Efficient storage and transport of cryogenic fluids are of prime importance because of the relatively high cost of liquid production. Vessels for holding liquid hydrogen and helium are always carefully insulated, usually with an insulation which includes vacuum. Less stringent requirements apply to vessels for nitrogen and oxygen. However, the same general rules and techniques apply to the insulation of any cryogenic device. The heat transport to the container holding the cryogenic fluid arises from conduction through mechanical supports and from heat transport across the insulation space.
KeywordsContact Resistance Heat Transport Aluminum Foil Fiber Glass Effective Thermal Conductivity
Unable to display preview. Download preview PDF.
- 1.Lady Dewar (ed.), Collected Papers of Sir James Dewar, Cambridge University Press (1927) Vols. 1 and 2.Google Scholar
- 4.M. Jakob, Heat Transfer, John Wiley and Sons, New York (1949) Vol. 1.Google Scholar
- 5.B. K. Larkin, “A study of the rate of thermal radiation through porous insulating materials,” Ph.D. thesis, University of Michigan, Ann Arbor (1957).Google Scholar
- 6.R. M. Christiansen and M. Hollingsworth, Jr., 1958 Cryogenic Engineering Conference Proceedings.Google Scholar
- 7.M.M. Fulk, “Evacuated powder insulation for low temperatures,” in: Progress in Cryogenics, K. Mendelssohn (ed.) Academic Press, New York (1959).Google Scholar
- 8.R. L. Powell and W. A. Blanpied, Nat. Bur. Standards Circ. 556 (1954).Google Scholar
- 9.R. H. Kropschot, ASHRAE Journal (in press).Google Scholar
- 11.M.M. Fulk. M.M.Reynolds, and R. M. Buriey, Am. Inst, of Physics Handbook, Sect. 6g and 6k.Google Scholar
- 12.B.J. Hunter, R. H. Kropschot, J.E. Schrodt, and M.M. Fulk, present volume, paper C-3.Google Scholar