A Cost-Effective Technology for Arsenic Removal: Case Study of Zerovalent Iron-Based IIT Bombay Arsenic Filter in West Bengal
Arsenic is present in groundwater in some parts of India. Despite the fact that a variety of treatment methods are available, the efficiency of these methods is not fully known. With the revision of Indian standards for permissible levels of arsenic in drinking water to 10 μg/L or lower, it is necessary to develop a treatment method, which meets drinking water standards of 10 μg/L. Iron based adsorbents have been reported to have high affinity for arsenic. Many researchers have also shown that the corrosion of Zero Valent Iron (ZVI) forms Hydrous Ferric Oxide (HFO) which can act as an adsorbent for arsenic. And the oxidation of Fe to Fe has also been reported to oxidize As(III) to As(V). Using this information a ZVI based Arsenic Filter has been developed by Indian Institute of Technology, Bombay. Test units of the IITB-Arsenic Filter have been installed in the field in four villages in West Bengal. From the results, it is clear that the filter is able to consistently achieve arsenic levels around 10 μg/L for initial arsenic concentrations ranging from 0.06 to 0.4 mg/L. The flowrate of the filtered water is aprox. 600 L/hr. Thereby the IITB-Arsenic Filter is able to consistently provide drinking water for about 200 families on a daily basis. The IITB-Arsenic Filter does not require frequent backwashing/cleaning (cleaning frequency is once in 3 months, and is done by the villagers) and therefore has low operation and maintenance costs. Moreover, it does not require monitoring of flow parameters and is easy-to-operate by unskilled personnel. The Fe/As ratio used in the filter is around 20. Low Fe/As ratios mean lesser sludge generation. Thus it is felt that the IITB Arsenic filter is a suitable technology for rural India.
KeywordsArsenic removal Zerovalent iron Iron nails Field trials IIT Bombay arsenic filter
The authors would like to thank the Department of Science and Technology, Government of India, for funding the research work.
- 7.WHO (2008) Guidelines for drinking-water quality: incorporating 1st and 2nd addenda, Vol. 1, Recommendations. – 3rd ed., WHO Library Cataloguing-in-Publication Data, Geneva. Available at http://www.who.int/water_sanitation_health/dwq/gdwq3rev/en/. Accessed on 27 July 2008
- 10.Halsey PM (2000) Arsenic contamination study of drinking water in Nepal, ME thesis submitted to Civil and Environmental Engineering, Massachusetts Institute of Technology, USAGoogle Scholar
- 12.Mathieu J L, Gadgil A J, Kowolik K, Addy SEA (2008) Removing arsenic from contaminated drinking water in rural Bangladesh: Recent fieldwork results & policy implications. 2008 UNC Environmental Symposium Safe and Sustainable Drinking Water in Developing and Developed Countries: Where Science Meets Policy. Available at http://arsenic.lbl.gov/pdf/unc-symposium-aruba.pdf. Accessed on 25 July 2010
- 13.Mathieu JL, Gadgil AJ, Kowolik K, Qazi S, Agogino AM (2010) Design strategies and preliminary prototype for a low-cost arsenic removal system for rural Bangladesh. Lawrence Berkeley National Laboratory: Lawrence Berkeley National Laboratory. LBNL paper LBNL-2696E. Available at http://www.escholarship.org/uc/item/6db8c8vn. Accessed on 25 July 2010
- 14.Ahmad J, Goldar BN, Misra S, Jakariya M (2003) Willingness to pay for arsenic-free, safe drinking water in Bangladesh, World Bank Water and Sanitation Program- South Asia. Available at http://www.cepis.org.pe/bvsacd/arsenico/willing.pdf. Accessed on 25 July 2010
- 22.Mehta VS (2008) Arsenic removal from drinking water using Zero Valent Iron (ZVI). M. Tech. dissertation, Centre for Environmental Science and Engineering, Indian Institute of Technology BombayGoogle Scholar