Multi-machine Power Systems Installed with VSC-Based Stabilizers
Without loss of generality, it can be assumed that a shunt VSC is installed at a busbar between nodes 1 and 2 in an N-machine power system, as shown in Fig. 7.1. The shunt VSC can be connected to an energy storage system (ESS ), a HVDC, or a static renewable power station, such as a photovoltaic (PV) or fuel cell (FC) power station. It can operate alone as a VSC-based FACTS device, STATCOM (see Sect. 220.127.116.11).
- 1.CIGRE TF 30-01-08 Report (1999) Modelling of power electronics equipment (FACTS) in load flow and stability programs Google Scholar
- 2.Wang HF (1999) Phillips-Heffron model of power systems installed with STATCOM and applications. IEE Proc Part C 146(5):521–527Google Scholar
- 3.Du W (2009) Power system small signal oscillation stability as affected by static synchronous compensator (STATCOM) and energy storage system (ESS). PhD thesis, University of Bath, UKGoogle Scholar
- 4.Wang HF (1999) Applications of modelling UPFC into multi-machine power systems. IEE Proc Part C 3Google Scholar
- 5.Wang HF (2000) A unified model for the analysis of FACTS devices in damping power system oscillations part III: unified power flow controller. IEEE Trans Power Del 3Google Scholar
- 8.Du W, Wu X, Wang HF, Dunn R (2010) Feasibility study to damp power system multi-mode oscillations by using a single FACTS device. Int J Electr Power Energy Syst 32(6):645–655Google Scholar