefore, a clear picture of strength and challenges of the existing methods to study forced oscillations is provided.

The paper is organized as follows. In Sect. 2, sources of forced oscillations are discussed. Section 3 provides an overview of existing methods to detect the forced oscillations. Oscillation classification methods are discussed in Sect. 4. Section 5 provides an overview of existing methods to locate forced oscillations. In Sect. 6, the impacts of forced oscillations on estimating electromechanical modes are reviewed. Future opportunities for studying forced oscillations are discussed in Sect. 7. Conclusions are drawn in Sect. 8.

## 2 Source of forced oscillations

It is important to locate the sources of forced oscillations because once their sources are identified, the forced oscillations can be mitigated by removing the sources. However, it is very challenging to locate the real disturbance source due to the complexity of a power system.

Forced oscillations have been observed and reported in power grids. One of the earliest studies on forced oscillations dates back to 1966 when Ness studied the responses of power systems to cyclic load variations [6]. To study the situation where frequency of forced oscillations is close to natural frequency of generator rotor oscillations, Vournas et al. introduced cyclic load, low-speed diesel generators and wind turbines, which is driving the synchronous generator, as possible sources of forced oscillations [8]. The Pinneilo et al. cited the nuclear accelerator as source of forced oscillations [10]. Power systems behaviors for steady state analysis, dynamic simulation and controller design have been considered in [11], where steel plants, nuclear accelerators, cement mills and aluminum processing plants are cited as sources of forced oscillations. Putting limit on generator field voltage in a single-machine infinite-bus system can induce stable limit cycle that consequently is a cause of forced oscillations via Hopf bifurcation [12]. To analyze the characteristics of regulating systems, the electro-hydraulic regulating system of a steam turbine is mentioned as a source of forced oscillations in [13]. Poorly designed PSS can induce amplification of forced oscillations [14]. Authors of [14] noted that traditional PSS control loops introduce additional poles and zeros which can resonate with cyclic inputs. To avoid possible resonance, authors in [14] provided adjusted PSS design. Rostamkolai et al. proposed that the impact of cyclic load, which is caused by a synchrotron in the power systems, is significant, especially in resonance situations with electromechanical oscillations [15]. In [16], incomplete islanding has been cited as a possible source of forced oscillations in the power system. To simulate the forced oscillations, mechanical power of a generator is modulated with a sinusoidal signal in [17]. These studies showed that forced oscillations may come from different sources.

- 1)
Before the year 2000, there are 7 papers studying causes of forced oscillations, i.e., No. 1-7: 6 of them used simulation data and they are focused on the load side, i.e., No. 1-5, 7.

- 2)
After the year 2000, 20 events have been reported, i.e., No. 8-27: ➀ 18 oscillations are recorded using PMU data, i.e., No. 1, 2, 12-27; ➁ 14 oscillation studies are related to generators, i.e., No. 8, 9, 12-21, 23, 27; ➂ 4 oscillation events are associated with wind power plants, i.e., No. 12, 17, 19, 21; ➃ 4 oscillation studies are associated with hydro power plants, i.e., No. 11, 15, 20, 22.

- 3)
Of all the events, the control actions of 5 events involve the reduction of asset usage, i.e., No. 6, 9, 10, 12, 21.

- 4)13 oscillations have the records on their time durations:
- a.
4 oscillations last for more than 1 hour, i.e., No. 15, 17, 21, 27.

- b.
5 oscillations last for more than 10 minutes but less than 1 hour, i.e., No. 6, 10, 12, 13, 24.

- c.
4 oscillations last for less than 10 minutes, i.e., No. 9, 14, 18, 23.

- a.
- 5)9 oscillations have the records on their oscillation amplitudes in MW or MVA:
- a.
The smallest peak-peak oscillation magnitude is 10 MVA, i.e., No 15.

- b.
The largest peak-peak oscillation magnitude is 280 MW, i.e., No. 6.

- c.
5 oscillations have their magnitude larger than 100 MW, i.e., No. 6, 9, 10, 13, 16.

- d.
4 oscillations have their magnitude less than 40 MW, i.e., No. 7, 14, 15, 22.

- a.
- 6)19 oscillations have the records on their oscillation frequency in Hz. According to [46], they are categorized as follows:
- a.
2 oscillations between (0.01-0.15 Hz), i.e., No. 16, 22.

- b.
7 oscillations between (0.15-1.0 Hz), i.e., No. 7, 9, 11, 14, 15, 16, 23.

- c.
7 oscillations between, i.e., (1.0–5.0 Hz), i.e., No. 6, 10, 18, 20, 21, 25, 26.

- d.
4 oscillations between (5.0-14.0 Hz), i.e., No. 12, 17, 19, 24.

- a.
- 7)19 oscillations have the records on their location sources:
- a.
9 oscillations are recorded in Eastern interconnection, i.e., No. 6, 12-14, 16, 18, 19, 22, 24.

- b.
8 oscillations are recorded in Western interconnection data, i.e., No. 9, 10, 15, 17, 23, 25-27.

- a.

Forced oscillations sorted by their reported years

No. | Ref. | Year | Reported source | Frequency (Hz) | Control action | Duration | Location | Magnitude | Signal |
---|---|---|---|---|---|---|---|---|---|

1 | [6] | 1966 | Cyclic load | N/A | N/A | N/A | Simulation studies | N/A | N/A |

2 | [10] | 1971 | Nuclear accelerator | N/A | N/A | N/A | Simulation studies | N/A | N/A |

3 | [11] | 1988 | Steel plant, nuclear accelerator, cement mills and aluminum processing | N/A | N/A | N/A | Simulation studies | N/A | N/A |

4 | [14] | 1990 | PSS in a generator | N/A | N/A | N/A | Simulation studies | N/A | N/A |

5 | [8] | 1991 | Cyclic load, low speed diesel generators and wind turbines | N/A | N/A | N/A | Simulation Studies | N/A | N/A |

6 | [18] | Jun. 1992 | Failure of an insulator, line switching and system re-configuration (Hopf bifurcation) | 1.0 | Reduce the MW of a generation => stop oscillation | 37 min | Rush Island (East) | 280 MW | Real power |

7 | [15] | 1994 | Synchrotron | 0.3–7.5 | N/A | N/A | Simulation studies | 20 MW | N/A |

8 | [12] | 2005 | Limits on PSS and AVR of a generator | N/A | N/A | N/A | Simulation Studies | N/A | N/A |

9 | Nov. 2005 | Steam extractor valve at a Co-Gen plant at Nova Joffre in Alberta | 0.28 | Reduce the steam supply to the industrial process | 6 min | Alberta, BPA, CAISO (West) | 20 MW (Source) 200 MW (COI) | Real power | |

10 | [21] | Jan. 2008 | Pacific DC intertie oscillations | 4.0 | Ramp down the PDCI power flow to zero | 55 min | BPA, SCE, CAISO West) | 150 MW 200 MVA | Real and reactive power |

11 | [13] | 2010 | Electro-hydraulic regulating system of steam turbine (PSS) of a generator | 0.2–2.5 | N/A | N/A | Simulation Studies | N/A | N/A |

12 | April 2011 | Two types of wind turbines during high wind output, wind power plant | 13.33 | Curtail wind during high wind | 25 min | OG&E, Oklahoma (Eastern) | 5.1 kV | Voltage magnitude | |

13 | [21] | 2011 | Lower a voltage setting in a nuclear generator (voltage setting issue) | N/A | Increase the voltage control back to normal setup | 12 min | Dominion (Eastern) | 250 MW | Real power voltage magnitude |

14 | [21] | Before 2012 | Malfunction of the governor controller at a large coal-fired generating plant during tests | 0.285 | N/A | 2.5 min | MISO (Eastern) | 40 MW | Real power |

15 | [23] | Summer 2013 | Hydro generator (vortex control, rough zone during startup/shut down) | 0.38 | Move the hydro generation out of its rough zone | Several hours | WECC | 10 MVA | Apparent power |

16 | [24] | April 2013 | A generator | 0.12 | N/A | N/A | NE ISO (Eastern) | 100 MW | Real power |

17 | [25] | April 2013 | Wind plant | 13 | N/A | Several hours | BPA (West) | N/A | Real power |

18 | May 2013 | AVR controller malfunctions of a generator | 1.25 | Turned off excitation system | 2 min | NYISO (Eastern) | N/A | Voltage magnitude, power | |

19 | [21] | Before 2014 | A controller of a wind plant | 14 | Upgrad the plant control by the manufacturer | N/A | BPA (Eastern) | N/A | Real and reactive power |

20 | [21] | Feb. 2014 | A faulty control card for a hydro power plant | 1.80 | Replace the faulty control card | N/A | ERCOT | N/A | Frequency |

21 | [21] | 2014 | Controller setting of a wind plant | 3.3 | Reduce wind power plant outputs (later, restore controller settings) | 17 hours | ERCOT | N/A | NA |

22 | [24] | Feb. 2014 | N/A | 0.14 | N/A | N/A | NE ISO (Eastern) | 20 MW | Real power |

23 | [27] | Oct. 2014 | Surging water vortex on turbine at a hydro generator | 0.33 | N/A | >1 min | BPA (Western) | N/A | Real, reactive power |

24 | [21] | Before 2015 | Load induced oscillation (a refinery) | 4.62–5.0 | N/A (Use IEEE 519 standard) | 15 min | OG&E (Oklahoma, Eastern) | N/A | Voltage, magnitude |

25 | [24] | Mar. 2015 | N/A | 1.48 | N/A | N/A | BPA (West) | N/A | |

26 | [24] | Nov. 2015 | N/A | 1.17 | N/A | N/A | BPA (West) | N/A | |

27 | [27] | Oct. 2015 | Interaction between an under-excited limiter and a PSS of a generator (Dalles) | >1 | Move the units out of the under excitation area | >60 min | Dalles, BPA (West) | N/A | Real, reactive power |

It can be observed that both cyclic load and generator control equipment (GCE) were reported as the sources of forced oscillations. In addition, in the recent years, GCEs such as PSS and automatic voltage regulators (AVR) are reported more often as the sources of forced oscillations. In other words, the sources of the forced oscillations mainly are located on the generator sides. This prior information suggests that to detect and locate forced oscillations, one may want to place more attentions on the generation sides.

## 3 Oscillation detection methods

*A*is the sinusoidal signal which represents forced oscillations;

*z*

_{ t }is the additive noise [50, 51];

*N*is the total number of samples.

Therefore, the challenge is to detect the sinusoidal covered with ambient noise.

*x*

_{ t }for the 30 seconds, 1 hour and 24 hours of data consequently when the window length is 128, Hamming windows, and overlapping is 50%. As can be seen in Fig. 2, there are four peaks. The peaks at 0.4 HZ, 3 Hz and 9 Hz represent the modes from the ambient noise. The peak at 5 Hz shows forced oscillations. This peak can be smaller for forced oscillations with lower SNR. However, Fig. 3 illustrates just two peaks, one at 0.4 Hz (i.e., mode from the ambient noise) and another at 5 Hz with high amplitude (i.e., the forced oscillations). Figure 4 clearly shows only one peak at 5 Hz with a very high amplitude. This observation indicates that there is a direct relationship between the magnitude of forced oscillation and time, which can be used to distinguish the different types of oscillations. Using PSD to detect the forced oscillation, there is a trade-off between time and the detection accuracy. Because it is important to detect the forced oscillations in a timely manner, using PSD to detect the oscillations is not the best practice. Therefore, there is a need for a method that can distinguish different types of oscillations in a timely manner.

*t*is 6.0 s. For the 60 minutes of date, Fig. 5 shows the self-coherence spectrum in a heat map where oscillations frequency is 8 Hz.

*α*= 1%. As it can be seen the only point that exceeds the threshold is at frequency of 8 Hz. However, there is question of how quickly this method can detect oscillations. To extend the coherence method, Ref [31] applied coherence method to multiple-channel data. It shows that using multiple-channel method can increase detection rates. To inspect the performance of the coherence method, different algorithms such as the Welch algorithm, Capon algorithm and autoregressive moving average (ARMA) algorithm are used to estimate coherence spectra. Moreover, the performances of three algorithms are compared. However, there is a question on applicability of the method when both forced and free oscillations exist in the system. In [23], covariance-driven stochastic subspace identification (SSI-COV) [32] was applied to detect the forced oscillations. This method can simultaneously detect forced oscillations while estimating system modes. The authors studied the effects of forced oscillations on the local modes and inter-area modes. However, proposed method failed to distinguish forced oscillations from free oscillations.

## 4 Oscillation classification methods

Oscillations classification is very important to the reliable operation of power systems because control strategy for suppressing different types of oscillations can be significantly different. Using support vector machine (SVM), [33] proposed a method that can classify two different types of oscillations based on feature extraction. Basically, increasing amplitude of free oscillations is used to distinguish it from forced oscillations. In this case, algorithm accuracy has direct relationship with envelope size. Thus, there is a question of whether this algorithm can work in real-time scenarios. Reference [34] proposed unique mathematical models for forced and free oscillations. In addition, they showed that the responses of the system to forced oscillations differs from those of free oscillations. Based on noise response and harmonic nature of oscillations, the authors proposed a method to distinguish forced oscillations from free oscillations. However, there is question of how to separate the pure sinusoid from noise in both cases (free and forced oscillations) and the effects of this separation on algorithm accuracy should be considered. In addition, it is important to evaluate the performance of proposed method when forced oscillations exist at a system’s mode frequency.

Modes of two-area model

Mode index | Frequency (Hz) | Damping ratio (%) |
---|---|---|

1 | 0.53 | 7.6 |

2 | 1.14 | 3.4 |

3 | 1.18 | 3.5 |

*α*

_{S}indicates the ratio of PSD between two different channels when oscillations exist where

*α*

_{N}indicates the ratio of PSD of two different channels when oscillations does not exist.

As it can be seen in Table 3, *α* _{S} and *α* _{N} are very close for case 1 so it can be considered a natural oscillation. In addition, the PSD ratios at 2 Hz are NOT equal which indicates that forced oscillations exist. However, if forced oscillations’ frequencies are close to the mode frequency of the system (i.e. 1.14 and 0.53 Hz) as in case 3 and 4, the PSD ratios are close to each other. In other words, the spectral approach [34] is not effective when forced oscillations exist at system’s mode frequency.

Wang et al. [36] introduced three different mathematical models for weakly damped oscillations, limit cycle and forced oscillation. Using Kurtosis estimation and PSD estimation, they proposed an algorithm which can distinguish these oscillations from each other. Authors of [36] used the standard deviation of PSD as a metric to detect forced oscillations. However, this method just has off-line application. To get the accurate PSD estimation for distinguishing oscillations, as Figs. 2, 3 and 4 illustrated, a reasonable amount of time required. In addition, this method may not be effective for oscillations with small signal-to-noise ratio (SNR).

As it can be seen, forced oscillations play a critical role in system performance and they can cause catastrophic events [1, 2]. Therefore, to increase the reliability of power systems, it is important to detect and distinguish forced oscillations and free oscillations. A robust method which can distinguish forced oscillations from free oscillations even when forced oscillations exist at system’s mode frequency is needed. Extracting the unique features of forced oscillations can be a possible solution. However, the unknown nature of forced oscillation sources has made it hard to model them mathematically.

## 5 Oscillation source locating methods

In order to suppress forced oscillations and mitigate their impacts, a robust method for locating the sources of forced oscillations is needed. Fundamentally, forced oscillations can be caused by an external perturbation in generator sites.

PMU data reflects the behaviors of the model at 30 to 60 samples/s. They basically are phasor measurements synchronized with GPS clock. PMU data have been widely used in power systems analysis [5, 37]. In [38], the authors proposed a new application of PMU data. PMU data have been utilized to locate the sites of disturbance sources. A hybrid dynamic simulation method is used to locate the forced oscillations. Basically, the idea is to replace part of dynamic states and algebraic variables with measurements, which in this case is PMU data, and run a power system model. Mismatch between simulation data and PMU data indicates the location of forced oscillations. Although the method shows promising results, it is only applicable in post-fault analysis studies. Using dynamic state variables, an energy based method is applied to locate the source of forced oscillations in [39, 40]. Although both methods shows promising results, they require detailed information of the model which makes the applicability and the validity of these methods unclear. In [41], after visually detecting oscillations, Prony analysis is applied to extract the oscillations’ characteristic (i.e. frequency, Magnitude, Phase and Damping ratio) and consequently damping torque of the generator is used to locate the source of forced oscillations. The authors detected the forced oscillations at a frequency of 0.56 Hz which is close to the mode frequency and the source of oscillation is not discussed in the paper. Thus, it is interesting to study the performance of this method for two different scenarios: forced oscillations with very small frequency (i.e. 0.13) imposed on a generator and applicability of method on a large power system. Reference [42] analyzed the forced oscillations at 0.7475 Hz based on extended equal-area criterion (EEAC) theory and then located the forced oscillations in two steps: ➀ identify the disturbance cluster by comparing steady phase relationships; ➁ locate the disturbance source by comparing transient response trajectories phase of observation points in identified disturbance clusters. However, the applicability of the proposed method for forced oscillations with high frequency (i.e. 14 Hz) is questionable. Reference [43] studied the differences between the free and forced oscillations in terms of their energy conversions. Considering the cyclical load disturbance as a cause of forced oscillations, an increase of potential power is proposed that can be used to locate the disturbance source of forced oscillations. As it is listed in Sect. 2, the cyclical load disturbance is one of the possible sources of forced oscillations besides malfunctioning generators, PSS limits on generators, nuclear accelerators and etc. So, it is important to evaluate the performance of the proposed method in [43] for different sources (especially when forced oscillations’ frequencies are considerably small). Reference [44] proposed a new approach based on power dissipation to locate the disturbance source of forced oscillations. As can be seen in Table 1 from the reported event, the forced oscillation frequencies can be expected to be between 0.12 Hz to 14 Hz, and it is not necessarily equal to the natural oscillations’ mode frequencies. Thus, the performance of the proposed method is questionable when forced oscillation frequencies are not equal to the system’s mode frequency. In [23], it was proposed that the location of forced oscillations can be determined using mode shape magnitude when there is not a strong resonant effect. However, in the case of resonance when frequency of forced oscillations is close to that of system modes, mode shape estimation may not be useful to locate the source of forced oscillations.

While aforementioned methods were able to locate the forced oscillations to some degree, there is a need to develop a method which can distinguish forced oscillations from free oscillations and locate the source of the forced oscillations under different scenarios: ➀ forced oscillations with different frequency ranges (i.e. 0.12 Hz to 14 Hz); ➁ forced oscillation in a large and complex system; ➂ forced oscillations with low SNRs; ➃ forced oscillations imposed by different causes (i.e. Cyclical load, generator malfunctioning, etc).

## 6 Effects of forced oscillations on mode estimation algorithms

Modes and mode shapes are critical parameters describing free oscillations. Mode describes the system’s oscillation frequency and damping behaviors while mode shape states the relative participation of state variables in particular mode [45]. Electromechanical modes in power systems are analyzed through many parametric methods.

Basically there are two approaches for estimating power system modes: simulation model-based approach [46] and measurement-based approach. Regarding model-based approaches, the challenge is to obtain an accurate dynamic model for real-time power system operating conditions. The task is even more difficult for large-scale power systems. The difference between real system responses and simulation model responses during a real-world event indicates the model’s deficiency, which can cause conservative operation and reduce asset utilization. For instance, an initial effort was made to build a component based model for simulating the Western Electricity Coordinating Council (WECC) [1]. The study shows that the simulated system responses do not match the field measurement data. Simulation results and measurement results matched only after extensive modification and calibration. In contrast, the measurement-based approach requires less effort than the model-based approach. In addition, measurement-based approaches can update the mode estimation based on incoming measurement data. Based on measurement approaches, modes of a system can be identified using ambient data, ring-down data and probing signals. Therefore, measurement-based methods have certain advantages over the model-based eigenvalue analysis in monitoring real-time power oscillations. An overview of mode estimation algorithms is given in [4, 5].

To estimate the modal properties of a system, mode-meter algorithms are constantly processing PMU data and estimating frequency, damping ratio and shape of a mode from ambient data. Forced oscillations impose a challenge on mode estimation algorithms [5, 47]. To estimate the mode accurately, it is important to study the impact of forced oscillations on mode estimation. Studying both simulation data and real-time PMU data, authors in [48], pointed out that damping estimate can be comprised when forced oscillations exist. Vanfretti et al. showed that the impact of forced oscillation on damping estimate depends on its location with respect to an inter-area mode [49]. It has been shown that estimated damping ratio decreases when a forced oscillation is superimposed on the inter-area mode. However, estimated damping ratios increase when forced oscillations are close to the inter-area mode. Myers et al. showed that existence of forced oscillations can have a slight impact on mode-shape estimation only when forced oscillation frequency is close to system mode frequency [9]. Forced oscillations with frequencies far away from system mode frequencies have no noticeable impact on mode-shape estimation. In addition, Sidorov discusses the online detection of inter-area oscillations in the power systems in [52].

Properties of the electromechanical modes describe system oscillation frequency and damping behavior. Therefore, identifying forced oscillations is important because it helps mode estimation algorithms to provide more accurate information about power-system stability.

## 7 Future opportunities for studying forced oscillations

- 1)
The relation between length of data and magnitude of PSD, as it has been shown in Figs. 3, 4 and 5, can be used to distinguish different types of oscillations.

- 2)
As it has been discussed throughout the paper, coherence analysis has shown promising results in detecting the forced oscillations. However, there is still some deficiency in the proposed algorithms. Applying other algorithms and improving existing algorithms can be critical for detecting forced oscillations.

- 3)
Effects of data length on PSD estimation to detect the forced oscillations.

- 4)
Comprehensive study to reveal the advantage and disadvantage of different algorithms to estimate the coherence spectra for detecting oscillations.

- 5)
Distinguishing free and forced oscillations using their distinct features.

- 6)
Combination of coherence and self-coherence for a system to monitor the propagation of the information on oscillation and to locate the sources of forced oscillations.

- 7)
PMUs are installed throughout systems. They carry different information based on their location, so their distinct characteristics can be used to detect and locate the oscillations. For example, coherence amplitude and phase differences of PMU data can be used to locate the forced oscillation’s location.

- 8)
One of the important issues in power systems is the placement of PMUs. Because PMU data can be used to locate the disturbance source of forced oscillations, it can be a factor for designing a PMU placement algorithm. For example, some new constraints can be added to the optimization problem of PMU placement to including the considerations of locating forced oscillations.

## 8 Conclusion

This paper presented a comprehensive overview of the forced oscillations in power systems. Basically five major areas are discussed: ➀ the source of forced oscillations; ➁ detecting methods for forced oscillations; ➂ distinguishing methods of forced oscillations; ➃ locating methods for forced oscillations; ⑤ the impact of forced oscillations on power systems. In addition, future opportunities to study forced oscillations are discussed. It can be concluded that in a large power system, GCEs (such as PSS and AVR) are often reported as the sources of forced oscillations in recent years. As it has been reported, the resonance between forced oscillations and electromechanical modes can cause catastrophic events. In addition, forced oscillations in a power system have negative impacts on mode estimation algorithms. Thus, they should be detected and located in their early stage.

There is a need for a comprehensive algorithm which distinguishes forced oscillations from free oscillations and to locate the sources of forced oscillations accurately in a large and complex power system.

## Notes

### Acknowledgements

This work was supported by the funding from State University of New York.

## References

- [1]Kosterev DN, Taylor CW, Mittelstadt WA (1999) Model validation for the August 10, 1996 WSCC system outage. IEEE Trans Power Syst 14(3):967–979CrossRefGoogle Scholar
- [2]Venkatasubramanian V, Li Y (2004) Analysis of 1996 western American electric blackouts. In: Proceedings of Bulk power system dynamics and control-VI, Cortina d’Ampezzo, Italy, pp 22–27Google Scholar
- [3]Zhou N, Huang Z, Tuffner F, Jin S, Lin J, Hauer M (2010) Final project report oscillation detection and analysis [online]. uc-ciee.org/downloads/ODA_Final_Report.pdf
- [4]Trudnowski DJ, Pierre JW (2009) Overview of algorithms for estimating swing modes from measured responses. In: 2009 IEEE Power Energy Society General Meeting (PES ’09), pp 1–8Google Scholar
- [5]Vanfretti L, Dosiek L, Pierre JW et al (2011) Application of ambient analysis techniques for the estimation of electromechanical oscillations from measured PMU data in four different power systems. Eur Trans Electr Power 21(4):1640–1656CrossRefGoogle Scholar
- [6]Ness JV (1966) Response of large power systems to cyclic load variations. IEEE Power Appar Syst 7:723–727CrossRefGoogle Scholar
- [7]Follum J, Pierre JW (2013) Initial results in the detection and estimation of forced oscillations in power systems. In: Proceedings of 2013 North American Power Symposium, pp 1–6Google Scholar
- [8]Vournas C, Krassas N (1991) Analysis of forced oscillations in a multimachine power system. Control 2:443–448Google Scholar
- [9]Myers RB, Trudnowski DJ (2013) Effects of forced oscillations on spectral-based mode-shape estimation. In: Proceedings of IEEE Power Energy Society General MeetingGoogle Scholar
- [10]Pinneilo JA, Ness JEV (1971) Dynamic response of a large power system to a cyclic load produced by a nuclear accelerator. IEEE Trans Power Appar Syst 90(4):1856–1862CrossRefGoogle Scholar
- [11]Rao K (1988) Studies on power systems that are subjected to cyclic loads. IEEE Trans Power Syst 3(1):31–37CrossRefGoogle Scholar
- [12]Reddy PB, Hiskens IA (2005) Limit-induced stable limit cycles in power systems. In: Proceedings of 2005 IEEE Russia Power Tech, pp 1–5Google Scholar
- [13]Wang X, Li X, Li F (2010) Analysis on oscillation in electro-hydraulic regulating system of steam turbine and fault diagnosis based on PSOBP. Expert Syst Appl 37(5):3887–3892MathSciNetCrossRefGoogle Scholar
- [14]Magdy MA, Coowar F (1990) Frequency domain analysis of power system forced oscillations. In: IEE proceedings C (Generation, transmission and distribution), vol 137. IET Digital Library, pp 261–268Google Scholar
- [15]Rostamkolai N, Piwko R (1994) Evaluation of the impact of a large cyclic load on the LILCO power system using time simulation and frequency domain techniques. IEEE Power Syst 9(3):1–6Google Scholar
- [16]Hauer JHJ (1996) Extending the realism of planning models for the western north america power system. In: Proceedings of Symposium of Specialists in Electric Operational and Expansion PlanningGoogle Scholar
- [17]Zhou N, Dagle J (2015) Initial results in using a self-coherence method for detecting sustained oscillations. IEEE Trans Power Syst 30(1):522–530CrossRefGoogle Scholar
- [18]Kimt K, Schattlertt H, Venkatasubramanianttt V et al (1997) Methods for calculating oscillations in large power systems. IEEE Power Syst 12(4):1639–1648CrossRefGoogle Scholar
- [19]Sarmadi SAN, Venkatasubramanian V, Salazar A (2016) Analysis of November 29, 2005 western American oscillation event. IEEE Trans Power Syst 31(6):5210–5211CrossRefGoogle Scholar
- [20]Venkatasubramanian MV, Carroll JR (2008) Oscillation monitoring system. In presentation at NASPI meeting, Charlotte, NCGoogle Scholar
- [21]Silverstein A (2015) Diagnosing equipment health and misoperations with PMU data, North American synchrophasor initiative (NASPI), NASPI technical report [online]. https://www.naspi.org/sites/default/files/reference_documents/14.pdf?fileID=1530
- [22]Wan YH (2013) Synchronized phasor data for analyzing wind power plant dynamic behavior and model validation. Contract 303:275–3000Google Scholar
- [23]Sarmadi SAN, Venkatasubramanian V (2015) Inter-area resonance in power systems from forced oscillations. IEEE Trans Power Syst 31(1):378–386CrossRefGoogle Scholar
- [24]Maslennikov S (2016) Locating the source of sustained oscillations. In: Presentation slide, WECC, JSIS meeting, Salt Lake CityGoogle Scholar
- [25]Zhou N (June 2013) Spectral analysis of power grid PMU data. In: DOE/OE transmission reliability program, Washington, DCGoogle Scholar
- [26]Cano EB (March 2014) NYISO case studies of system events analysis using PMU data. In: Proceedings of NASPI work group meeting, Knoxville, TNGoogle Scholar
- [27]Donahoo A (2016) Oscillation detection monitor. In: Proceedings of WECC, JSIS meeting, Salt Lake City, USAGoogle Scholar
- [28]Kay SM (1998) Fundamentals of Statistical signal processing. Prentice Hall PTR, Englewooed CliffsGoogle Scholar
- [29]Zhou N (2013) A coherence method for detecting and analyzing oscillations. In: Proceedings of IEEE Power Energy Society General Meeting, pp 1–5Google Scholar
- [30]Ghorbaniparvar M, Zhou N (2015) Bootstrap-based hypothesis test for detecting sustained oscillations. In: Proceedings of Power & Energy Society General Meeting, 2015, IEEE. pp 1–5Google Scholar
- [31]Ghorbaniparvar M, Zhou N, Li X (2016) Coherence function estimation with a derivative constraint for power grid oscillation detection. In: Proceedings of 2016 IEEE Global Conference on Signal and Information Processing (GlobalSIP), pp 791–795Google Scholar
- [32]Sarmadi SAN, Venkatasubramanian V (2014) Electromechanical mode estimation using recursive adaptive stochastic subspace identification. IEEE Trans Power Syst 29(1):349–358CrossRefGoogle Scholar
- [33]Liu J, Yao W, Wen J et al (2014) Active power oscillation property classification of electric power systems based on SVM. J Appl Math. doi: 10.1155/2014/218647 Google Scholar
- [34]Xie R, Trudnowski D (2015) Distinguishing features of natural and forced oscillations. In: Proceedings of Power & Energy Society General Meeting, 2015, pp 1–5Google Scholar
- [35]Chow J (1991) Power system toolbox version 2.0: dynamic tutorial and functions. Cherry Tree Scientific Software, RR, 5Google Scholar
- [36]Wang X, Turitsyn K (2016) Data-driven diagnostics of mechanism and source of sustained oscillations. IEEE Trans Power Syst 31(5):4036–4046CrossRefGoogle Scholar
- [37]Liu G, Venkatasubramanian V (2008) Oscillation monitoring from ambient PMU measurements by frequency domain decomposition. In: Proceedings of the IEEE international symposium on circuits and systems, pp 2821–2824Google Scholar
- [38]Ma J, Zhang P, Fu HJ et al (2010) Application of phasor measurement unit on locating disturbance source for low-frequency oscillation. IEEE Trans Smart Grid 1(3):340–346CrossRefGoogle Scholar
- [39]Chen L, Min Y, Hu W (2013) An energy-based method for location of power system oscillation source. IEEE Trans Power Syst 28(2):828–836CrossRefGoogle Scholar
- [40]Ying L, Chen S, Feng L (2012) An energy-based methodology for locating the source of forced oscillations in power systems. In: Proceedings of 2012 IEEE international conference on power syst. technol. (POWERCON), pp 1–6Google Scholar
- [41]Gao Y, Liu D, Huang G et al (2012) Locating method of disturbance source of forced power oscillation based on prony anyasis. In: Proceedings of China international conference on electricity distribution, pp 1–4Google Scholar
- [42]Li Z, Fang Y, Li W et al (2012) Forced power oscillation analysis based on EEAC theory. In: 2012 Asia-Pacific Symposium on Electromagnetic compatibility (APEMC). IEEE, pp 833–836Google Scholar
- [43]Yu Y, Min Y, Chen L et al (2011) The disturbance source identification of forced power oscillation caused by continuous cyclical load. In: Proceedings of DRPT 2011–2011 4th international conference on electr. util. deregul. restruct. power technol., pp 308–313Google Scholar
- [44]Hu W, Lin T, Gao Y et al (2011) Disturbance source location of forced power oscillation in regional power grid. In: Proceedings of the 2011 IEEE power eng. autom. conf. (PEAM 2011), pp 363–366Google Scholar
- [45]Zhou N, Huang Z, Dosiek L et al (2009) Electromechanical mode shape estimation based on transfer function identification using PMU measurements. In: Proceedings of Power & Energy Society General Meeting, pp 1–7Google Scholar
- [46]Kundur P (1994) Power system stability and control. McGraw-Hill, New YorkGoogle Scholar
- [47]Vanfretti L, Bengtsson S, Aarstrand VH et al (2012) Applications of spectral analysis techniques for estimating the Nordic grid’s low frequency electromechanical oscillations. IFAC Proc Vol 45(16): 1001–1006CrossRefGoogle Scholar
- [48]Vanfretti L, Bengtsson S, Peric VS et al (2013) Spectral estimation of low-frequency oscillations in the Nordic grid using ambient synchrophasor data under the presence of forced oscillations. In: Proceedings of 2013 IEEE grenoble conf. PowerTech, POWERTECH, pp 1–6Google Scholar
- [49]Vanfretti L, Bengtsson S, Peric VS et al (2012) Effects of forced oscillations in power system damping estimation. In: Proceedings of the IEEE int. work. appl. meas. power syst. (AMPS 2012), pp 59–64Google Scholar
- [50]Jabbar M, Ghorbaniparvar H (2014) Determination of volatile components in black cardamom with gas chromatography-mass spectrometry and chemometric resolution. Int J Eng Res Technol 3(11)Google Scholar
- [51]Jabbar M, Ghorbaniparvar H (2014) Use of GC-MS combined with resolution methods to characterize and to compare the essential oil components of green and bleached cardamom. IJRCE 5Google Scholar
- [52]Sidorov DN, Grishin YA, Šmádl V (2010) On-line detection of inter-area oscillations using forgetting approach for power systems monitoring. In: Proceedings of 2010 The 2nd International Conference on Computer and Automation Engineering, Singapore, pp 292–295Google Scholar

## Copyright information

**Open Access**This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.