# Building a Digital Wind Farm

## Abstract

The purpose of this paper is to provide a high level, holistic overview of the work being undertaken in the wind energy industry. It summarises the main techniques used to simulate both aerodynamic and structural issues associated with wind turbines and farms. The motivation behind this paper is to provide new researchers with an outlook of the modelling and simulation landscape, whilst highlighting the trends and direction research is taking. Each section summarises an individual area of simulation and modelling, covering the important historical research findings and a comprehensive analysis of recent work. This segregated approach emphasises the key components of wind energy. Topics range in geometric scales and detail, ranging from atmospheric boundary layer modelling, to fatigue and fracture in the turbine blades. More recent studies have begun to combine a range of scales and physics to better approximate real systems and provide higher fidelity and accurate analyses to manufacturers and companies. This paper shows a clear trend towards coupling both scales and physics into singular models utilising high performance computing system.

## Keywords

Wind energy Simulation Modelling Aerodynamics Fluid–structure interaction## 1 Introduction

With an ever growing population size and the improvement in living standards, the demand and consumption of energy is only going to escalate. Considering the surge in power consumption in combination with growing concerns about the finite nature of fossil fuels and the impact they can have on the climate, there has been a concerted effort from governments to encourage development and integration of more renewable sources of energy. This push has come through social and economic policies, such as the EU 2030 climate and energy framework [1] and the US “Clean Power Plan” [2]. Along with the obvious benefits it can have for the climate, a diverse set of energy sources can provide a greater level of economic and social security against possible disruptions [3].

In 2015, renewable sources of energy covered approximately \(23\%\) of the UK’s electricity consumption and \(11\%\) of the US energy production [4]. In the UK, wind represented \(67\%\) of these sources [5], however there still requires a significant level of installation, of both onshore and offshore wind farms, to begin playing a significant role in meeting growing energy demands. The levelised cost (lifetime cost of the system divided by its total energy output) of wind power for projects starting in 2019 currently stands at approximately 99 and 107 £\(/{\mathrm{MWh}}\) for onshore and offshore projects respectively. These costs are currently only surpassed by technologies such as nuclear, 80 £\(/{\mathrm{MWh}}\) and combined coal and gas turbines, 85 £\(/{\mathrm{MWh}}\) [6].

Technological advances in material science have allowed turbine manufacturers to build taller turbines with larger rotor diameters with a minimal increase in weight and cost. These turbines are then able to cover and capture more of the energy at higher altitudes where the wind is faster and more stable over a 24 h period. As the size of turbines grows, the blades become more flexible and it becomes increasingly important to simulate and understand both the complex flow physics and structural performance of these systems.

## 2 Previous Literature Reviews

In 1998 Snel [24] produced one of the first reviews considering the simulation methodologies used to study aero elasticity in wind turbine rotors. This was soon followed by two papers in 2000 and 2002 by Akermann and Soder [25, 26], describing the history of wind turbines and the basics behind the technology. This included simple analytical approaches to modelling the wind, how turbines and turbine arrays are integrated into the network, some of the economics and siting issues and some special applications for wind turbines. Sahin [27] then provided a much more in depth review of wind as a resource and the economic factors involved in wind energy, before concluding with a current state of the market across the continents. In 2007 Joselin Herbert [28] provided a summary of wind assessment techniques and site selection methodologies, along with some general issues with components present in the turbine nacelle, such as the gearbox and generator.

A number of authors have focused on the environmental impacts of harvesting wind energy [29, 30, 31, 32]. Pryor et al. [29] analysed the effects that the changing climate can have on wind turbine technology, whilst Leung and Yang [31] and Dai et al. [32] considered the environmental effects wind turbines cause, such as noise and visual pollution as well as some of the effects they can have on animals and radio systems.

Aero elasticity and the aerodynamics of wind turbines was covered by Hansen et al. [7] in 2006, discussing structural and aerodynamic modelling of wind turbines. It covered recent models used to represent the rotor and wake aerodynamics, along with simple structural models currently used to model rotor instabilities. Then in 2011 Zhang and Huang [8] provided a more up to date collection of the work done in aero elasticity and some areas they believed should be investigated in the future. Also in 2011 Sanderse et al. [14] provided a good summary of work undertaken in the field of wake analysis using more recent CFD models developed.

In 2010 Barlas and Van Kuik [33] reported on the state of the art in rotor control. The review analysed advanced control techniques and their use for load reduction in wind turbines. Four years later in 2014, Cheng et al. [34] explored the state of the art in generators and control methods, studying the latest technologies for wind energy conversion systems, along with the general trends and future possibilities of generation modules. In 2015 Hossain and Ali [35] discussed the future direction of generation mechanisms in turbines and how they would deal with the intermittent nature of wind. In the same year Rahman et al. [36] reviewed the control methods in wind turbines, considering both active and passive control methods used to limit vibrations and noise in the structure and blades.

The use of vertical axis turbines in an offshore application has been reviewed by Borg et al. in a number of papers [37, 38, 39], which cover the aerodynamic models used, the methods of mooring the turbines and mathematical models to simulate the combination of wind and wave induced oscillations. In 2015 Benitz et al. [40] covered the hydrodynamics of offshore applications, including water wave theory, ocean physics and how these effect structures such as turbines moored at sea.

Table 1 summarises the papers mentioned in this section into specific topics. This review provides a state of the art summary of simulation methodologies used in the wind energy industry. Providing this high level summary begins to highlight the implications and relevance of each individual subcomponent of “Wind Energy” and how these components aid the design and manufacturing process in the industry.

It looks at the development of the models used to simulate both aerodynamic and structural features within the wind turbine. A review of the recent trends in wind resource and atmospheric modelling on a number of length and time scales is provided which, to the authors knowledge, has not been reported on previously.

## 3 Wind Resource Modelling

In the 1980s, as wind turbine technology was becoming more utilised, the ability to reliably and accurately predict weather conditions became more important. This in turn motivated a need to develop more accurate models and methods to predict wind speed patterns. Research led to the developments by the National Renewable Energy Laboratory (NREL), in the US, of the Wind Energy Resource Atlas of the United States [42] and the European Wind Atlas by The Technical University of Denmark [43] which describe the wind profiles over both temporal and spatial scales and are used in the initial stages of the siting process for wind farms.

The earth’s atmosphere is split up into layers, however the maximum height of a wind turbine currently stands at approximately 220 m, it is therefore only the lower portion of the atmosphere that concerns the wind industry. This lower layer is known as the troposphere, reaching approximately 12 km from the earth’s surface. This is subsequently split up into smaller regions, the Atmospheric Boundary Layer (ABL) and the free atmosphere [44].

### 3.1 ABL Modelling

Early work on ABL modelling began in the 1970s. From the 70s to late 90s the work undertaken considered 2D flow in complex terrain [45, 46, 47, 48, 49, 50]. These ranged from analytical approximations as in [48] to numerical simulations considering single, shallow hills [45, 46] and multiple hills ranging in steepness [51, 52], along with different approaches to modelling [49, 50], using a stream-function/vorticity numerical scheme, and parameter space studies [53, 54] looking at appropriate boundary conditions to generate accurate results.

In parallel to the work described above, researchers began considering Large Eddy Simulations (LES) and Reynolds Averaged Navier–Stokes (RANS) models to improve the understanding of the physics in the ABL. Deardorff [55] was one of the first to use LES in considering the stability of the ABL due to heat fluxes. Following on from the work done by Deardorff, in 1984 Moeng [56] developed a new LES model using a pseudo spectral representation of properties in the horizontal directions. Raithby [57] tested a new second order closure model using RANS on Askervein hill, an isolated area, for which experimental data was available.

At the turn of the 21st century, with increased computational power and better solution algorithms, there was an increase in the number of studies considering more complex physics involving ‘LES’ or ‘RANS’ and ‘Boundary Layer’ [58].

Extending the work done by Richards and Hoxey [54] in 1993, a number of authors concentrated on the development and validation of more accurate turbulence models and inflow parameters used in RANS simulations for flows over complex terrains [59, 60, 61, 62, 63, 64, 65, 66]. Hargreaves et al. [61, 62] concentrated on the implementation of a new *k*−\(\epsilon\) turbulence model in the commercial codes CFX and Fluent to maintain a more consistent ABL, which they suggested decayed too quickly using some of the previously developed models. Many of the studies concerned with ABL modelling [20, 60, 65, 67] used Askervein hill as a test case.

LES also played a significant role in the development of ABL modelling in the early 2000s. After initial studies in the late 1980s and 1990s considering LES [56, 68, 69, 70], a wide range of work has been done in improving the sub grid scale models of turbulence [67, 71, 72, 73]. In particular Bechmann began developing a *k*−\(\epsilon\) LES model during his PhD in 2006 [67] and subsequently developed a Hybrid RANS/LES model [20] in order to combine the added physics of the LES with the more relaxed mesh requirements near the wall/boundary of RANS. In 2011 he used the Bolund experiment to compare the results from RANS and LES simulations [74]. The Bolund experiment was developed to provide a validation case for CFD codes studying complex terrains. Extensive measurements were taken over the hill, in Denmark, which induces complex 3D flows. It was found that RANS simulations with a two equation turbulence model offered better accuracy than the LES simulations, however mean errors for speed up of flow over the hill and turbulent kinetic energy were still quite high, 10 and 22% respectively.

*k*−\(\epsilon\) turbulence model and implementation of boundary conditions for improved ABL modelling in complex terrains.

Work is being done by a number of authors [76, 77] into coupling the different scales of flow seen in the atmosphere. Mesoscale atmospheric models that capture effects down to around 1 km are being coupled to CFD simulations, particularly LES models that can simulate the smaller detail down to approximately 50 m, see Fig. 2. CFD studies struggle to incorporate all the atmospheric phenomena that mesoscale models such as the Weather Research and Forecasting Model (WRF) can, but are able to model more local effects such as hills and turbine wakes. This coupling ultimately improves the fidelity of simulations, by providing more realistic input profiles and improving the resource assessment process.

The work in coupling scales of flow is providing more realistic input profiles however, the state of the art in ABL modelling over complex terrains seems to be encased in RANS simulations with two equation closure models. Although LES can provide a more complete analysis of turbulent properties, until the accuracy and time limitations can be improved, RANS simulations will be used by both researchers and industry in modelling flows in complex terrains.

The studies described above have built a foundation for researchers interested in wind turbines. Models have begun to combine both the ABL modelling along with the interesting flow physics generated by turbines and farms. These will be described in Sect. 5.

## 4 Rotor Modelling Methods

Some of the simpler models are usually used for larger computations that are concerned with the effect wind farms can have on the ABL [85, 86, 87] and how wakes interact [88, 89, 90]. More detailed analysis requires fully resolved geometric models [91, 92, 93] that provide much more information about the loads on the turbine rotor and structure, along with better predictions about power production.

### 4.1 Blade Element Momentum Theory (BEM)

The most simple method used to predict blade loads is BEM, which is based on simple assumptions including analysing the force on the blade through control volumes and the conservation of linear and angular momentum. For a full derivation see [94].

BEM theory can provide quick, computationally cheap and reasonably accurate results [95] for steady conditions with a wake in equilibrium. The original BEM has been extended with the introduction of tip loss correction factors [96, 97]. Recently in 2016 Koh and Ng [98] provided a good comparison of accuracy between three tip loss correction models in tidal turbines. Further developments have resulted in models accounting for separation and other factors; these include dynamic inflow models [99], yaw and tilt models [100] and dynamic stall models [101]. Further descriptions of these can be found in [95].

### 4.2 Actuator Disc (AD)

The AD model is the most simplified CFD approach that can be used for turbine modelling; it is based on the one dimensional conservation of linear momentum through a control volume. The turbine blades are modelled as a porous disc that extracts energy from the upstream flow. The force exerted on the flow by the blades is distributed over the disc and is a function of the turbine thrust coefficient, found using engineering lookup tables.

Since the development of this simplified model, researchers have constantly improved it. For example, the distribution of the thrust forces can be achieved in numerous ways, from a simple uniform distribution [81, 102] over the rotor swept area to more complex fourth order polynomial approximations [103]. In 2007 and 2008 Jimenez et al. [80, 104] modelled the forces across the disc in a uniform manner, focusing on the spectral coherence of the turbulence within the Nørrekaer Enge II Windfarm. Then in 2014 Simisiroglou et al. [103] compared a uniform and polynomial distribution of thrust forces over the disc area using different turbulence models. The Lillgrund offshore wind farm, off the coast of southern Sweden provided experimental results with which to compare the numerical results. It was concluded that the polynomial distribution of forces more accurately modelled the turbine wake aerodynamics, with a better match to the experimental results.

More advanced methods have used BEM theory to add rotational effects into the flow [81, 105]. These studies represent two examples that have compared the AD method with both rotational and non rotational factors. Wu and Porté-Agel [81] in 2010 showed that in the far wake region (ten rotor diameters downstream [106]) the AD method with rotational effects showed little difference to the AD model without rotational effects. In 2013 Aubrun et al. [105] showed experimentally similar results, that in the far wake region a porous disc closely modelled three rotating blades in the level of turbulent intensity and stream wise velocity.

The AD model does not require a fine mesh resolution around the blades, which makes it computationally cheap, ideal for large domains, containing turbine arrays. In 2012 Gonzalez-Longatt et al. [107] investigated the impact of wake effects on the operation of the wind farms, considering both the short and long term effects on power output. Avila et al. [108] offered a proof of concept study to modelling CFD farms and its ABL on large computing systems. Whilst in 2013 Castellani et al. [109] and in 2015 Creech et al. [110] used the AD model with RANS and LES respectively to model offshore wind farms.

The AD model does not represent finite blades, the simplified representation of the turbine rotor means the model cannot simulate any boundary layer effects on the blades [12], and struggles to capture blade tip vortices and more complex physical phenomenon that occur in the near wake region of a turbine. However it can provide a good representation of the far wake, and is useful for computationally expensive simulations looking at larger flow scales, such as those found in the ABL. The next “step-up” for modelling the turbine is the Actuator Line Method.

### 4.3 Actuator Line (AL)

The AL method developed by Sorensen et al. [111] modelled the blades as distinct lines as shown in Fig. 3, as opposed to a disc covering the swept area. The loading on each blade can be determined through available airfoil data. Results in [111] and [12] show that there is a distinct difference in the near wake between the AD and AL method. The AL method is able to capture the tip vortices as distinct vortex tubes in the near wake region, as opposed to a sheet in AD simulations.

Studies[12, 112] have compared the AD and AL methods for modelling the wake in turbines. In 2014 Wilson et al. [112] compared the AD, AL and a fully resolved model and compared the numerical results to the NREL 5MW reference turbine. A similar study by Martinez et al. [12] in 2015, summarised the differences between the AD and AL methods and again used the NREL 5MW turbine experimental results [113] as a reference. They used a non turbulent and uniform inflow, with a turbine operating at its maximum energy extraction capabilities. The mean wake profiles for both these methods is almost indistinguishable, however the AL method creates tip and root vortices that are convected downstream. This slight difference in the way the downstream wake is formed results in two different methods of wake breakdown. The AD method results in axi-symmetric Kelvin–Helmholtz instability and roll up, whereas the AL method disrupts this symmetry with its tip and root vortices.

Many studies involving the AD and AL methods do not include the effects of the nacelle within the models, however Lu and Porté-Agel [88] used the AL method and included the effects of a nacelle by modelling it as a solid bullet shaped object, to investigate the effects of the ABL on large wind farms.

Further examples of authors using the AL method include Machefaux et al. [114] who compared the results from computational simulations with experimental results taken from the Tjaereborg wind farm in Denmark, whilst Churchfield et al. [115] simulated the Lillgrund wind farm using the LES and AL methods.

### 4.4 Actuator Surface (AS)

An advancement on the AL method is the AS approach developed by Shen et al. in 2007 [83]. The blades are represented by points distributed over a surface, representative of the blade shape, shown in Fig. 3. The distribution of forces over the blade was determined using XFOIL [116], a computer program that resolves the viscous boundary layer over a blade. The study revealed that the AS technique more accurately predicted the flow structures at the blade edges and tips.

Many studies have been conducted using the AS method. In 2007 Dobrev et al. [117] offered a Hybrid approach using BEM and the AS model in the CFD code Fluent 6.2 and found this method was suitable up to wind speeds of around 10 m/s. It fails to accurately simulate higher wind velocities because the method does not account for radial forces, which become more prevalent at higher wind speeds. In 2009 Shen et al. [118] used the AS approach to model a vertical axis wind turbine and Sibuet Watters et al. [119] compared numerical results using the AS method with experimental values from the NREL phase VI rotor. Good agreement was found between the two sets of results from high tip speed ratios, or until stall begins to occur. More recently, in 2015, Kim et al. [84] improved the AS model to remove the over prediction of the thrust and power coefficients at the hub and tip areas previously seen in AS methods.

It was found in [117, 118, 120] that although the actuator surface model goes further in accurately modelling some of the flow in the near wake, such as the structure near the blades and the root and tip vortex regions, it fails to model the flow well at high inflow speeds, when the flow is detached from the blades and the three dimensional effects, ignored in BEM theory, become more dominant.

### 4.5 Fully Resolved Models (FRM)

At the top of the hierarchy is a FRM of the turbine blades. FRMs provide more accurate predictions of the flow around blades and offer engineers more detail about the smaller scale structures and loads on the blades.

A large proportion of the work [82, 92, 121, 122, 123] undertaken using FRMs to study rotors in more detail has been carried out by the Risø National Laboratory, Wind Energy Department at the Danish Technical University. They use the EllipSys3D program, which uses a multi block finite volume approach based on the incompressible RANS equations, and makes use of the Message Passing Interface (MPI) library to run simulations in parallel.

A number of the early studies in 2002 and 2003 [82, 121, 124, 125] compared their results with experimental data taken from the comprehensive tests done by the National Renewable Energy Laboratory (NREL), in the US, on the Phase VI turbine [126]. The Phase VI is a two bladed turbine with a 10 m rotor diameter. It was encased in an 80 by 120 foot tunnel and rotated at 72 rpm.

Sorensen et al. [82] ran two configurations, one in free conditions and the other with a surrounding tunnel using a *k*−\(\omega\) SST turbulence model. It was found that the model accurately simulated the 3D flow effects on the rotor below stall conditions, however it failed to accurately predict the rotor power at higher wind speeds (>10 m/s) when the flow detached from the blade. Johansen et al. [121] ran similar models using a Detached Eddy Simulation (DES) method, finding that the DES did not improve on the results obtained using the *k*−\(\omega\) SST model.

Duque et al. [125] compared the analytical lifting line computer program, CAMRAD II, with OVERFLOW-D, a structured grid RANS solver, on the NREL Phase VI. It was found that OVERFLOW-D predicted the performance of the rotor well in stalled conditions which CAMRAD II failed to predict.

In 2003 Benjanirat and Sankar [124] studied a number of turbulence models and their accuracy at predicting forces and bending moments at the blades, using a 3D Navier Stokes program developed at Georgia Institute of Technology. In 2005 Tongchitpakdee et al. [127] used the same program to study the effects of three turbulence models at four wind speeds and four different yaw angles. Results showed that for highly separated and fully attached flows, the turbulence models used had little effect on the accuracy, however for partially separated flows they determined more sophisticated models and better mesh resolution was required, to produce higher fidelity results.

In 2005 and 2006 Schmitz et al. [15, 128] used CFX V5.6 and V5.7 respectively, which combines RANS equations and the Vortex Panel Method (VPM), in a series of studies. This method combined the ability of the RANS to model 3D effects at the blade tip and root with the VPM’s to model the convection of the vortex sheet downstream. The VPM does not suffer from numerical dissipation of vortical structures that RANS models do [129], however the flow is assumed to be fully attached to the blade.

More recently, in 2011 there were multiple studies using Finite Element Methods (FEMs) to model the incompressible Navier-Stokes equations. Bazilevs et al. [10, 11] have produced a comprehensive methodology for modelling the geometry of the turbine rotor and the aerodynamics associated with it. The study made us of quadratic Non Uniform Rational B-Splines (NURBS) to model the geometry, whilst the incompressible Navier–Stokes equations were solved using a Residual Based Variational Multiscale (RBVMS) method. This methodology has subsequently been used by Hsu et al. [9, 130], considering the capabilities of the method for large computing systems and its future in fluid structure interaction.

Takizawa et al. [131] compared two advances on the basic Deforming Spatial Domain/Stabilised Space Time model (DSD/SST) to study the NREL 5MW offshore baseline wind turbine. The DSD/SST is a FEM adapted to work with moving boundaries and interfaces [132, 133]. They compared the torques on the blades of each method to a reference value [10]. This study highlighted the numerical performance of stabilisation methods used to study loading on a turbine rotor.

In 2016 Zhou et al. [134] used ANSYS Fluent 14.0 to study the effect of different inflow conditions on the NREL phase VI wind turbine. The LES study compared the results from a number of inflow conditions: uniform, vertical linear wind shear and vertical linear wind shear with turbulence present. The conclusions showed that wind shear must be taken account of when studying both the wake and loading on the blades. It introduced cyclic loading onto the rotor not seen in the uniform inflow case, and resulted in a non symmetric, non uniform far wake structure. This is an example of a study modelling the wind resource more accurately; many studies done by the Wind Engineering and Renewable Energy Laboratory (WIRE) in Switzerland have considered the effect that atmospheric stability can have on wind farms, some of which will be discussed in Sect. 5.

#### 4.5.1 Rotor–Tower Interaction

The interaction between the tower and rotor is in its infancy with a limited number of studies. The first full 3D analysis of a down-wind turbine configuration was by Zahle et al. [92] in 2009. The upwind turbine has been looked into a greater number of times, with the first study being done by Gomez-Iradi et al. [135] in 2009, and further research undertaken since 2010 including [93, 123, 136].

The downwind configuration of the NREL phase VI turbine was studied by Zahle et al. [92], due to the recent introduction of the overset grid method into EllipSys3D. This led to better techniques to deal with the relative movement between the rotor and the tower/nacelle. The model was able to preserve the tip vortices for approximately 1D downstream before dissipating, which is believed to be a result of mesh resolution. The study further highlighted the tower shedding frequencies dependence on the rotor. The torque and thrust experienced by the blade was determined by whether it passed through a region of positive or negative vorticity shed from the tower.

Li et al. [136] again used an overset grid technique with an incompressible unsteady RANS and DES solver, in CFD-Ship-Iowa V4.5, to study the NREL phase VI at varying wind speeds and blade pitch. This study used a finite difference approach using a blended* k−* \(\omega\)/*k−* \(\epsilon\) SST turbulence model. The domain contained \(52.3\times 10^6\) grid points distributed across 2048 processors. Simulations were run by fixing the pitch and varying the wind speed and vice versa, subsequently comparing the power and thrust calculated to experimental results. The CFD simulations predicted the values well, however for more demanding wind speeds, where large separation occurs on the blades, the thrust was over predicted and the power under predicted. The DES caught fluctuations of thrust and power at similar frequencies however, in general, it under predicted the amplitudes.

Summary of papers using fully resolved models

Paper | Test case | Software | Year | CFD model | Turbulence model |
---|---|---|---|---|---|

[82] | NREL phase VI | EllipSys3D | 2002 | RANS | \(k-\omega \, SST\) |

[121] | NREL phase VI | EllipSys3D | 2002 | DES | – |

[124] | NREL phase VI | NASCART-GT | 2003 | RANS | \(B-L,S-A,k-\epsilon\) |

[125] | NREL phase VI | CAMRAD II& | 2003 | RANS | \(B-B\) |

OVERFLOW-D | |||||

NREL phase VI | CFX 5.6 & 5.7 | 2005, 2006 | RANS | \(k-\omega , k-\epsilon\) | |

+VPM | |||||

[137] | Siemens SWT-2.3 | CFX 10.0 | 2007 | RANS | \(k-\omega \, SST\) Langtry/Menter |

[122] | NREL phase VI | EllipSys3D | 2007 | RANS | \(k-\omega \, SST\) |

[135] | NREL phase VI | – | 2009 | RANS | – |

[92] | NREL phase VI | EllipSys3D | 2009 | RANS | \(k-\omega \,SST\) |

[123] | MEXICO | EllipSys3D | 2011 | RANS | \(k-\omega \, SST\) |

[138] | NREL 5MW | – | 2011 | RBVMS | – |

[93] | MEXICO | OpenFOAM | 2012 | RANS | \(k-\omega \,SST\) |

[134] | NREL phase VI | FLUENT | 2016 | LES | – |

## 5 Wind Farms

Wind turbines are usually grouped together into large arrays called farms. The power output from a wind farm is not as simple as the sum of the rated powers of all the turbines. The leading turbines extract energy from the wind resulting in a wake. This leads to a reduced power output from preceding turbines and higher unsteady loads on the rotor and tower [139]. The velocity deficit between the free stream and wake region is usually negligible after ten rotor diameters, however the turbulence intensity difference can be detected as far as 15 rotor diameters downstream [94]. For a detailed review of wind turbine wake aerodynamics, the reader is directed to Sanderse et al. [14].

There are three main sources of turbulence from a wind turbine. Firstly, atmospheric, this is caused by the roughness of the earth’s surface and the stability of the ABL. Secondly, mechanical, caused by the interaction between the flow and the turbine rotor and tower and finally, the shear layer, caused by the tip vortices breaking down into the main wake body.

Modelling wind farms is key to maximising the energy extracted from the wind and minimising the power losses due to the wake incurred downstream of the leading turbine. As the number of turbines increases, it becomes more computationally expensive to model [108]. A large number of wind farm studies [140, 141] make use of the simplified rotor models described in Sect. 4.

- 1.
Wake analysis

- 2.
Layout optimisation.

### 5.1 Wake Analysis

Wake analysis involves the study of the wake interaction models and their accuracy and application for multiple turbines under varying conditions, different layouts and inflow parameters. In 2011 Sanderse et al. [14] provided a review of wake aerodynamics for different rotor modelling techniques.

The main issue with analysing a wake model is the variability and uncertainty in collected data. Barthelmie et al. [139] studied multiple different wake models from software used for wind turbine modelling; WAsP, WakeFarm, WindFarmer and NTUA and compared them to observational results taken from Nysted and the Hors Rev wind farms in Denmark. The models were able to capture the wake widths well at 10 m/s however the author concluded that the uncertainty in the models was still too high. All the models made approximations to resolve the near and far wake. NTUA is the most sophisticated model, using RANS equations in combination with the AD method. This is suitable for industrial applications as they are computationally quick and provide good results for mean quantities in the flow field. However models based on 1st principles are required to resolve some of the finer details.

Tabib et al. [141] studied the difference between RANS and LES models in the onshore Bessaker wind farm. The models used the AL method and included the effects of terrain in the study. It was found that the RANS model does not capture the wake dynamics, including the wake decay and interference as well as the LES model.

Many studies have been undertaken using LES [85, 86, 88, 140, 143] in order to better understand and resolve the wake aerodynamics of turbine arrays and the effects large farms can have on the stability of the ABL.

Calaf et al. [85, 86] discovered that if the length of the wind farm is greater than the size of the ABL then the flow through the farm enters into a fully developed regime; in this situation the main transfer of energy comes from the vertical transport of momentum. The study used the AD model to reduce the computational time of the simulations. They studied a range of different farm layouts, turbine loading factors and initial surface roughness values to study the mean statistical data throughout the farm. A key finding was that the vertical fluxes of kinetic energy were of the same order as the power extracted by the turbines. It was further discovered that there was between a 10–15% increase in the scalar fluxes in the ABL due to the higher turbulence, induced by the turbines, and so increased turbulent diffusivity and mixing.

In 2011 Lu et al. [88] used the AL model along with LES to model a large wind farm in a stable atmospheric boundary layer. The study showed how the effects of non-uniform incoming turbulence, the Coriolis force and rotational effects from the blades lead to a skewed spatial structure in the wake with some of the turbulence being driven away from the centre. Clear asymmetric loading were seen on the blades due to the inclusion of high wind shears in the incoming flow. Lu et al. [143] further used the same model to study the effects of a large wind farm on a convective ABL. Both aligned and staggered farms were studied with different streamwise and spanwise spacings. The presence of the wind farm altered the stability of the ABL, by increasing the height of the boundary layer and magnitude of the heat flux from the surface. It is hoped studies such as these provide information that can be used in weather and climate models.

Porté-Agel et al. [140] developed a model using LES and the AD model including the rotational effects of the blades. This was compared to experimental results of a scaled wind farm test carried out in a wind tunnel. This model was then used to compare the lateral wake interaction in both aligned and staggered wind farms. The staggered setup showed much stronger wake interaction than the aligned one.

In 2015 Goit and Meyers [144] published an interesting study where the turbines where used to optimally influence the transport of momentum and energy vertically. Optimising the vertical fluxes led to increased turbulent dissipation within the farm and hence a reduced wake recovery.

Large wind farms can have big impacts on the local and global climate. A number of studies have highlighted the effects they can have on the local climate. In 2004 Baidya Roy [145] and Keith et al. [146] showed that the increased turbulence from the farms leads to increased vertical mixing of momentum and heat, which can have significant effects on the surface temperatures. Baidya Roy et al. [147] showed using a regional atmospheric modelling system [148], that under stable atmospheric conditions, there is a warming effect underneath the farm boundary layer. Wang et al. [149, 150] found results agreeing with [147] and also showed that in offhsore wind farms the opposite occurs, there is increased surface cooling.

Summary of papers simulating farms

Paper | Rotor model | CFD model | Test case | Year |
---|---|---|---|---|

[102] | AD | RANS | Sexberium | 2013 |

[89] | AD + parabolic wake model | RANS | Sexberium | 2014 |

AD | LES | – | 2010, 2011 | |

[88] | AL + BEM | LES | – | 2011 |

[115] | AL + FAST | LES | – | 2012 |

AD + R | LES | – | 2013–2016 | |

[154] | AL | LES | Lillgrund | 2013 |

AD + BEM | LES | Horns Rev, – , Lillgrund | 2015 | |

[156] | AD | LES & WRF | Lillgrund | 2015 |

### 5.2 Layout Optimisation

In order to maximise the energy output from a wind farm the positioning of individual turbines must be decided carefully. This can be considered as an optimisation problem. Optimisation problems are computationally expensive with 100 s and sometimes 1000 s of solutions considered, and the objective function depends on a range of factors that can all affect each other. Some important variables to consider during the development of the optimisation function include: initial capital costs, wind speed and direction, turbine and farm losses and operation and maintenance costs. Optimising the layout of wind farms is important in maximising the output of energy at the lowest cost, making wind energy more competitive compared to sources such as oil and gas.

In formulating the optimisation problem some assumptions and constraints have to be made. At this moment in time it is not feasible to model turbine arrays using CFD methods, so simplifications are made. A wake model developed by Jensen [157], is one of the most common models used to model the deficit and losses in turbine arrays. It assumes momentum is conserved within the wake stream and the wake expansion is linear and a function of distance from the turbine [158].

Studies have used a wide range of methods to solve the optimisation problem. Some of the first studies used genetic algorithms [159, 160, 161, 162] with a discrete computational domain. Other solution strategies have included, Monte Carlo methods [163], mathematical models [164], evolutionary algorithms [165, 166, 167], ant colony algorithms [168] and particle swarm optimisation [169, 170]. Software used in industry such as WindPro and WindFarm use heuristic methods to optimise the wind farm layout.

In studies between 1994 and 2007, the domain was discrete, with each grid square representing a set area and possible WT location. However in 2010 Kusiak and Song [165] presented one of the first studies in which the turbine location was represented by coordinates in a continuous circular computational domain. The study assumed a fixed number of turbines with any two being separated by at least four rotor diameters. A Weibull distribution was used to approximate the wind speed at the hub height and an evolutionary algorithm was used to solve the optimisation problem.

Gonzalez et al. [167, 171] produced a comprehensive analysis of the WT cost using net present value as the cost function. The study included initial capital costs, wake decay effects, auxiliary costs and the electrical infrastructure in its cost analysis, whilst also considering different types and sizes of turbines. It used a Weibull distribution and wind rose to model the wind speed and direction respectively.

In 2015 Chen et al. [172] researched the possibility of using turbines with different tower heights. It used a genetic algorithm with two different tower height possibilities, in a 2 by 2 km domain considering only a constant wind speed and direction. For this limited study it was concluded that using turbines with different heights could be beneficial to total power output.

In 2016 Song et al. [23] used the study in [165] and considered 3D optimisation of WT layout. It extended the 2D wake loss model by including the wind profile and geometric height into the analysis. The computational study considered two cases, low and high variability in the wind direction. It was in agreement with [172] and extended this to conclude that for variable winds, different sized turbines positively benefited the power production of the farm in the long term, however this effect gradually decreased as the wind direction became more stable.

Some studies have included the effects of landowner costs into their objective functions [173, 174]. These models add an extra constraint into the problem but are useful when considering wind farm siting.

The linear wake model used in many of the studies described above and the following, [158, 175, 176, 177, 178] cannot be used for more complex terrain and non-uniform flow fields. A method developed in [179] known as the virtual particle model has been used by studies [180, 181, 182] considering complex terrain. The increased computational demand of this wake model means genetic algorithms cannot be used, as they generate huge populations that must all be resolved. The studies use evolutionary methods that start with an initial layout, then go through cycles of adding, moving and removing turbines to settle on an optimised layout.

Table 3 summarises the papers discussed in this section. It is clear to see a majority of the research undertaken has made use of LES with one of the simplified rotor models to reduce the computational expense that resolving the turbines brings.

## 6 Turbine Mechanics

- 1.
Structural analysis of the blades

- 2.
Mechanical components in the hub and nacelle

- 3.
Power control methods

Turbines are designed to last a minimum of 20 years, which is equivalent to approximately \(10^8\) rotations of the blades. The turbine must withstand a range of different loads that can cause considerable damage and fatigue to the structure. Common load types incurred are shown in Fig. 4.

Main sources of loading come from the aerodynamic effects. Turbines must be able to withstand the effects of high winds and stochastic loads such as turbulence, in a range of different positions. Transient loads are generated during start-up, braking and yawing of the system, and can lead to large stressing of joints and bearings within the system.

One of the first models developed to study the turbine as a single system was the Linearized Hinge-Spring Blade rotor model, developed in 1987 by Eggleston and Stoddard [189], which is a simple model for the analysis of the deformation incurred by the turbine. It has an analytical solution that accounts for steady and cyclic loads, modelling each blade as a rigid body attached to a rigid hub through a series of springs and hinges. The model is a first order model that fails to predict higher frequency oscillations throughout the structure, so more developed models have been produced to resolve the finer details of turbine dynamics.

FEM has become increasingly popular to model the static and dynamic deformation of blades and structures in wind turbines. More recent studies using static analysis methods such as that by Jensen et al. [16] considered the geometrically non linear structural deformation of a blade. It took into account elastic effects such as buckling using a combination of solid and shell elements, however it neglected any damage criterion such as crack propagation or delamination. In the following year, Yang et al. [184] compared a full scale experiment to numerical results analysing the structural collapse of a blade. It included geometric non linear effects using shell elements. In 2015 Lee et al. [18] simulated the static analysis of the wind turbine blade root.

A transient analysis is often more useful due to the information it provides. Blades are increasingly failing due to vibratory and fatigue loads induced through cyclic loadings, which transient models can account for. In 2012 Lee et al. [79] used a flexible multi-body dynamic solver to analyse the aeroelastic response of a turbine blade. In 2014 Yu and Kwon [190] used FEM with non linear coupled flap-lag torsion beam theory, in combination with a CFD model, to again study the aeroelastic response of full wind turbine configuration. Gebhardt et al. [191, 192] used a segregated formulation of the structural equations, with an aero elastic model to predict the elastic response of the blade.

### 6.1 Failure Criterion

The loading on a wind turbine can be categorised into ultimate loads or fatigue loads. Ultimate loads are the maximum forces that can be withstood by the structure and its components, where as fatigue loads consider the ability of the structure to withstand cyclic loading. The most obvious periodic/cyclic load is the stress at the blade root caused by gravity and rotation of the rotor.

The blade is considered the most important part of the wind turbine as its structural integrity and ability to convert kinetic energy of the wind to mechanical energy, is paramount to efficient and cost effective turbines. As such there have been a number of experimental and numerical studies considering both the ultimate [16, 18] and fatigue [193, 194] failure of the blades. The cause of failure in turbine blades has an inherent link with research areas involved in composite laminates [17, 188] and analysis of thin structures [184].

Modern blades are made of polymer-matrix composites, and undergo approximately \(10^8\) cycles/rotations in their 20 year lifetime. With such a large number of cycles even the smallest periodic loads can dramatically fatigue the structure [195].

A number of studies have aimed to pinpoint the main failure system in turbine blades, Fig. 4 summarises the failure mechanisms that will be described below.

Jensen et al. [16, 187] determined that the Brazier effect [196] was the main cause of failure. The Brazier effect arises due to the bending of thin walled hollow structures, such as the shear web within the blade, and causes a crushing pressure on it. They used solid and shell elements to analyse the elastic, geometrically non-linear structural behaviour of the structure using FEM.

Overgaard et al. [17, 188] considered the primary failure mechanism to come from delamination within the composite layup which led to buckling. They produced an FEM model capable of modelling the propagation of inter-laminar failure.

Yang et al. [184] discovered that under flapwise loading, stress concentrations around defects within the material cause an initial fracture which, in combination with delamination and debonding of the aerodynamic shell, propagates to cause complete structural collapse.

Chou et al. [186] analysed the failure mode of blades damaged in a typhoon that hit the Changhua Costal Industrial Park in Taichung. An finite element model was produced based on the criteria found during the field analysis of the blades, which was then used to simulate both a static and dynamic load on the blades. It was found that the resonance of the blade over long term can lead to the formulation of cracks and delamination. This would lead to progressive damage within the blades and subsequently under high wind conditions failure.

In 2015 Lee et al. [18] undertook an experimental study, discovering that the onset of failure began from delamination at the blade root. Subsequently an FEM model of the blades was produced in Abaqus using a combination of shell and solid elements. A static analysis was undertaken which showed that conventional methods of modelling the root as a hollow circular cylinder does not represent the real stress distribution. It emphasised the difference in loading across the bolts used to join the blade to the hub.

The above studies all use finite element models to clarify and obtain more detail about the initial causes of failure in turbine blades. Along with using previously existing finite elements to model wind turbines, some studies [197, 198] have focused on the development of finite elements specifically to model turbine blades. There has been a number of purely experimental tests [199, 200] that do not fall under the scope of this review, but are useful for the analysis of blade failure mechanisms.

Fatigue analysis has been used in [185, 193, 194, 201] to improve the approximation of lifespans. It is usually modelled using empirical formulae developed by Spera in [202] in conjunction with S–N linear damage equation, Miners law and Goodman diagrams. The basics of fatigue in turbines is described in [195].

Kong et al. [185, 194] undertook a full analysis on a 750 kW blade made of E-glass and epoxy, using a full scale experimental test to validate the FEM model developed. The model included a wide range of loading from aerodynamic and mechanical loads to effects of ice and extreme conditions. The study showed good agreement between the experimental and numerical model.

Marin et al. [201] used S–N curves along with miners rule to identify the fatigue mechanics that were predicted to have caused failure in a 300*kW* turbine blade. The analysis showed that the onset of fatigue caused a superficial crack to be formed which propagated, causing further cracking and delamination, eventually leading to failure of the blade.

### 6.2 Turbine Design

The design of blades is critical in the development of longer lasting turbines with lower maintenance costs. With the size of blades growing there has been a trend towards composite materials such as glass fibre reinforced polymers to lower the weight and improve stiffness. In 2015 Chenouri et al. [21] produced a comprehensive review of optimisation methods and techniques used towards improving wind turbine performance.

The design of blades can be split into two categories, aerodynamic design and structural design. Aerodynamic design involves the geometric shape with respect to the inflow conditions: wind speed, wind shear, rated power and tower height to name a few. The structural design of the blade involves the optimisation of the blade, with outer geometric constraints from the aerodynamic design, to reduce factors such as cost, stress and fatigue in the blades.

The objective functions have focused on a range of factors from minimising the blade mass as in [203, 204] to minimising the cost of energy as in [205, 206].

#### 6.2.1 Aerodynamic Design

In order to design efficient, light and stiff blades there have been many models that take the form of optimisation problems, with inputs from the aerodynamic and structural factors and outputs of a given blade design.

- 1.
- 2.

Benini and Toffolo [206] also used BEM theory with tip loss corrections to test their solutions generated using a multi objective evolutionary algorithm aiming to minimise the COE and maximise the AEP. These are two conflicting issues and so a pareto-optimal design space is found as opposed to a single solution. The design variables included the hub/tip ratio, chord distribution, twist and tip speed ratio.

Xudong et al. [213] used similar design variables and flow model as Benini and Toffolo, but included a dynamic structural model to analyse flap-wise and edgewise deflections. The framework was used to optimise three current rotors, Tjoereborg 2 MW, MEXICO 25 kW and NREL 5 MW, by altering the chord and twist angle along the blade radius. The study only considered the cost of the rotor itself but showed a reduction in COE by 1.1, 3.4 and 2.6% respectively.

A more recent study by Ribeiro et al. [207] used artificial neural network methods along with a genetic algorithm to maximise the L/D ratio. The analysis of the solutions used the incompressible Navier–Stokes equations and the Spalart-Allmaras turbulence model in Fluent. A pareto front was found, with one solution offering the lowest coefficient of drag and another the highest coefficient of lift.

Other authors have used unique objective functions, with Jeong et al. [214] aiming to minimise the fluctuating flap wise bending moment of the blade in turbulent wind and Lee et al. [215] minimising the noise produced by the airfoil of a 10 kW turbine.

#### 6.2.2 Structural Design

The structural design of a blade is heavily linked with the fatigue and failure modes described in the previous section. With the concern about the blade weight and stiffness, there was a movement away from metals towards composite materials. There had been a number of studies [216, 217, 218] concerning the optimisation of composite laminates in structures. There have also been comprehensive studies into optimisation techniques [219] used in physical sciences. A combination of these two research areas led to the optimisation of the structural design of wind turbine blades.

Jureczko et al. [220] used a modified genetic algorithm in a multi-criterion optimisation model to minimise vibration, maximise power output, minimise blade cost and fulfil any strength requirements of the blade. This was done using the following criteria: the shell and web thickness and the number and position of stiffening ribs. The models were tested using the FEM in Ansys to ensure strength and displacement requirements of the blade were met.

A similar study was conducted by Chen et al. [22]. A BEM model was used to predict the aerodynamic forces which are applied to the proposed design and modelled using the FEM method. A particle swarm method was used to alter the spar cap position and thickness to minimise the mass of the blade.

Lund and Stegmann [221] used a gradient based optimisation technique to design the blade to maximise the stiffness. The composite layup of the main spar is altered using a discrete material optimisation approach and the subsequent model stiffness is calculated using a weighted sum of the candidate materials and linear buckling analysis in the FEM. This optimisation methodology was similarly used in [222] and [223] to optimise the fibre direction in spar caps, with the former assuming linear elastic behaviour and the latter using non linear buckling analysis to model the material.

Monroy Aceves et al. [224] have produced a methodology for material selection and design, that combines properties of the material with results of non-linear finite element analysis of the model, based on aerodynamic forces. The solutions are then reduced down based on specific selection criteria to choose an exact design.

The optimisation of blade shape and structure will become increasingly important as the blades grow in size and flexibility.

## 7 Fluid–Structure Interaction

FSI has been present in the wind industry under the name of aero-elasticity [190, 225, 226] for some time. Aero-elasticity involves coupling a flow solver to a structural model, to predict the dynamic response of the structure to a range of loads. A series of programs are available that use BEM theory with simple one dimensional structural models [227, 228].

However, with recent improvements to performance and capabilities to both software and hardware in the high performance computing industry, there has been a trend towards full 3D analysis of both the structural and aerodynamic analysis of entire turbines [9, 10, 229].

The main body of work has been carried out by the Department of Structural Engineering at the University of California. The studies have been built upon the development of Iso-Geometric Analysis (IGA) by Hughes et al. in 2005 [230]. The development of this methodology led to the first comprehensive study by Bazilevs et al. [10, 11], as a method to model aerodynamics in turbines. The model has been used to run FSI simulations, using a combination of Kirchoff–Love shell theory and the bending strip method, with only displacement degrees of freedom to model the structure.

The domain was reduced to one blade, a 120° cut. The paper showed the twist angle of the flexible blades undergoes high frequency oscillations, attributed to vortex shedding off the trailing edge and turbulence effects.

This led to similar low magnitude, high frequency oscillations in the torque developed on the blade. In 2012 he proposed a new framework to model FSI problems [231] using T-splines to model the structure and NURBS to model the fluid non matching grid at the interface. It performed well in early simulations, showing no drop in accuracy compared to matching NURBS–NURBS fluid structure grid. These models did not include the effects of a tower or nacelle.

Hsu et al. [9] simulated a full downwind turbine using an FSI model. Their model combined an ALE-VMS finite element fluid domain with a structural domain, discretised using NURBS based iso-geometric analysis. The entire domain consisted of 1,440,425 nodes and 4,828,692 elements. These simulations showed the presence of the tower caused a 10–12% drop in torque generated by a blade as it rotated. It also captured the non symmetric loading on the blades which can cause irregular loading on the hub. These findings are important in studying fatigue and expected life span of turbines.

Yu and Kwon from the Department of Aerospace Engineering at the Korea Advanced Institute of Science and Technology [190], produced a loosely coupled fluid structure interaction solver that was used to model the NREL 5 MW turbine. It modelled the blade using non-linear Euler–Bernoulli beam theory, with lead-lag bending, flapwise bending and deformations due to torque all included in the model. They discovered similar results to [9] in that there was a drop in blade loading as it passed the tower and the interference with the tower caused both loading and displacement oscillations. The tower also caused high frequency vibrations that occurred at the blade root.

Most recently two studies have been conducted that again build on the IGA framework [232, 233], that have focused on developing more accurate methods to model the problem, from new mesh moving techniques in the former to a new method to smoothly connect fluid sub domains in the latter.

Some 2D studies have been conducted looking at the effects of morphing blades on the loads generated [234, 235]. It was concluded that morphing blades performed better when the wind speed was under optimum value but worse when over it. Given the operating point of the blade can be controlled in the design process it was suggested that morphing blades offer a better option than rigid blades when it comes to performance over a wide range of loadings. This 2D model has been improved to a full 3D model in [236].

Full 3D analysis, combining the fluid and structure offers more realistic and physical results that can be utilised to design and build more energy efficient turbines.

## 8 State of the Art

Over the past 15–20 years, wind energy has grown in both maturity and efficiency to a point where it is almost competitive with traditional forms of energy, such as coal and gas. Governments have made extensive efforts to encourage investment in renewable technologies, specifically onshore and offshore wind energy devices, so that they can play a major role in the energy market. The trend over the past 15 years has been towards taller and larger turbines, which are more cost effective than their smaller counterparts. However, the linear and simplified approximations originally developed to model the physics no longer provide the fidelity and detail required by engineers. There is a requirement for models that better simulate both the fluid dynamics and structural mechanics of the problem.

This review has revealed the state of the art in the research being undertaken in the area of “Wind Energy” and “Computer Simulation”. The review has covered a wide range of topics, from atmospheric flow modelling to blade design optimisation.

The wind resource was the first topic covered. In order to generate more reliable and physical models it is important to correctly simulate the input to a wind turbine or farm. The state of the art in boundary layer modelling, combines the mesoscale atmospheric models that capture effects down to around 1 km with large eddy simulations that can capture the finer details to approximately 50 m [76, 77]. The Weather Research Forecasting Model (WRF) is one mesoscale model used, it captures the atmospheric dynamics and can be run across multiple cores in parallel environments. However for more specific modelling of complex terrains, studies have found that RANS simulations can more accurately predict the flow, when compared with experimental results [74].

It has been clear the effect that available computing power has had on the development of rotor models and the CFD approaches used. When modelling turbine rotors and blades, fully resolved geometries combined with RANS simulations using two equation turbulence models, currently dominate the field, see Table 2. They provide results that most accurately match the extensive experimental data available, for a range of turbines. The computational requirements needed to resolve the near wall boundary layer using LES models is high, however in 2016 Zhou et al. [134] performed an LES study using a fully resolved model of the NREL phase VI turbine. This represents a important step towards higher fidelity CFD simulations.

Modelling and simulation involving wind farms, has made use of the recent developments in wind resource modelling techniques to simulate the complex dynamic flows that occur at turbine rotor heights. The farms are modelled using a range of techniques but, the state of the art lies in LES simulations using AD and AL models, see Table 3. These types of models have been used for both wake analysis [86, 88, 140] and layout optimisation [23, 165], in large turbine arrays. These models provide important information about how turbines interact with each other when arranged in a large array.

Research involving the structural mechanics in wind turbine blades has involved research into the failure mechanisms [17, 186, 188]. The FEM is used in a large proportion of the studies reviewed, utilising a range of different finite elements to model the external and internal structure of blades. Optimisation studies into blade structure and shape use the finite element models to validate the final solutions.

Figure 1 represents the division between the scales of modelling and simulation in the wind industry. From 2011, studies [9, 10] begun to couple fully resolved CFD simulations with full 3D geometric representations of the structure in FSI simulations. This represents a large step in coupling the physics of the flow and structure. The state of the art in FSI simulations currently lies in the use of IGA, with studies gone as far as modelling the full turbine [9].

The wind industry faces a range of challenges as the size and number of turbines increases. It is clear that the software used to model and simulate the associated issues will be essential in improving the efficiency and reducing the cost of energy, so wind energy can play a larger role in the energy market.

A large number of models exist to simulate the different scales and physics involved in the wind industry. They will continue to play an important role in the development process, however a clear trend towards models encompassing a range of physics and scales can be seen from the literature. Examples include linking mesoscale numerical weather prediction models to CFD codes in order to improve estimations about incoming wind profiles and ultimately power output from farms. FSI models have been developed to more accurately model the interaction between the turbine and fluid, in order to improve the design of the blades. These models have represented a key step towards full first principal simulations involving multi physics.

The linking and coupling of both scales and physics is possible due to the growing availability of computer resources, HPC systems and cloud computing, to researchers and companies. The opportunities to develop more flexible and scalable software, to improve the fidelity and detail of models, are increasing.

The author believes that with the ever growing computing power available to researchers and the trends towards coupling through scales and disciplines that the “Digital Wind Farm” is a possibility. It strives to encompass and link the individual simulation methodologies currently being undertaken, from mesoscale wind profiles down to damage and fracture models of the structure.

In this era of “Big Data” the amount of information that is obtained from currently existing wind turbines and farms is huge. This data can be integrated into models to add a further level of realism to the simulations. Integration of data into simulations offers many possibilities. The use of LiDAR to measure incoming wind speeds and directions can be used to run pre-emptive/real time simulations to predict power output. The use of sensors on turbine components can be used to provide simulations with data concerning material variability over its lifetime, to better predict lifespan and failure mechanisms.

The gap between the models developed and the industrial solutions produced is slowly reducing. As these models improve and the level of information and detail they provide increases, the wind industry should see more durable efficient turbines being developed. This will result in the wind industry being capable of competing with non-renewable sources and playing a major role in the global energy market.

## Notes

### Acknowledgements

The authors acknowledge the support of EPSRC and General Electric through Grant EP/M507969/1.

### Compliance with Ethical Standards

### Conflict of interest

The authors declare that they have no conflict of interest.

## References

- 1.European Commission (2030) Energy strategyGoogle Scholar
- 2.Environmental Protection Agency (2017) Clean power plan. https://www.epa.gov/cleanpowerplan
- 3.Grubb M, Butler L, Twomey P (2006) Diversity and security in UK electricity generation: the influence of low-carbon objectives. Energy Policy 34(18):4050–4062CrossRefGoogle Scholar
- 4.Energy Information Administration (2016) Electric power monthly (Data for March 2016)Google Scholar
- 5.Department for Business, Energy & Industrial Strategy (2017) Energy trends: renewablesGoogle Scholar
- 6.Department of Energy & Climate Change (2013) DECC electricity generation costsGoogle Scholar
- 7.Hansen M, Sørensen J, Voutsinas S, Sørensen N, Madsen H (2006) State of the art in wind turbine aerodynamics and aeroelasticity. Prog Aerosp Sci 42(4):285–330CrossRefGoogle Scholar
- 8.Zhang P, Huang S (2011) Review of aeroelasticity for wind turbine: current status, research focus and future perspectives. Front Energy 5(4):419–434MathSciNetGoogle Scholar
- 9.Hsu MC, Bazilevs Y (2012) Fluid–structure interaction modeling of wind turbines: simulating the full machine. Comput Mech 50(6):821–833zbMATHCrossRefGoogle Scholar
- 10.Bazilevs Y, Hsu MC, Akkerman I, Wright S, Takizawa K, Henicke B, Spielman T, Tezduyar TE (2011a) 3D simulation of wind turbine rotors at full scale. Part I: geometry modeling and aerodynamics. Int J Numer Methods Fluids 65(1–3):207–235zbMATHCrossRefGoogle Scholar
- 11.Bazilevs Y, Hsu MC, Kiendl J, Wüchner R, Bletzinger KU (2011b) 3D simulation of wind turbine rotors at full scale. Part II: fluid–structure interaction modeling with composite blades. Int J Numer Methods Fluids 65(1–3):236–253zbMATHCrossRefGoogle Scholar
- 12.Martínez-Tossas LA, Churchfield MJ, Leonardi S (2015) Large Eddy simulations of the flow past wind turbines: actuator line and disk modeling. Wind Energy 18:657–669CrossRefGoogle Scholar
- 13.Zhou N, Chen J, Adams DE, Sanford F (2016) Influence of inflow conditions on turbine loading and wake structures predicted by Large Eddy simulations using exact geometry. Wind Energy 19:803–824CrossRefGoogle Scholar
- 14.Sanderse B, Pijl S, Koren B (2011) Review of computational fluid dynamics for wind turbine wake aerodynamics. Wind Energy 14(7):799–819CrossRefGoogle Scholar
- 15.Schmitz S, Chattot JJ (2006) Characterization of three-dimensional effects for the rotating and parked NREL phase VI wind turbine. J Sol Energy Eng 128(4):445CrossRefGoogle Scholar
- 16.Jensen F, Weaver P, Cecchini L, Stang H, Nielsen R (2012) The brazier effect in wind turbine blades and its influence on design. Wind Energy 15(2):319–333CrossRefGoogle Scholar
- 17.Overgaard L, Lund E (2010) Structural collapse of a wind turbine blade. Part B: progressive interlaminar failure models. Composites A 41(2):271–283CrossRefGoogle Scholar
- 18.Lee HG, Kang MG, Park J (2015) Fatigue failure of a composite wind turbine blade at its root end. Compos Struct 133:878–885CrossRefGoogle Scholar
- 19.Balogh M, Parente A, Benocci C (2012) RANS simulation of ABL flow over complex terrains applying an enhanced k–\(\epsilon\) model and wall function formulation: implementation and comparison for fluent and openfoam. J Wind Eng Ind Aerodyn 104:360–368CrossRefGoogle Scholar
- 20.Bechmann A, Sørensen NN (2010) Hybrid RANS/LES method for wind flow over complex terrain. Wind Energy 13(1):36–50CrossRefGoogle Scholar
- 21.Chehouri A, Younes R, Ilinca A, Perron J (2015) Review of performance optimization techniques applied to wind turbines. Appl Energy 142:361–388CrossRefGoogle Scholar
- 22.Chen J, Wang Q, Shen WZ, Pang X, Li S, Guo X (2013) Structural optimization study of composite wind turbine blade. Mater Design 46:247–255CrossRefGoogle Scholar
- 23.Song Z, Zhang Z, Chen X (2016) The decision model of 3-dimensional wind farm layout design. Renewable Energy 85:248–258CrossRefGoogle Scholar
- 24.Snel H (1998) Review of the present status of rotor aerodynamics. Wind Energy 1(S1):46–69CrossRefGoogle Scholar
- 25.Ackermann T (2000) Wind energy technology and current status: a review. Renew Sustain Energy Rev 4(4):315–374CrossRefGoogle Scholar
- 26.Ackermann T, Söder L (2002) An overview of wind energy-satus 2002. Renew Sustain Energy Rev 6(1–2):67–127CrossRefGoogle Scholar
- 27.Sahin A (2004) Progress and recent trends in wind energy. Prog Energy Combust Sci 30(5):501–543CrossRefGoogle Scholar
- 28.Joselin Herbert G, Iniyan S, Sreevalsan E, Rajapandian S (2007) A review of wind energy technologies. Renew Sustain Energy Rev 11(6):1117–1145CrossRefGoogle Scholar
- 29.Pryor S, Barthelmie R (2010) Climate change impacts on wind energy: a review. Renew Sustain Energy Rev 14(1):430–437CrossRefGoogle Scholar
- 30.Esteban MD, Diez JJ, López JS, Negro V (2011) Why offshore wind energy? Renewable Energy 36(2):444–450CrossRefGoogle Scholar
- 31.Leung DY, Yang Y (2012) Wind energy development and its environmental impact: a review. Renew Sustain Energy Rev 16(1):1031–1039CrossRefGoogle Scholar
- 32.Dai K, Bergot A, Liang C, Xiang WN, Huang Z (2015) Environmental issues associated with wind energy a review. Renewable Energy 75:911–921CrossRefGoogle Scholar
- 33.Barlas T, van Kuik G (2010) Review of state of the art in smart rotor control research for wind turbines. Prog Aerosp Sci 46(1):1–27CrossRefGoogle Scholar
- 34.Cheng M, Zhu Y (2014) The state of the art of wind energy conversion systems and technologies: a review. Energy Convers Manage 88:332–347CrossRefGoogle Scholar
- 35.Hossain MM, Ali MH (2015) Future research directions for the wind turbine generator system. Renew Sustain Energy Rev 49:481–489CrossRefGoogle Scholar
- 36.Rahman M, Ong ZC, Chong WT, Julai S, Khoo SY (2015) Performance enhancement of wind turbine systems with vibration control: a review. Renew Sustain Energy Rev 51:43–54CrossRefGoogle Scholar
- 37.Borg M, Shires A, Collu M (2014a) Offshore floating vertical axis wind turbines, dynamics modelling state of the art. Part I: aerodynamics. Renew Sustain Energy Rev 39:1214–1225CrossRefGoogle Scholar
- 38.Borg M, Collu M, Kolios A (2014b) Offshore floating vertical axis wind turbines, dynamics modelling state of the art. Part II: mooring line and structural dynamics. Renew Sustain Energy Rev 39:1226–1234CrossRefGoogle Scholar
- 39.Borg M, Collu M (2015) Offshore floating vertical axis wind turbines, dynamics modelling state of the art. Part III: hydrodynamics and coupled modelling approaches. Renew Sustain Energy Rev 46:296–310zbMATHCrossRefGoogle Scholar
- 40.Benitz M, Lackner M, Schmidt D (2015) Hydrodynamics of offshore structures with specific focus on wind energy applications. Renew Sustain Energy Rev 44:692–716CrossRefGoogle Scholar
- 41.McKenna R, Ostman vd Leye P, Fichtner W (2016) Key challenges and prospects for large wind turbines. Renew Sustain Energy Rev 53:1212–1221CrossRefGoogle Scholar
- 42.Elliott D, Holladay C, Barchet W, Foote H, Sandusky W (1986) Wind energy resource Atlas of the United States. Tech. rep. National Renewable Energy Laboratory, GoldenGoogle Scholar
- 43.Troen I, Lundtang Petersen E (1989) European wind atlas. Risø National Laboratory, RoskildeGoogle Scholar
- 44.Stull RB (ed) (1988) An introduction to boundary layer meteorology. Springer, NetherlandszbMATHGoogle Scholar
- 45.Taylor PA, Gent PR (1974) A model of atmospheric boundary-layer flow above an isolated two-dimensional ‘hill’; an example of flow above ‘gentle topography’. Bound-Layer Meteorol 7(3):349–362CrossRefGoogle Scholar
- 46.Taylor PA (1977) Some numerical studies of surface boundary-layer flow above gentle topography. Bound-Layer Meteorol 11(4):439–465CrossRefGoogle Scholar
- 47.Frost W, Maus J, Fichtl G (1974) A boundary-layer analysis of atmospheric motion over a semi-elliptical surface obstruction. Bound-Layer Meteorol 7(2):165–184CrossRefGoogle Scholar
- 48.Jackson PS, Hunt JCR (1975) Turbulent wind flow over a low hill. Q J R Meteorol Soc 101(430):929–955CrossRefGoogle Scholar
- 49.Deaves D (1980) Computations of wind flow over two-dimensional hills and embankments. J Wind Eng Ind Aerodyn 6(1):89–111CrossRefGoogle Scholar
- 50.Deaves D (1981) Computations of wind flow over changes in surface roughness. J Wind Eng Ind Aerodyn 7(1):65–94CrossRefGoogle Scholar
- 51.Kim HG, Lee CM, Lim H, Kyong N (1997) An experimental and numerical study on the flow over two-dimensional hills. J Wind Eng Ind Aerodyn 66(1):17–33CrossRefGoogle Scholar
- 52.Carpenter P, Locke N (1999) Investigation of wind speeds over multiple two-dimensional hills. J Wind Eng Ind Aerodyn 83(1):109–120CrossRefGoogle Scholar
- 53.Paterson D, Holmes J (1993) Computation of wind flow over topography. J Wind Eng Ind Aerodyn 46:471–476CrossRefGoogle Scholar
- 54.Richards P, Hoxey R (1993) Appropriate boundary conditions for computational wind engineering models using the k–\(\epsilon\) turbulence model. J Wind Eng Ind Aerodyn 46–47:145–153CrossRefGoogle Scholar
- 55.Deardorff JW (1972) Numerical investigation of neutral and unstable planetary boundary layers. J Atmos Sci 29(1):91–115CrossRefGoogle Scholar
- 56.Moeng CH (1984) A Large-Eddy-simulation model for the study of planetary boundary-layer turbulence. J Atmos Sci 41(13):2052–2062CrossRefGoogle Scholar
- 57.Raithby GD, Stubley GD, Taylor PA (1987) The Askervein Hill project: a finite control volume prediction of three-dimensional flows over the hill. Bound-Layer Meteorol 39(3):247–267CrossRefGoogle Scholar
- 58.Scopus (2016) https://www.scopus.com/. Accessed on 16 June 2016
- 59.Castro FA, Palma JMLM, Silva Lopes A (2003) Simulation of the Askervein flow. Part 1: reynolds averaged Navier–Stokes equations (k–\(\epsilon\)epsilon turbulence model). Bound-Layer Meteorol 107(3):501–530CrossRefGoogle Scholar
- 60.Crasto G (2007) Numerical simulations of the atmospheric boundary layer. PhD thesis, Faculty of Engineering, University of Cagliari, Cagliari.Google Scholar
- 61.Hargreaves DM, Wright NG (2006) The use of commercial CFD software to model the atmospheric boundary layer. Cwe 2006:797–800Google Scholar
- 62.Hargreaves D, Wright N (2007) On the use of the k–\(\epsilon\) model in commercial CFD software to model the neutral atmospheric boundary layer. J Wind Eng Ind Aerodyn 95(5):355–369CrossRefGoogle Scholar
- 63.Blocken B, Stathopoulos T, Carmeliet J (2007) CFD simulation of the atmospheric boundary layer: wall function problems. Atmos Environ 41(2):238–252CrossRefGoogle Scholar
- 64.Yang Y, Gu M, Chen S, Jin X (2009) New inflow boundary conditions for modelling the neutral equilibrium atmospheric boundary layer in computational wind engineering. J Wind Eng Ind Aerodyn 97(2):88–95CrossRefGoogle Scholar
- 65.Chow FK, Street RL (2009) Evaluation of turbulence closure models for Large-Eddy simulation over complex terrain: flow over Askervein hill. J Appl Meteorol Climatol 48(5):1050–1065CrossRefGoogle Scholar
- 66.Parente A, Gorlé C, van Beeck J, Benocci C (2011) Improved k–\(\epsilon\) model and wall function formulation for the RANS simulation of ABL flows. J Wind Eng Ind Aerodyn 99(4):267–278CrossRefGoogle Scholar
- 67.Bechmann A (2006) Large-Eddy simulation of atmospheric flow over complex terrain. PhD thesis, Technical University of Denmark (DTU), LyngbyGoogle Scholar
- 68.Mason PJ (1989) Large-Eddy simulation of the convective atmospheric boundary layer. J Atmos Sci 46(11):1492–1516CrossRefGoogle Scholar
- 69.Andren A, Brown AR, Mason PJ, Graf J, Schumann U, Moeng CH, Nieuwstadt FTM (1994) Large-Eddy Simulation of a neutrally stratified boundary layer: a comparison of four computer codes. Q J R Meteorol Soc 120(520):1457–1484CrossRefGoogle Scholar
- 70.Albertson JD, Parlange MB (1999) Natural integration of scalar fluxes from complex terrain. Adv Water Resour 23(3):239–252CrossRefGoogle Scholar
- 71.Bou-Zeid E (2004) Large-Eddy simulation of neutral atmospheric boundary layer flow over heterogeneous surfaces: blending height and effective surface roughness. Water Resour Res 40(2):1–18CrossRefGoogle Scholar
- 72.Porté-Agel F (2004) A scale-dependent dynamic model for scalar transport in Large-Eddy Simulations of the atmospheric boundary layer. Bound-Layer Meteorol 112(1):81–105CrossRefGoogle Scholar
- 73.Silva Lopes A, Palma JMLM, Castro FA (2007) Simulation of the Askervein flow. Part 2: Large-Eddy simulations. Bound-Layer Meteorol 125(1):85–108CrossRefGoogle Scholar
- 74.Bechmann A, Sørensen NN, Berg J, Mann J, Réthoré PE (2011) The bolund experiment. Part II: blind comparison of microscale flow models. Bound-Layer Meteorol 141(2):245–271CrossRefGoogle Scholar
- 75.Yan BW, Li QS, He YC, Chan PW (2016) RANS simulation of neutral atmospheric boundary layer flows over complex terrain by proper imposition of boundary conditions and modification on the k–\(\epsilon\) model. Environ Fluid Mech 16(1):1–23CrossRefGoogle Scholar
- 76.Muñoz-Esparza D, Kosović B, Mirocha J, van Beeck J (2014) Bridging the transition from mesoscale to microscale turbulence in numerical weather prediction models. Bound-Layer Meteorol 153(3):409–440CrossRefGoogle Scholar
- 77.Talbot C, Bou-Zeid E, Smith J, Talbot C, Bou-Zeid E, Smith J (2012) Nested mesoscale Large-Eddy simulations with WRF: performance in real test cases. J Hydrometeorol 13(5):1421–1441CrossRefGoogle Scholar
- 78.Esfahanian V, Salavati Pour A, Harsini I, Haghani A, Pasandeh R, Shahbazi A, Ahmadi G (2013) Numerical analysis of flow field around NREL phase II wind turbine by a hybrid CFD/BEM method. J Wind Eng Ind Aerodyn 120:29–36CrossRefGoogle Scholar
- 79.Lee JW, Lee JS, Han JH, Shin HK (2012) Aeroelastic analysis of wind turbine blades based on modified strip theory. J Wind Eng Ind Aerodyn 110:62–69CrossRefGoogle Scholar
- 80.Jimenez A, Crespo A, Migoya E, Garcia J (2008) Large-Eddy simulation of spectral coherence in a wind turbine wake. Environ Res Lett 3(1):015004CrossRefGoogle Scholar
- 81.Wu YT, Porté-Agel F (2010) Large-Eddy simulation of wind-turbine wakes: evaluation of turbine parametrisations. Bound-Layer Meteorol 138(3):345–366CrossRefGoogle Scholar
- 82.Sørensen NN, Michelsen JA, Schreck S (2002) Navier–Stokes predictions of the NREL phase VI rotor in the NASA ames 80 Ft \(\times\) 120 Ft wind tunnel. Wind Energy 5(2–3):151–169CrossRefGoogle Scholar
- 83.Shen WZ, Sørensen JN, Zhang JH (2007) Actuator surface model for wind turbine flow computations. European Wind Energy Conference and Exhibition 2007, EWEC 2007 2:1198–1205Google Scholar
- 84.Kim T, Oh S, Yee K (2015) Improved actuator surface method for wind turbine application. Renewable Energy 76:16–26CrossRefGoogle Scholar
- 85.Calaf M, Meneveau C, Meyers J (2010) Large Eddy simulation study of fully developed wind-turbine array boundary layers. Phys Fluids 22(1):015110zbMATHCrossRefGoogle Scholar
- 86.Calaf M, Parlange MB, Meneveau C (2011) Large Eddy simulation study of scalar transport in fully developed wind-turbine array boundary layers. Phys Fluids 23(12):126603CrossRefGoogle Scholar
- 87.Abkar M, Porté-Agel F (2013) The effect of free-atmosphere stratification on boundary-layer flow and power output from very large wind farms. Energies 6(5):2338–2361CrossRefGoogle Scholar
- 88.Lu H, Porté-agel F (2011) Large-Eddy simulation of a very large wind farm in a stable atmospheric boundary layer. Phys Fluids 23(6):065101CrossRefGoogle Scholar
- 89.Cabezón D, Migoya E, Crespo A (2014) A semi-parabolic wake model for large offshore wind farms based on the open source CFD Solver openfoam. ITM Web Conf 2(06):002Google Scholar
- 90.Abkar M, Sharifi A, Porté-Agel F (2016) Wake flow in a wind farm during a diurnal cycle. J Turbul 17(4):420–441MathSciNetCrossRefGoogle Scholar
- 91.Zahle F, Johansen J, Sørensen N (2007) Wind turbine aerodynamics using an incompressible overset grid method. In: European Wind Energy Conference & Exhibition, StockholmGoogle Scholar
- 92.Zahle F, Sørensen NN, Johansen J (2009) Wind turbine rotor-tower interaction using an incompressible overset grid method. Wind Energy 12(6):594–619CrossRefGoogle Scholar
- 93.Wang Q, Zhou H, Wan D (2012) Numerical simulation of wind turbine blade–tower interaction. J Mar Sci Appl 11(3):321–327CrossRefGoogle Scholar
- 94.Manwell JE, McGowan JG (2009) Wind energy explained: theory, design and application, 2nd edn. Wiley, HobokenCrossRefGoogle Scholar
- 95.Hansen MOL (2008) Aerodynamics of wind turbines, 2nd edn. Earthscan, LondonGoogle Scholar
- 96.Branlard E, Gaunaa M (2014) Development of new tip-loss corrections based on Vortex theory and Vortex methods. J Phys 555(012):012Google Scholar
- 97.Shen WZ, Mikkelsen R, Sørensen JN, Bak C (2005) Tip loss corrections for wind turbine computations. Wind Energy 8(4):457–475CrossRefGoogle Scholar
- 98.Koh W, Ng E (2016) Effects of reynolds number and different tip loss models on the accuracy of bem applied to tidal turbines as compared to experiments. Ocean Eng 111:104–115CrossRefGoogle Scholar
- 99.Henriksen L, Hansen M, Poulsen N (2013) A simplified dynamic inflow model and its effect on the performance of free mean wind speed estimation. Wind Energy 16(8):1213–1224Google Scholar
- 100.Branlard E, Gaunaa M, Machefaux E (2014) Investigation of a new model accounting for rotors of finite tip-speed ratio in yaw or til. J Phys 524(1):012124Google Scholar
- 101.Pereira R, Schepers G, Pavel MD (2013) Validation of the Beddoes–Leishman dynamic stall model for horizontal axis wind turbines using MEXICO data. Wind Energy 16(2):207–219CrossRefGoogle Scholar
- 102.Castellani F, Vignaroli A (2013) An application of the actuator disc model for wind turbine wakes calculations. Appl Energy 101:432–440CrossRefGoogle Scholar
- 103.Simisiroglou N, Breton SP, Crasto G, Hansen K, Ivanell S (2014) Numerical CFD comparison of Lillgrund employing RANS. Energy Proc 53:342–351CrossRefGoogle Scholar
- 104.Jimenez A, Crespo A, Migoya E, Garcia J (2007) Advances in Large-Eddy simulation of a wind turbine wake. J Phys 75(1):012041Google Scholar
- 105.Aubrun S, Loyer S, Hancock P, Hayden P (2013) Wind turbine wake properties: comparison between a non-rotating simplified wind turbine model and a rotating model. J Wind Eng Ind Aerodyn 120:1–8CrossRefGoogle Scholar
- 106.Voutsinas S, Rados K, Zervos A (1993) Wake effects in wind parks: a new modelling approach. In: 1993 European Community Wind Energy Conference, Lubeck, pp 444–447Google Scholar
- 107.González-Longatt F, Wall P, Terzija V (2012) Wake effect in wind farm performance: steady-state and dynamic behavior. Renewable Energy 39(1):329–338CrossRefGoogle Scholar
- 108.Avila M, Folch A, Houzeaux G, Eguzkitza B, Prieto L, Cabezón D (2013) A parallel CFD model for wind farms. Proc Comput Sci 18:2157–2166CrossRefGoogle Scholar
- 109.Castellani F, Gravdahl A, Crasto G, Piccioni E, Vignaroli A (2013) A practical approach in the CFD simulation of off-shore wind farms through the actuator disc technique. Energy Proc 35:274–284CrossRefGoogle Scholar
- 110.Creech A, Früh WG, Maguire AE (2015) Simulations of an offshore wind farm using Large-Eddy simulation and a torque-controlled actuator disc model. Surv Geophys 36(3):427–481CrossRefGoogle Scholar
- 111.Sørensen JN, Shen WZ (1999) Computation of wind turbine wakes using combined Navier-Stokes/Actuator-line methodology. In: 1999 European Wind Energy Conference and Exhibition, StockholmGoogle Scholar
- 112.Wilson JM, Davis CJ, Venayagamoorthy SK, Heyliger PR (2014) Comparisons of horizontal-axis wind turbine wake interaction models. J Sol Energy Eng 137(3):031001CrossRefGoogle Scholar
- 113.Jonkman J, Butterfield S, Musial W, Scott G (2009) Definition of a 5-MW Reference Wind Turbine for Offshore System Development. Tech. rep. National Renewable Energy LaboratoryGoogle Scholar
- 114.Machefaux E, Troldborg N, Gunner C Larsen, Mann J, Madsen HA (2012) Experimental and Numerical Study of Wake to Wake Interaction in Wind Farms. In: European Wind Energy Conference and Exhibition, BrusselsGoogle Scholar
- 115.Churchfield MJ, Lee S, Moriarty PJ, Martinez LA, Leonardi S, Vijayakumar G, Brasseur JG (2012) A Large-Eddy Simulation of wind-plant aerodynamics preprint. In: 50th AIAA Aerospace Sciences MeetingGoogle Scholar
- 116.Drela M (1989) XFOIL: an analysis and design system for low reynolds number airfoils. Springer, BerlinGoogle Scholar
- 117.Dobrev I, Massouh F, Rapin M (2007) Actuator surface hybrid model. J Phys 75(1):012019Google Scholar
- 118.Shen WZ, Zhang JH, Sørensen JN (2009) The actuator surface model: a new Navier-Stokes based model for rotor computations. J Sol Energy Eng 131(1):011002CrossRefGoogle Scholar
- 119.Sibuet Watters C, Breton S, Masson C (2009) Application of the actuator surface concept to wind turbine rotor aerodynamics. Wind Energy 13(5):433–447CrossRefGoogle Scholar
- 120.Masson C, Sibuet Watters C (2008) Moving actuator surfaces: a new concept for wind turbine aerodynamic analysis. In: Proceedings of the international conference on renewable energies and power qualityGoogle Scholar
- 121.Johansen J, Sørensen NN, Michelsen JA, Schreck S (2002) Detached-Eddy simulation of flow around the NREL phase VI blade. Wind Energy 5(2–3):185–197CrossRefGoogle Scholar
- 122.Zahle F, Sørensen NN (2007) On the influence of far-wake resolution on wind turbine flow simulations. J Phys 75(1):012042Google Scholar
- 123.Bechmann A, Sørensen NN (2011) Hybrid RANS/LES applied to complex terrain. Wind Energy 14(2):225–237CrossRefGoogle Scholar
- 124.Benjanirat S, Sankar LN, Xu G (2003) Evaluation of turbulence models for the prediction of wind turbine aerodynamics. A Collection of the 2003 ASME Wind Energy Symposium Technical Papers Presented at the 41st AIAA Aerospace Sciences Meeting and Exhibit, pp 73–83Google Scholar
- 125.Duque EPN, Burklund MD, Johnson W (2003) Navier–Stokes and comprehensive analysis performance predictions of the NREL phase VI experiment. J Sol Energy Eng 125(4):457CrossRefGoogle Scholar
- 126.Simms D, Schreck S, Hand M, Fingersh L (2001) Wind tunnel testing of NREL’S unsteady aerodynamics experiment (AIAA). Tech. rep. National Renewable Energy Laboratory, GoldenGoogle Scholar
- 127.Tongchitpakdee C, Benjanirat S, Sankar LN (2005) Numerical simulation of the aerodynamics of horizontal axis wind turbines under yawed flow conditions. J Sol Energy Eng 127(4):464CrossRefGoogle Scholar
- 128.Schmitz S, Chattot JJ (2005) A parallelized coupled Navier–Stokes/vortex-panel solver. J Sol Energy Eng 127(4):475CrossRefGoogle Scholar
- 129.Steinhoff J, Underhill D (1994) Modification of the Euler equations for “vorticity confinement”: application to the computation of interacting vortex rings. Phys Fluids 6(8):2738zbMATHCrossRefGoogle Scholar
- 130.Hsu MC, Akkerman I, Bazilevs Y (2014) Finite element simulation of wind turbine aerodynamics: validation study using NREL phase VI experiment. Wind Energy 17(3):461–481CrossRefGoogle Scholar
- 131.Takizawa K, Henicke B, Tezduyar TE, Hsu MC, Bazilevs Y (2011) Stabilized spacetime computation of wind–turbine rotor aerodynamics. Comput Mech 48(3):333–344zbMATHCrossRefGoogle Scholar
- 132.Tezduyar T (1991) Advances in Applied Mechanics, vol 28. Elsevier, AmsterdamGoogle Scholar
- 133.Tezduyar T, Behr M, Liou J (1992) A new strategy for finite element computations involving moving boundaries and interfaces-the deforming-spatial-domain/space–time procedure: I. The concept and the preliminary numerical tests. Comput Methods Appl Mech Eng 94(3):339–351MathSciNetzbMATHCrossRefGoogle Scholar
- 134.Zhou N, Chen J, Adams DE, Fleeter S (2016) Influence of inflow conditions on turbine loading and wake structures predicted by large eddy simulations using exact geometry. Wind Energy 19(5):803–824CrossRefGoogle Scholar
- 135.Gomez-Iradi S, Steijl R, Barakos GN (2009) Development and validation of a CFD technique for the aerodynamic analysis of HAWT. J Sol Energy Eng 1313:031009CrossRefGoogle Scholar
- 136.Li Y, Paik KJ, Xing T, Carrica PM (2012) Dynamic overset CFD simulations of wind turbine aerodynamics. Renew Energy 37(1):285–298CrossRefGoogle Scholar
- 137.Laursen J, Enevoldsen P, Hjort S (2007) 3D CFD quantification of the performance of a multi-megawatt wind turbine. J Phys 75(1):012007Google Scholar
- 138.Hsu MC, Akkerman I, Bazilevs Y (2011) High-performance computing of wind turbine aerodynamics using isogeometric analysis. Comput Fluids 49(1):93–100MathSciNetzbMATHCrossRefGoogle Scholar
- 139.Barthelmie RJ, Pryor SC, Frandsen ST, Hansen KS, Schepers JG, Rados K, Schlez W, Neubert A, Jensen LE, Neckelmann S (2010) Quantifying the impact of wind turbine wakes on power output at offshore wind farms. J Atmos Oceanic Technol 27(8):1302–1317CrossRefGoogle Scholar
- 140.Porté-Agel F, Lu H, Wu YT (2014) Interaction between large wind farms and the atmospheric boundary layer. Proce IUTAM 10:307–318CrossRefGoogle Scholar
- 141.Tabib M, Rasheed A, Kvamsdal T (2015) LES and RANS simulation of onshore bessaker wind farm: analysing terrain and wake effects on wind farm performance. J Phys 625(012):032Google Scholar
- 142.Frandsen S, Barthelmie R, Pryor S, Rathmann O, Larsen S, Højstrup J, Thøgersen M (2006) Analytical modelling of wind speed deficit in large offshore wind farms. Wind Energy 9(1–2):39–53CrossRefGoogle Scholar
- 143.Lu H, Porté-Agel F (2015) On the impact of wind farms on a convective atmospheric boundary layer. Bound-Layer Meteorol 157(1):81–96CrossRefGoogle Scholar
- 144.Goit JP, Meyers J (2015) Optimal control of energy extraction in wind-farm boundary layers. J Fluid Mech 768:5–50MathSciNetzbMATHCrossRefGoogle Scholar
- 145.Baidya Roy S (2004) Can large wind farms affect local meteorology? J Geophys Res 109(D19):D19101CrossRefGoogle Scholar
- 146.Keith DW, Decarolis JF, Denkenberger DC, Lenschow DH, Malyshev SL, Pacala S, Rasch PJ (2004) The influence of large-scale wind power on global climate. In: Proceedings of the National Academy of Sciences of the United States of America 101(46):16115–16120Google Scholar
- 147.Baidya Roy S, Traiteur JJ (2010) Impacts of wind farms on surface air temperatures. In: Proceedings of the National Academy of Sciences of the United States of America 107(42):17899–17904Google Scholar
- 148.Pielke RA, Cotton WR, Walko RL, Tremback CJ, Lyons WA, Grasso LD, Nicholls ME, Moran MD, Wesley DA, Lee TJ, Copeland JH (1992) A comprehensive meteorological modeling system-RAMS. Meteorol Atmos Phys 49(1–4):69–91CrossRefGoogle Scholar
- 149.Wang C, Prinn RG (2010) Potential climatic impacts and reliability of very large-scale wind farms. Atmos Chem Phys 10(4):2053–2061CrossRefGoogle Scholar
- 150.Wang C, Prinn RG (2011) Potential climatic impacts and reliability of large-scale offshore wind farms. Environ Res Lett 6(2):025101CrossRefGoogle Scholar
- 151.Rasheed A, Holdahl R, Kvamsdal T, Åkervik E (2014) A comprehensive simulation methodology for fluid-structure interaction of offshore wind turbines. Energy Proc 53(C):135–145CrossRefGoogle Scholar
- 152.Abkar M, Porté-Agel F (2014) Mean and turbulent kinetic energy budgets inside and above very large wind farms under conventionally-neutral condition. Renewable Energy 70:142–152CrossRefGoogle Scholar
- 153.Abkar M, Porté-Agel F (2015) Influence of atmospheric stability on wind-turbine wakes: a Large-Eddy simulation study. Phys Fluids 27(3):035104CrossRefGoogle Scholar
- 154.Archer CL, Mirzaeisefat S, Lee S (2013) Quantifying the sensitivity of wind farm performance to array layout options using Large-Eddy simulation. Geophys Res Lett 40(18):4963–4970CrossRefGoogle Scholar
- 155.Wu YT, Porté-Agel F (2015) Modeling turbine wakes and power losses within a wind farm using LES: an application to the horns rev offshore wind farm. Renewable Energy 75:945–955CrossRefGoogle Scholar
- 156.Eriksson O, Lindvall J, Breton SP, Ivanell S (2015) Wake downstream of the lillgrund wind farm: a comparison between LES using the actuator disc method and a wind farm parametrization in WRF. J Phys 625(012):028Google Scholar
- 157.Jensen NO (1983) A note on wind generator interaction. Risø National Laboratory, RoskildeGoogle Scholar
- 158.Shakoor R, Hassan MY, Raheem A, Wu YK (2016) Wake effect modeling: a review of wind farm layout optimization using Jensens model. Renew Sustain Energy Rev 58:1048–1059CrossRefGoogle Scholar
- 159.Mosetti G, Poloni C, Diviacco B (1994) Optimization of wind turbine positioning in large windfarms by means of a genetic algorithm. J Wind Eng Ind Aerodyn 51(1):105–116CrossRefGoogle Scholar
- 160.Grady S, Hussaini M, Abdullah M (2005) Placement of wind turbines using genetic algorithms. Renewable Energy 30(2):259–270CrossRefGoogle Scholar
- 161.Castro Mora J, Calero Barón JM, Riquelme Santos JM, Burgos Payán M (2007) An evolutive algorithm for wind farm optimal design. Neurocomputing 70(16–18):2651–2658CrossRefGoogle Scholar
- 162.Huang HS (2007) Distributed genetic algorithm for optimization of wind farm annual profits. In: 2007 International Conference on Intelligent Systems Applications to Power Systems, pp 1–6Google Scholar
- 163.Marmidis G, Lazarou S, Pyrgioti E (2008) Optimal placement of wind turbines in a wind park using Monte Carlo simulation. Renewable Energy 33(7):1455–1460CrossRefGoogle Scholar
- 164.Turner S, Romero D, Zhang P, Amon C, Chan T (2014) A new mathematical programming approach to optimize wind farm layouts. Renewable Energy 63:674–680CrossRefGoogle Scholar
- 165.Kusiak A, Song Z (2010) Design of wind farm layout for maximum wind energy capture. Renewable Energy 35(3):685–694CrossRefGoogle Scholar
- 166.Mayo M, Daoud M (2016) Informed mutation of wind farm layouts to maximise energy harvest. Renewable Energy 89:437–448CrossRefGoogle Scholar
- 167.Gonzalez JS, Gonzalez Rodriguez AG, Mora JC, Santos JR, Payan MB (2010) Optimization of wind farm turbines layout using an evolutive algorithm. Renewable Energy 35(8):1671–1681CrossRefGoogle Scholar
- 168.Erolu Y, Seçkiner SU (2012) Design of wind farm layout using ant colony algorithm. Renewable Energy 44:53–62CrossRefGoogle Scholar
- 169.Chowdhury S, Zhang J, Messac A, Castillo L (2012) Unrestricted wind farm layout optimization (UWFLO): investigating key factors influencing the maximum power generation. Renewable Energy 38(1):16–30CrossRefGoogle Scholar
- 170.Chowdhury S, Zhang J, Messac A, Castillo L (2013) Optimizing the arrangement and the selection of turbines for wind farms subject to varying wind conditions. Renewable Energy 52:273–282CrossRefGoogle Scholar
- 171.González JS, Rodríguez ÁG, Mora JC, Burgos Payán M, Santos JR (2011) Overall design optimization of wind farms. Renewable Energy 36(7):1973–1982CrossRefGoogle Scholar
- 172.Chen Y, Li H, Jin K, Elkassabgi Y (2017) Investigating the possibility of using different hub height wind turbines in a wind farm. Int J Sustain Energy 36(2):142–150CrossRefGoogle Scholar
- 173.Chen L, MacDonald E (2014) A System-level Cost-of-energy Wind Farm Layout Optimization with Landowner Modeling. Energy Convers Manage 77:484–494CrossRefGoogle Scholar
- 174.Wang L, Tan AC, Gu Y, Yuan J (2015) A new constraint handling method for wind farm layout optimization with lands owned by different owners. Renewable Energy 83:151–161CrossRefGoogle Scholar
- 175.Emami A, Noghreh P (2010) New approach on optimization in placement of wind turbines within wind farm by genetic algorithms. Renewable Energy 35(7):1559–1564CrossRefGoogle Scholar
- 176.Pérez B, Mínguez R, Guanche R (2013) Offshore wind farm layout optimization using mathematical programming techniques. Renewable Energy 53:389–399CrossRefGoogle Scholar
- 177.Pookpunt S, Ongsakul W (2013) Optimal placement of wind turbines within wind farm using binary particle swarm optimization with time-varying acceleration coefficients. Renewable Energy 55:266–276CrossRefGoogle Scholar
- 178.Erolu Y, Seçkiner SU (2013) Wind farm layout optimization using particle filtering approach. Renewable Energy 58:95–107CrossRefGoogle Scholar
- 179.Song M, Chen K, He Z, Zhang X (2012) Wake flow model of wind turbine using particle simulation. Renewable Energy 41:185–190CrossRefGoogle Scholar
- 180.Song M, Chen K, He Z, Zhang X (2014) Optimization of Wind farm micro-siting for complex terrain using Greedy algorithm. Energy 67:454–459CrossRefGoogle Scholar
- 181.Song M, Chen K, Zhang X, Wang J (2015) The Lazy Greedy algorithm for power optimization of wind turbine positioning on complex terrain. Energy 80:567–574CrossRefGoogle Scholar
- 182.Song M, Chen K, Zhang X, Wang J (2016) Optimization of wind turbine micro-siting for reducing the sensitivity of power generation to wind direction. Renewable Energy 85:57–65CrossRefGoogle Scholar
- 183.El Chazly N (1993) Static and dynamic analysis of wind turbine blades using the finite element method. Comput Struct 48(2):273–290zbMATHCrossRefGoogle Scholar
- 184.Yang J, Peng C, Xiao J, Zeng J, Xing S, Jin J, Deng H (2013) Structural investigation of composite wind turbine blade considering structural collapse in full-scale static tests. Compos Struct 97:15–29CrossRefGoogle Scholar
- 185.Kong C, Kim T, Han D, Sugiya Ma Y (2006) Investigation of fatigue life for a medium scale composite wind turbine blade. Int J Fatigue 28(10):1382–1388zbMATHCrossRefGoogle Scholar
- 186.Chou JS, Chiu CK, Huang IK, Chi KN (2013) Failure analysis of wind turbine blade under critical wind loads. Eng Fail Anal 27:99–118CrossRefGoogle Scholar
- 187.Jensen FM, Puri AS, Dear JP, Branner K, Morris A (2011) Investigating the impact of non-linear geometrical effects on wind turbine blades. Part 1: current status of design and test methods and future challenges in design optimisation. Wind Energy 14:239–254CrossRefGoogle Scholar
- 188.Overgaard L, Lund E, Thomsen O (2010) Structural collapse of a wind turbine blade. part a: static test and equivalent single layered models. Composites A 41(2):257–270CrossRefGoogle Scholar
- 189.Eggleston DM, Stoddard FS (1987) Wind turbine engineering design. Van Nostrand Reinhold, New YorkGoogle Scholar
- 190.Yu DO, Kwon OJ (2014) Predicting wind turbine blade loads and aeroelastic response using a coupled CFD–CSD method. Renewable Energy 70:184–196CrossRefGoogle Scholar
- 191.Gebhardt C, Preidikman S, Jørgensen M, Massa J (2012) Non-linear aeroelastic behavior of large horizontal-axis wind turbines: a multibody system approach. Int J Hydrogr Energy 37(19):14719–14724CrossRefGoogle Scholar
- 192.Gebhardt C, Roccia B (2014) Non-linear aeroelasticity: an approach to compute the response of three-blade large-scale horizontal-axis wind turbines. Renewable Energy 66:495–514CrossRefGoogle Scholar
- 193.Shokrieh MM, Rafiee R (2006) Simulation of fatigue failure in a full composite wind turbine blade. Compos Struct 74(3):332–342CrossRefGoogle Scholar
- 194.Kong C, Bang J, Sugiyama Y (2005) Structural investigation of composite wind turbine blade considering various load cases and fatigue life. Energy 30(11–12):2101–2114CrossRefGoogle Scholar
- 195.Sutherland H (1999) On the fatigue analysis of wind turbines. Tech. rep. Sandia National Laboratories, AlbuquerqueGoogle Scholar
- 196.Brazier LG (1927) On the flexure of thin cylindrical shells and other “thin” sections. Proc R Soc A 116(773):104–114zbMATHCrossRefGoogle Scholar
- 197.Kim T, Hansen AM, Branner K (2013) Development of an anisotropic beam finite element for composite wind turbine blades in multibody system. Renewable Energy 59:172–183CrossRefGoogle Scholar
- 198.Cárdenas D, Escárpita AA, Elizalde H, Aguirre JJ, Ahuett H, Marzocca P, Probst O (2012) Numerical validation of a finite element thin-walled beam model of a composite wind turbine blade. Wind Energy 15(2):203–223CrossRefGoogle Scholar
- 199.Liu D, Shang X (2013) Failure investigation of the wind turbine blade root bolt. J Fail Anal Prev 13(3):333–339CrossRefGoogle Scholar
- 200.Lee HG, Park J (2016) Static test until structural collapse after fatigue testing of a full-scale wind turbine blade. Compos Struct 136:251–257CrossRefGoogle Scholar
- 201.Marín J, Barroso A, París F, Cañas J (2009) Study of fatigue damage in wind turbine blades. Eng Fail Anal 16(2):656–668CrossRefGoogle Scholar
- 202.Spera D (1993) Dynamic Loads in horizontal axis wind turbines. Part II: empirical equations. Wind Power 93:282–289Google Scholar
- 203.Zhu J, Cai X, Pan P, Gu R (2012) Optimization design of spar cap layup for wind turbine blade. Front Arch Civil Eng China 6(1):53–56Google Scholar
- 204.Liao C, Zhao X, Xu J (2012) Blade layers optimization of wind turbines using fast and improved Pso algorithm. Renewable Energy 42:227–233CrossRefGoogle Scholar
- 205.Fuglsang P, Madsen H (1999) Optimization method for wind turbine rotors. J Wind Eng Ind Aerodyn 80(1–2):191–206CrossRefGoogle Scholar
- 206.Benini E, Toffolo A (2002) Optimal Design of horizontal-axis wind turbines using blade-element theory and evolutionary computation. J Sol Energy Eng 124:357CrossRefGoogle Scholar
- 207.Ribeiro A, Awruch A, Gomes H (2012) An airfoil optimization technique for wind turbines. Appl Math Modelling 36(10):4898–4907CrossRefGoogle Scholar
- 208.Ju YP, Zhang CH (2012) Multi-point robust design optimization of wind turbine airfoil under geometric uncertainty. Proc Inst Mech Eng A 226(A2):245–261MathSciNetCrossRefGoogle Scholar
- 209.Huque Z, Zemmouri G, Harby D, Kommalapati R (2012) Optimization of wind turbine airfoil using nondominated sorting genetic algorithm and pareto optimal front. Int J Chem Eng 193:021Google Scholar
- 210.Davari AR, Hasheminejad M, Boorboor A (2013) Shape optimization of wind turbine airfoils by genetic algorithm. Int J Eng Technol 5(1):206–209CrossRefGoogle Scholar
- 211.He Y, Agarwal RK (2014) Shape optimization of NREL S809 airfoil for wind turbine blades using a multi-objective genetic algorithm. In: 32nd AIAA Applied Aerodynamics Conference 2014Google Scholar
- 212.Derakhshan S, Tavaziani A, Kasaeian N (2015) Numerical shape optimization of a wind turbine blades using artificial bee colony algorithm. J Energy Resour Technol 137(5):051210CrossRefGoogle Scholar
- 213.Xudong W, Shen WZ, Zhu WJ, Sørensen JN, Jin C (2009) Shape optimization of wind turbine blades. Wind Energy 12(8):781–803CrossRefGoogle Scholar
- 214.Jeong J, Park K, Jun S, Song K, Lee DH (2012) Design optimization of a wind turbine blade to reduce the fluctuating unsteady aerodynamic load in turbulent wind. J Mech Sci Technol 26(3):827–838CrossRefGoogle Scholar
- 215.Lee S, Lee S, Ryi J, Choi JS (2013) Design optimization of wind turbine blades for reduction of airfoil self-noise. J Mech Sci Technol 27(2):413–420CrossRefGoogle Scholar
- 216.Paluch B, Grédiac M, Faye A (2008) Combining a finite element programme and a genetic algorithm to optimize composite structures with variable thickness. Compos Struct 83(3):284–294CrossRefGoogle Scholar
- 217.Conceição António C (2001) A hierarchical genetic algorithm for reliability based design of geometrically non-linear composite structures. Compos Struct 54(1):37–47CrossRefGoogle Scholar
- 218.Grediac M (2004) Optimal design of a multiperforated composite plate. J Compos Mater 38(16):1401–1423CrossRefGoogle Scholar
- 219.Marler R, Arora J (2004) Survey of multi-objective optimization methods for engineering. Struct Multidiscip Optim 26(6):369–395MathSciNetzbMATHCrossRefGoogle Scholar
- 220.Jureczko M, Pawlak M, Mȩzyk A (2005) Optimisation of wind turbine blades. J Mater ProcessTechnol 167(2–3):463–471CrossRefGoogle Scholar
- 221.Lund E, Stegmann J (2005) On structural optimization of composite shell structures using a discrete constitutive parametrization. Wind Energy 8(1):109–124zbMATHCrossRefGoogle Scholar
- 222.Lund E (2009) Buckling topology optimization of laminated multi-material composite shell structures. Compos Struct 91(2):158–167MathSciNetCrossRefGoogle Scholar
- 223.Lindgaard E, Lund E (2010) Nonlinear buckling optimization of composite structures. Comput Methods Appl Mech Eng 199(37–40):2319–2330MathSciNetzbMATHCrossRefGoogle Scholar
- 224.Monroy Aceves C, Sutcliffe M, Ashby M, Skordos A, Rodríguez Román C (2012) Design methodology for composite structures: a small low air-speed wind turbine blade case study. Mater Design 36:296–305CrossRefGoogle Scholar
- 225.Carrión M, Steijl R, Woodgate M, Barakos G, Munduate X, Gomez-Iradi S (2014) Aeroelastic analysis of wind turbines using a tightly coupled CFD–CSD method. J Fluids Struct 50:392–415CrossRefGoogle Scholar
- 226.Li Y, Castro A, Sinokrot T, Prescott W, Carrica P (2015) Coupled multi-body dynamics and CFD for wind turbine simulation including explicit wind turbulence. Renewable Energy 76:338–361CrossRefGoogle Scholar
- 227.Jonkman J (2015) FAST: an aeroelastic computer-aided engineering (CAE) tool for horizontal axis wind turbines. https://nwtc.nrel.gov/FAST
- 228.HAWC2: Aeroelastic simulation of wind turbines. http://www.hawc2.dk/
- 229.Bazilevs Y, Korobenko A, Deng X, Yan J (2016) Fluid–structure interaction modeling for fatigue-damage prediction in full-scale wind-turbine blades. J Appl Mech 83(6):061010CrossRefGoogle Scholar
- 230.Hughes T, Cottrell J, Bazilevs Y (2005) Isogeometric analysis: cad, finite elements, nurbs, exact geometry and mesh refinement. Comput Methods Appl Mech Eng 194(39–41):4135–4195MathSciNetzbMATHCrossRefGoogle Scholar
- 231.Bazilevs Y, Hsu MC, Scott M (2012) Isogeometric fluid–structure interaction analysis with emphasis on non-matching discretizations, and with application to wind turbines. Comput Methods Appl Mech Eng 249–252:28–41MathSciNetzbMATHCrossRefGoogle Scholar
- 232.Bazilevs Y, Korobenko A, Deng X, Yan J (2015) Novel structural modeling and mesh moving techniques for advanced fluid-structure interaction simulation of wind turbines. Int J Numer Methods Eng 102(766–783):1724MathSciNetzbMATHGoogle Scholar
- 233.Matijaševic D, Terze Z, Vrdoljak M (2015) Composed fluid–structure interaction interface for horizontal axis wind turbine rotor. J Comput Nonlinear Dyn 10(4):041009CrossRefGoogle Scholar
- 234.MacPhee D, Beyene A (2013) Fluid–structure interaction of a morphing symmetrical wind turbine blade subjected to variable load. Int J Energy Res 37(1):69–79CrossRefGoogle Scholar
- 235.Krawczyk P, Beyene A, MacPhee D (2013) Fluid structure interaction of a morphed wind turbine blade. Int J Energy Res 37(14):1784–1793CrossRefGoogle Scholar
- 236.MacPhee DW, Beyene A (2015) Experimental and fluid structure interaction analysis of a morphing wind turbine rotor. Energy 90:1055–1065CrossRefGoogle Scholar

## Copyright information

**Open Access**This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.