Failure of last-stage turbine blades in a geothermal power plant
- 193 Downloads
This paper presents an investigation into causes of failure of geothermal steam turbine blades. Several L-0 blades of geothermal steam turbines of 110 MW capacity suffered failures, causing forced outages of the turbines. To assess the causes of failure, the natural frequencies of the blades installed on the rotor were measured in the laboratory. The measured frequencies were compared with the natural frequencies calculated through a finite-element analysis (FEA) of the blade. The FEA was also used to calculate the vibratory stresses on the blade numerically. Also, the investigation analyzed the operational data and the history of the blade failures on several rotors of different units from the same system. The results of previous repairs were reviewed, and metallurgical investigations were conducted to identify the mechanical and metallurgical modes of failure. The results of the investigation showed that the fracture of two blades was attributed to installation and manufacturing errors and aggravated by general deterioration of the blades. The deterioration was caused by the erosion and corrosion process that resulted from moisture condensation in the steam.
Keywordsblade fracture blade vibration corrosion erosion fatigue
Unable to display preview. Download preview PDF.
- 1.J. Kubiak and J.C. García: History of the Unit and Visual Inspection of the Last Step Blade Disk in a Geothermal Turbine of 110 MW, Centre for Research in Engineering and Applied Sciences, CIICAp, Internal Report 53/DM/CIICAp, Cuernavaca, Mexico, 2004.Google Scholar
- 2.R.J. Ortolano and J.C. Hendelman: “Adjustments to Steam Turbine Blade Design Available during Blade Repair and Refurbishment,” Proc. ASME/IEEE Power Gen. Conf., Philadelphia, Sep 25–29, 1988.Google Scholar
- 3.K. Borst and F. Koch: Examination of Damaged Turbine Blades, ASME Joint Power Gen. Conf., Houston, 1996.Google Scholar
- 4.R.J. Ortolano: “Modification of Troublesome Blading Design by Converting Existing Steam Turbine Blading to Continuous Tie Structures,” II Latin American Turbomachinery Conf., Cuernavaca, Mexico, Feb 1993, pp. 125–32.Google Scholar
- 5.R.J. Ortolano: “Current Industry Blade Problems,” II Latin American Turbomachinery Conf., Cuernavaca, Mexico, Feb 1993, pp. 133–35.Google Scholar
- 6.J. Kubiak, J.C. García, and F.Z. Sierra: Excitation Force Coefficients Computation of the Last Step Blade Disk, and Due to Flow Pressure Field of the Stationary Blades, in a Geothermal Turbine of 110 MW and 37.5 MW, Centre for Research in Engineering and Applied Sciences, CIICAp, Internal Report 60/DM/CIICAp, Cuernavaca, Mexico, 2004.Google Scholar
- 7.J. Kubiak and J.C. García: MEF Analysis and Useful Life Estimation of the Last Step Blade Disk in a Geothermal Turbine of 110 MW, Centre for Research in Engineering and Applied Sciences, CIICAp, Internal Report 61/DM/CIICAp, Cuernavaca, Mexico, 2004.Google Scholar