Interactive effects of temperature, organic carbon, and pipe material on microbiota composition and Legionella pneumophila in hot water plumbing systems
- 1.5k Downloads
Several biotic and abiotic factors have been reported to influence the proliferation of microbes, including Legionella pneumophila, in hot water premise plumbing systems, but their combined effects have not been systematically evaluated. Here, we utilize simulated household water heaters to examine the effects of stepwise increases in temperature (32–53 °C), pipe material (copper vs. cross-linked polyethylene (PEX)), and influent assimilable organic carbon (0–700 μg/L) on opportunistic pathogen gene copy numbers and the microbiota composition, as determined by quantitative polymerase chain reaction and 16S rRNA gene amplicon sequencing.
Temperature had an overarching influence on both the microbiota composition and L. pneumophila numbers. L. pneumophila peaked at 41 °C in the presence of PEX (1.58 × 105 gene copies/mL). At 53 °C, L. pneumophila was not detected. Several operational taxonomic units (OTUs) persisted across all conditions, accounting for 50% of the microbiota composition from 32 to 49 °C and 20% at 53 °C. Pipe material most strongly influenced microbiota composition at lower temperatures, driven by five to six OTUs enriched with each material. Copper pipes supported less L. pneumophila than PEX pipes (mean 2.5 log10 lower) at temperatures ≤ 41 °C, but showed no difference in total bacterial numbers. Differences between pipe materials diminished with elevated temperature, probably resulting from decreased release of copper ions. At temperatures ≤ 45 °C, influent assimilable organic carbon correlated well with total bacterial numbers, but not with L. pneumophila numbers. At 53 °C, PEX pipes leached organic carbon, reducing the importance of dosed organic carbon. L. pneumophila numbers correlated with a Legionella OTU and a Methylophilus OTU identified by amplicon sequencing.
Temperature was the most effective factor for the control of L. pneumophila, while microbiota composition shifted with each stepwise temperature increase. While copper pipe may also help shape the microbiota composition and limit L. pneumophila proliferation, its benefits might be constrained at higher temperatures. Influent assimilable organic carbon affected total bacterial numbers, but had minimal influence on opportunistic pathogen gene numbers or microbiota composition. These findings provide guidance among multiple control measures for the growth of opportunistic pathogens in hot water plumbing and insight into the mediating role of microbial ecological factors.
KeywordsHot water Premise plumbing Legionella Opportunistic pathogen Temperature control Pipe material
Preventing proliferation of opportunistic pathogens (OPs) in building plumbing is an important step in delivery of safe drinking water to consumers. In particular, Legionella pneumophila is an OP that has become the leading cause of drinking-water-related disease in developed countries . L. pneumophila is especially challenging to control because it establishes and grows as part of the native plumbing microbiota, even under oligotrophic conditions and in the presence of disinfectants. L. pneumophila can thrive in biofilms, partly owing to the protection provided by amoeba hosts, inside which they preferentially amplify . Some amoebae occurring in drinking water, such as Acanthaomeba spp. and Naegleria fowleri, are also OPs [3, 4, 5]. In considering options for intentionally shaping the microbiota in building plumbing systems, temperature and pipe material are practical factors that can be directly controlled at the building level, while assimilable organic carbon (AOC) is influenced by both municipal water treatment and conditions in the building plumbing.
Elevating the water temperature > 60 °C can be highly effective for killing and inhibiting L. pneumophila and other OPs [6, 7]. However, the reality is that such “hot” temperatures are difficult to maintain throughout the system, resulting in “warm” water conditions that are highly conducive to pathogen growth in much of the building plumbing environment . Water heaters pose a risk for promoting microbial illness when operated between 30 and 54 °C  or whenever the water coming out of the heaters is below 60 °C or fails to remain consistently above 55 °C throughout the premise plumbing . Despite the well-established benefits of elevated temperatures for OP control, some guidelines for water heater operation recommend temperatures as low as 48 °C [11, 12] because of concerns about scalding, scaling, and energy conservation, with only some recommending higher temperatures [13, 14, 15]. Besides direct effects on pathogens, temperature is a fundamental selective force in shaping the broader microbiota of tap water .
Within a building, pipes and plumbing components are made from a vast array of materials, all with the potential to influence microbial regrowth . The high surface area to volume ratio in the home compared to that of the main water distribution system can exacerbate microbial growth, while the higher temperatures encountered in hot water lines can mediate the influence of materials [17, 18]. Plastic pipes, especially cross-linked polyethylene (PEX), can release substantial amounts of organic carbon, stimulating growth of heterotrophic bacteria and amoebae [18, 19, 20, 21]. Plastic pipes can also release phosphate, antioxidants, and complex non-biodegradable organics [19, 22, 23]. Copper, on the other hand, has antimicrobial properties and is commonly applied together with silver for on-site disinfection [24, 25]. However, when used as a pipe material, the disinfectant properties of copper can vary [26, 27, 28, 29]. For example, in one model distribution system, copper pipe seemed to control L. pneumophila growth, but only for a limited time , while in a field study, positive correlations between copper fixtures of unknown age and L. pneumophila were noted . Another study found no difference in Legionella spp. abundance associated with PEX versus copper in an office building, but did note that copper suppressed other potential OPs (i.e., mycobacteria), demonstrating that different OPs can vary in their associations with materials and that individual microbiota members can behave differently .
Limiting the levels of nutrients in treated and distributed water could enable water utilities to reduce risk of pathogen regrowth at the community-scale. AOC is a common target, with proposed limits of 10 μg/L  and 32 μg/L  in non-disinfected water or 100 μg/L in water carrying disinfectant residual . However, it is important to also consider that AOC can be produced during distribution and in building plumbing, for example, via nitrifying and other autotrophic organisms  or through leaching from plastic pipes . Moreover, expectations for AOC control have been based on studies of distribution system water under continuous-flow conditions, whereas premise plumbing operates under warm semi-stagnant conditions. A prior controlled study simulating the premise plumbing environment noted that total organic carbon level was not the master variable controlling proliferation of L. pneumophila or Mycobacterium avium .
Here, we employed simulated water heaters (SWH) to establish a fundamental understanding of interactive effects of temperature, pipe material, and AOC levels on the microbiota structure and L. pneumophila numbers with time. SWHs were equipped with copper or PEX pipe sections, dosed in triplicate with AOC from 0 to 700 μg/L, and subject to an incrementally increased temperature regime. Effects of copper pipe were further explored in complementary experiments in which Cu2+ was dosed into SWHs. In addition to Illumina amplicon sequencing of 16S rRNA genes, L. pneumophila, Vermamoeba vermiformis, and Acanthamoeba spp. gene markers were monitored by quantitative polymerase chain reaction (qPCR). Insights gained help understand how the microbiota composition is shaped, intentionally and unintentionally, in hot water plumbing systems.
Simulated water heaters (SWHs)
SWHs consisted of 125-mL glass bottles equipped with PEX or copper pipe sections (8 Φ½ in. × 1.25 cm), a 2-mm layer of glass beads (Φ1 mm), and polytetrafluoroethylene caps. SWHs were operated at 32 °C for 2.5 years prior to the present study. During the 2.5 years, SWHs were initially fed with synthesized water and/or Blacksburg tap water (water was treated the same way as described previously , unfiltered with 0.45-μm filters) to allow the development of mature and complex drinking water biofilms in SWHs. SWHs were also inoculated with approximately 2.03 × 105 gene copies/mL L. pneumophila (ATCC 33152, 33733, 33734, 33823, a mixture of environmental isolates, to maximize the likelihood that L. pneumophila established in the systems), 2.08 × 103 gene copies/mL Acanthamoeba polyphaga (ATCC 30871), and 1.46 × 103 amoeba/mL Vermamoeba vermiformis (ATCC 50237) after the first 4 months of the 2.5 years. On day 0 of the present study (defined as 2.5 years after initial setup), SWHs were cross-inoculated during a routine water change by pooling 100 mL water from each, mixing, and returning 1 mL of the mixture to each SWH together with 100 mL freshly prepared influent (details below). Cross-inoculation was done in this manner to limit interruptions to delivery of fresh nutrients during normal water changes.
Influent water was prepared from local Blacksburg, VA, water, which is usually chloraminated. Influent was prepared by breakpoint chlorinating cold tap water through incremental addition of chlorine while measuring total residual chlorine using the Hach reagent Powder Pillows (Loveland, CO), totaling 2–5 mg/L chlorine addition. As per breakpoint chlorination kinetics with chloraminated waters, residual chlorine level initially increased, then decreased and increased again at the breakpoint, when chlorine addition was stopped. Breakpoint chlorinated water was further prepared by heating it to 90 °C for 10 min, passing it through a biologically active granular activated carbon (GAC) filter (Undercounter Standard Filter Unit, Model GX1S01R, General Electric, Fairfield, CT), filtering with a 0.45-μm polyvinylidene fluoride (PVDF) filter to remove colloidal carbon particles and most microbes to lower background carbon level and to reduce seasonal variations in influent water microbiota, and adjusting the pH to 7.5 ± 0.1. Three times a week, 100 of the 120 mL total volume was gently decanted (i.e., without mixing) and replaced with freshly prepared influent water. Water changes and sample collection were conducted using aseptic technique.
Five levels of influent AOC were investigated by dosing influent water with an acetate and glucose mixture (0, 5, 30, 150, and 700 μg C/L). While organic carbon in drinking water is typically complex in nature and not directly assimilable, as it is largely derived from natural organic matter and plumbing components, acetate and glucose were selected because they are highly assimilable by a wide variety of bacteria, common intermediates of degradation of more complex organic carbon forms, and commonly employed in assimilable organic carbon assays . Triplicate SWHs represented each pipe material and AOC level.
Temperature was elevated in a stepwise fashion (2.5–4 °C every 5–7 weeks) in all SWHs, except for an extra temperature control set for each pipe material maintained at 32 °C and receiving 700 μg/L AOC. Samples were collected during regular water changes at the end of each temperature period, specifically, on days 1, 27, 58, 106, 141, 183, 224, 267, and 316, with temperatures of 32, 32, 32, 34.5, 37, 41, 45, 49, 53 °C, respectively.
Temperature was maintained with a New Brunswick Scientific Classic Series C24 Incubator Shaker (Edison, NJ, USA). Upon malfunction on days 274 and 277, SWHs were transferred to a New Brunswick Scientific Innova 43 Incubator Shaker (Edison, NJ, USA) for the remainder of the experiment. During malfunction, the incubator reached 60 °C for no more than 24 h.
Cu2+ dosing experiment
Six new SWHs were established to investigate the impact of copper ion (Cu2+) dosing. These new glass bottles were amended with PEX pipe sections (8 Φ ½ in. × 1.2 cm) and incubated at 32 °C. Water was prepared and changed as described above (no AOC dosed) three times per week. In week one (3 times change), influent was spiked with 34 mL pooled effluent from the temperature experiment SWHs. Starting from day 22, influent pH was adjusted from 7.5 to 7.0. Soluble Cu2+ was dosed into three SWHs at increasing levels (0, 5, 30, 150, and 1000 μg/L) using a stock 0.0014 M CuSO4 solution with 14 days between every increase, while the other three SWHs served as controls with no Cu2+ dosing. This experiment was run for a total of 90 days.
Copper ions (Cu2+) were measured using inductively coupled plasma mass spectrometry (ICP-MS). Ten milliliter from each SWH were acidified by adding 2% nitric acid by mass prior to analysis. Soluble copper was operationally defined by that passing through a 0.45-μm pore size filter.
Total organic carbon
Total organic carbon (TOC) was measured with a Sievers 5310 C Laboratory TOC-MS Analyzer using the Data Pro 5310 C Computer Program. Samples were analyzed using 30 mL from each SWH or by pooling 10 mL from each triplicate SWH. Samples were acidified with phosphoric acid and sparged with N2 gas to purge inorganic carbon prior to analysis.
One hundred milliliter of SWH water was filtered onto sterile 0.22-μm pore size mixed cellulose ester filters (Millipore, Billerica, MA, USA). DNA was extracted using the FastDNA® SPIN Kit (MP Biomedicals, Solon, OH, USA) according to the manufacturer’s instructions.
Quantitative polymerase chain reaction
The quantitative polymerase chain reaction (qPCR) method was applied to quantify the macrophage infectivity potentiator (mip) gene specific to L. pneumophila , the 18S rRNA gene of V. vermiformis , the 18S rRNA gene of Acanthamoeba , and bacterial 16S rRNA genes  using protocols previously optimized for drinking water samples . Q-PCR was carried out using a CFX96™ Real Time system (Bio-Rad, Hercules, CA, USA), including a calibration curve of seven to eight points and negative controls in each run.
Culturing for detection of L. pneumophila was conducted by heating 100 μL water samples to 50 °C for 30 min and directly plating onto buffered charcoal yeast extract (BCYE) agar according to published methods [41, 42].
Illumina 16S rRNA gene amplicon sequencing
Illumina amplicon sequencing of bacterial 16S rRNA genes was applied to triplicate SWHs corresponding to both pipe materials, three levels of dosed AOC (0, 30, and 700 μg/L), and six temperature levels (32, 37, 41, 45, 49, and 53 °C), along with corresponding constant temperature controls sampled on the same days (days 58, 141, 183, 224, 267, and 316). 16S rRNA genes were amplified with barcoded primers targeting the V4 region according to the Earth Microbiome Project Illumina Amplification Protocol , followed by sequencing with an Illumina MiSeq Sequencer (2 × 250 bp) at the Virginia Bioinformatics Institute (Blacksburg, VA, USA). Sequences were deposited to the European Nucleotide Archive under project accession number PRJEB11665.
Microbial numbers (gene copies/mL water) were log-transformed [log10(x + 1)], with L. pneumophila numbers below detection treated as zero. T tests and correlation analyses were performed in JMP Pro 12 (Cary, NC, USA). 16S rRNA gene sequences were analyzed in mothur (1.36.0). Sequences with an average similarity ≥ 97% were assigned an operational taxonomic unit (OTU). Each sample was rarefied to 12,430 sequences for comparison. Alpha and beta diversities were determined as mean values of 1000 random rarefactions. Bray-Curtis similarity matrix and jclass matrix were applied to analysis of similarity (ANOSIM) in mothur, non-metric multi-dimensional scaling (NMDS) in Primer-E 6.0 (Plymouth, UK), and Adonis in R. Adonis analysis served to quantify the relative influences of temperature, pipe material, and dosed AOC level in shaping the hot water microbiota composition. “Persistent” OTUs were defined as being detected at all temperatures for any AOC level after rarifying to 12,430 sequences/sample. “Enriched” OTUs were those OTUs firstly identified by an indicator in mothur and then selected either having an indicator value > 80 or a relative abundance > 1%.
Total bacterial numbers
AOC was amended to the SWHs as glucose and acetate and directly measured as TOC in the SWH influent and effluent at two time points, corresponding to the 37 and 53 °C experimental conditions. Influent TOC (TOCin) was confirmed to be proportional to the dosed AOC (ρ = 0.89–0.99) (Additional file 1: Fig. S1A). ΔTOC (ΔTOC = TOCin−TOCout) was calculated to represent reduction in organic carbon due to biodegradation and TOC generated (e.g., via autotrophy or leaching from pipes). At 37 °C, ΔTOC was positive (i.e., highly amenable to biodegradation) and correlated with dosed AOC for both pipe materials (Pearson correlation coefficient ρ = 0.87–0.88) (Additional file 1: Fig. S1B). At 53 °C, ΔTOC in SWHs with copper pipe remained low, regardless of the level of dosed AOC, suggesting that biodegradation was somewhat inhibited. ΔTOC values in SWHs with PEX pipe were consistently negative (TOCout > TOCin), indicating leaching of organic carbon from PEX pipe. Under conditions amenable to biodegradation (37 °C with both pipe materials and 53 °C with copper), ΔTOC was strongly correlated with total bacterial numbers (measured as 16S rRNA gene copy numbers) (ρ = 0.87, p < 0.0001) (Additional file 1: Fig. S2), consistent with microbial activity consuming TOC.
L. pneumophila and amoebae gene markers
Both pipe material and temperature significantly affected L. pneumophila and V. vermiformis gene copy numbers (hereafter “numbers”) (Fig. 2a). Positive correlations between individual microorganisms and supplemented AOC were only occasionally found (Fig. 2b), primarily driven by the highest dose(s) of AOC.
The effect of pipe material was best illustrated in the first three samplings, before increasing the temperature, and the control SWHs at 32 °C (Fig. 1). SWHs with PEX pipe had consistently higher numbers (2.5 log10) of L. pneumophila and lower numbers (3.1 log10) of V. vermiformis compared to SWHs with copper pipe.
Copper ion (Cu2+) dosing
Relative impacts of the three factors and their interactions on hot water microbiota. Results shown as analysis of similarity (ANOSIM) global R statistics
Explained variations in microbiota
Overarching factor test ANOSIM
R = 0.63*
Pipe material (M)
R = 0.16*
R = 0.002 (p > 0.05)
T × M
T × C
C × M
T × C × M
Shannon diversity decreased as temperature increased from 41 to 45 °C, but then significantly increased (1.2–1.7 times) at 49 and 53 °C, regardless of pipe material (compared to temporal changes observed in the control SWHs, Fig. 6b). Together with increased diversity (Shannon index) at 49 and 53 °C, there was more evenness (1.3–1.8 times for both copper and PEX) and lower richness (0.4–0.5 times for PEX only). SWHs with PEX usually had higher Shannon diversity than copper. The effects of dosed AOC level on Shannon diversity varied with temperature (Additional file 1: Fig. S4). The highest AOC level (700 μg/L) resulted in a lower Shannon index, with few exceptions (copper and PEX at 41–45 °C, PEX at 53 °C).
OTUs persisting across temperatures and pipe materials
Some OTUs persisted from warm (32 °C) to hot (53 °C) conditions, indicating their resistance or tolerance to this substantial temperature shift. A total of 14 OTUs were detected across all temperatures in both copper and PEX (Fig. 6c). Although their relative abundances shifted with temperature and pipe material, together, these persistent OTUs accounted for ~ 50% of the microbiota at all temperatures except 53 °C (< 20% at 53 °C).
OTUs selectively enriched at various temperatures
Some OTUs were enriched mainly at a specific temperature. Each set of 4–7 OTUs was identified to have significantly higher abundance at one temperature than all other temperatures, across both pipe materials and all AOC levels (Fig. 6d, Additional file 1: Table S2). The selectively enriched OTUs at 41, 49, or 53 °C were highly specific to temperature, displaying high abundance (18–78%) at the corresponding temperature, but becoming “rare” (total abundance < 5%) at all other temperatures.
OTUs selectively enriched by different pipe materials
Genera containing pathogens
Several genera were of particular interest because they potentially contain OPs. Temperature was the most influential factor to the relative abundances of Mycobacteria, Pseudomonas and Stenotrophomonas, peaking at 49, 53, and 53 °C, respectively, regardless of pipe material (Fig. 3a, Additional file 1: Fig. S5). Dosed AOC level up to 30 μg/L was associated with an increase in the relative abundance of Mycobacteria. Among the four OP-containing genera tracked in this study, only the relative abundance of Legionella was significantly influenced by pipe material (Fig. 3b), remaining low in SWHs with copper (< 0.2%), but peaking at 41 °C with a relative abundance of >1.5% of the total microbial composition in the PEX pipe condition.
Variance among replicates
Variance in microbiota composition among SWH replicates (estimated as pairwise Bray-Curtis dissimilarities) increased markedly at 49 and 53 °C in SWHs with copper pipe, but remained relatively stable in SWHs with PEX over the range of temperatures (Additional file 1: Fig. S6). Dissimilarities among replicates were higher in PEX (~ 30%) than copper (~ 12%) among SWHs at lower temperatures (≦45 °C), with most dissimilarity among replicates attributed to the 700 μg/L AOC condition.
Comparison of microbiota and qPCR profiling
We further compared microbiota and qPCR analyses by correlating the relative abundances of L. pneumophila calculated from qPCR with the relative abundances of the 100 most dominant OTUs identified by the amplicon sequencing. The strongest positive correlation with L. pneumophila numbers was a Legionella OTU (OTU69) (ρ = 0.47). The second highest correlation was with an OTU with a high sequence similarity to Methylophilus (ρ = 0.37), which is a known endosymbiont of Acanthamoeba .
Temperature, material, and AOC all affected hot water microbial composition and L. pneumophila occurrence. Here, we systematically discuss the relative importance of each factor and interactive effects among them.
While temperature control is an established method of preventing OP regrowth , recommendations for water heater settings vary due to conflicting priorities and goals [11, 12, 13, 14]. In this study, a temperature of 53 °C uniformly reduced L. pneumophila and V. vermiformis (a key host for L. pneumophila) to below detection, regardless of AOC or pipe material conditions (Fig. 1b, c). This supports the concept of temperature as a diagnostic of risk of OP colonization . It also suggests that 55 °C, a temperature considerably lower than the standard set point 60 °C, can technically be effective if achieved homogeneously in the system, as was the case in these SWHs. However, water temperature in realistic water heaters and hot water distribution pipes is typically lower than the set point due to cooling in distal pipes or mixing with cold water [8, 46]. In a recent pilot-scale simulation, L. pneumophila remained detectable at the tap and in the recirculating line even when the water heater was set at 58 °C .
Based on OP-containing genera identified by amplicon sequencing, mid-range temperatures (41–49 °C) could be more problematic than the assumed “worst-case scenario” of 32 °C. For example, Mycobacterium spp., while consistently detected at all temperatures in both pipe materials, peaked at 49 °C (Fig. 3a). L. pneumophila numbers peaked in PEX reactors when maintained at 41 °C (Fig. 1b), matching a spike in calculated relative abundance and both relative and calculated absolute abundance of Legionella spp. based on amplicon sequencing (Figs. 3 and 8). The peak concentrations of L. pneumophila in this study (5.2 log10 mip gene copies/mL) may even surpass the critical threshold for L. pneumophila infection of 107CFU/L, which was identified in a quantitative microbial risk assessment model .
While temperature was the most influential factor inducing differences in microbiota structure, there were 14 persistent OTUs that dominated at most temperatures for both materials (Fig. 6c). These OTUs include some implicated in regrowth during stagnation (Comamonadaceae, Bradyrhizobium) , some commonly identified in drinking water biofilms (Mycobacterium and Sphingobacteriales) , some likely involved in nitrogen cycling (Nitrosomonadaceae)  and some potential methanotrophs known to degrade chlorine byproducts (Methylocystaceae) . The former two are likely related to the imposed hydraulic cycle of 2–3 days between water changes and constant seeding from mature SWH biofilms, a phenomenon previously observed in other systems . The latter two may indicate that the breakdown of disinfection byproducts continues to influence SWHs, even though the influent water was breakpoint chlorinated.
The microbiota shift at 53 °C was mostly attributed to Firmicutes. While Firmicutes were previously associated with adoption of a new chloramine disinfection system in a hospital , in this study, it is their thermophilic nature that likely provided them a selective advantage . Actinobacteria were also enriched at this temperature, consistent with the selective advantage of high GC content and Gram-positive characteristics at high temperature.
Interestingly, the community changes occurring at each temperature increase could be largely accounted for by just a few OTUs that were enriched at individual temperatures (Fig. 6d). These OTUs are particularly interesting at 41 °C, when L. pneumophila peaked in PEX reactors and the communities with both materials began to converge. Novosphingobium, an aromatic carbon degrader , and Caulobacter were favored. Caulobacter was previously associated with shower hose biofilms that formed under similar conditions (41 °C with 24-h stagnation) and consistently contained Legionella . Together with the previously mentioned Methylophilus, these OTUs may be indicators for Legionella issues.
This study clearly indicates that temperature will induce shifts in hot water microbial structure, even with differences as little as 4 °C. While previous studies have shown wide-scale differences between hot and cold water microbiota , to the authors’ knowledge, this is the first study to examine such fine-scale adaptation to temperature under conditions representative of building plumbing. The fine-scale temperature adjustment approach selected here allowed the microbial community to gradually adapt and helped to identify threshold temperatures likely to be effective for opportunistic pathogen control under various conditions. Such fine-scale adjustments may also be made in the real world in seeking to address concerns such as energy, scalding, or cost. It is important to note, however, that a dramatic “heat-shock” type temperature adjustment would likely have resulted in microbial community structures distinct from those observed here. While incremental shifts may allow bacteria to build up resistance to higher temperature, sudden increase from 32 to 53 °C would trigger a heat-shock response .
Copper pipe had no measureable effect on total bacterial numbers in our long-term aged pipe study (Fig. 1a). Although copper pipes may retard initial biofilm formation relative to plastic pipes , often, studies are conducted using a new pipe material, where the effects of carbon leaching from plastics and Cu+2 from copper pipes are greatest. This experiment was conducted with pipes that were experimentally operational and aged for > 3 years, greatly exceeding prior studies of 30 days , 1 year [16, 18], and 2 years . Although a general toxicity of copper on total bacterial numbers was not observed, aged copper pipe exerted selective pressure that benefitted some microorganisms over others, as illustrated by the microbiota composition (Fig. 7) and response of specific OPs and organisms of interest.
There is some evidence that copper pipe can be beneficial for some free-living amoeba (FLA) hosts for L. pneumophila . In this study, SWHs with aged copper pipes had higher concentrations of V. vermiformis than PEX reactors at low temperatures (Fig. 1b), while Acanthamoeba did not respond to Cu+2 dosing (Additional file 1: Fig. S3). Although co-occurrence of FLA and L. pneumophila has been reported , specific FLA and L. pneumophila may respond differently to stresses like temperature , potentially explaining the discrepancy in L. pneumophila versus V. vermiformis response in this study. Additionally, although potential copper pipe toxicity towards Mycobacterium was observed in a prior building survey , Mycobacterium was persistent on both materials in this study.
Below 45 °C, copper pipe consistently suppressed L. pneumophila numbers compared to PEX, even after 2.5 years of conditioning and operation of the present experiment for over a year (Fig. 1b). The Cu+2 dosing study made it possible to further examine the selective pressure. A concentration as low as 5–30 μg/L effectively inhibited L. pneumophila at 32 °C (Fig. 4), indicating that the lower L. pneumophila numbers in SWHs with aged copper pipe than PEX pipe at day 1 may be due to its sensitivity to Cu+2 released from copper pipe during the acclimation period.
At lower temperatures, there was a clear distinction in the microbiota structure associated with copper versus PEX (Fig. 7). The OTUs associated with PEX represented a variety of ecological niches consistent with the leaching of diverse organic carbon from the plastic [19, 23]. For example, Phenylobacterium has a specific metabolism associated with herbicides and complex carbon  and Sediminibacterium was previously associated with biofilms on PVC-P . The wide range of carbon niches could also account for the higher Shannon diversity observed in PEX SWHs. Previously, a higher diversity was also observed in biofilms on plastic than on copper .
The OTUs specific to the copper condition were associated with adaptive metabolism and resistance to harsh environments, likely reflecting the toxicity of the copper pipes and lowered carbon availability compared to the PEX condition. For example, some are known for tolerance to acidic conditions (Acidobacteriaceae)  and preference for low organic carbon levels (Hyphomicrobiaceae) . Pseudomonas was also persistent in Cu SWHs, and the opportunistic pathogen, P. aeruginosa, has previously demonstrated copper resistance . At higher temperatures, the distinction between materials became less obvious.
Prior studies have yielded conflicting conclusions with respect to the relative effects of copper versus plastic (PEX, PVC, C-PVC) pipes on levels of L. pneumophila and other organisms [16, 18, 21, 22, 55, 63, 64]. However, since temperature can alter the water chemistry (e.g., pH) and overall tendency towards dissolution of copper ions from pipes , it is critical to consider both water chemistry and physiochemical parameters when determining the effectiveness of copper pipe in controlling L. pneumophila. We hypothesize that the influence of pipe material is highly dependent on water temperature, which governs both leaching of organic carbon from plastics and copper dissolution chemistry.
In this study, higher temperature decreased the dissolution of total copper from the pipe (Additional file 1: Fig. S7), and further, this copper also likely had decreased solubility . Thus, as one selective pressure was increased (temperature), another selective pressure was relieved (copper), perhaps accounting for the converging communities and similar response of L. pneumophila between pipe materials at these temperatures. SWHs with aged copper pipe at high temperatures had a noticeable increase in microbiota dissimilarity among replicates (Additional file 1: Fig. S6), possibly because new niches opened up by reduced copper pressure were quickly occupied by different organisms among the replicates.
At 53 °C, there was strong evidence of organic carbon leaching from the PEX pipes. The negative ΔTOC in PEX reactors at higher temperature indicated that leaching of organic carbon from the pipe exceeded the organic carbon consumed by microbes. Although the pipes were aged and carbon leaching tends to diminish over time, higher temperatures can still greatly increase the amount of TOC leaching from pipes . There was also a strong shift in the microbiota structure at 53 °C in PEX reactors, especially when dosed AOC was low (0, 30 μg/L) (Additional file 1: Fig. S8). The communities with little dosed AOC (0, 30 μg/L) likely adapted to utilize the newly dominant PEX-derived carbon source, while those with higher dosed AOC (700 μg/L) could continue the previous metabolic patterns utilizing dosed AOC.
AOC has been extensively studied in water distribution main systems (from treatment plant or source to consumers), with reduction below 100 or 10 μg/L AOC associated with effective control of regrowth, depending on other limiting factors [30, 31, 32]. However, these limits have not been validated for controlling regrowth within the hot water plumbing environment, where AOC can also be generated from pipes, especially when stagnation events greater than 6 h are common [34, 46]. In this experiment, the incoming carbon concentration was first minimized via biologically active GAC filtration, in order to reduce the background TOC/AOC and exclude potential effects of seasonal AOC variations.
Increasing AOC levels resulted in more bacteria at temperatures ≤ 45 °C, consistent with consumption of TOC and incorporation into biomass (Fig. 2a, Additional file 1: Figs. S1 and S2). However, in PEX reactors at 53 °C, there was a negative correlation between dosed AOC and 16S rRNA genes (Fig. 2a). With temperature-dependent leaching from pipes, local carbon production diminished the importance of the influent water, as has been previously observed with plastic pipes [34, 67].
Although other studies have found correlations between TOC and L. pneumophila in flowing hot  and cold water systems , in this study, only the highest levels of supplemented AOC corresponded to an increase in L. pneumophila or other organisms of interest, while high levels even seemed to suppress Mycobacteria. Thus, there may be a threshold at which AOC control is no longer effective for specific OPs, as suggested by Williams et al. . Carbon production within the building (e.g., plastics leaching carbon) and specific preferences of potential pathogens may change the community response to increased carbon. For example, some organisms, like Mycobacteria and P. aeruginosa, may prefer a lower range of AOC because they can out-compete others for carbon in oligotrophic stagnant environments, as has been previously observed [34, 69]. Regardless, L. pneumophila and FLA are not directly dependent on carbon available in the water, especially under warm stagnant conditions, but rather derive largely secondary influences of carbon and broader microbiota as an intermediary [70, 71].
Finally, the low Shannon diversity and high dissimilarity among replicate SWHs in the 700 μg/L AOC condition may be related to the semi-batch nature of the reactors. A high concentration of easily assimilable organic carbon may select for fast-growing organisms that out-compete others for secondarily limiting nutrients (nitrogen, phosphorus), ultimately limiting diversity. Which bacteria dominate in semi-batch growth reactor can vary considerably among replicates. A notable exception to this trend occurred in PEX reactors at 53 °C, when carbon leaching introduced new carbon sources that were better utilized in the low carbon addition conditions.
This study brings to light the importance of interactive effects of temperature, pipe material, and AOC in shaping the microbiota composition and controlling OPs in building plumbing. While temperature was the strongest factor, increasing temperature did not linearly reduce concentrations of OPs or amoeba hosts, which peaked at temperatures 41–49 °C. L. pneumophila and the two amoebae were reduced to below detection when the temperature was consistently maintained at 53 °C. Temperature also mediated the leaching behavior of pipes, reducing the selectively inhibitive effect of copper pipes and increasing TOC release from plastic pipes. AOC correlated with total bacteria, but not with L. pneumophila.
We acknowledge Brittany Flittner, Rachel Thomas, and Christine Pankow for significant contributions to reactor maintenance and lab work and Jeffery Parks for assistance with ICP measurements.
This study was funded by the Alfred P. Sloan Foundation Microbiology of the Built Environment Program, the U.S. National Science Foundation (CBET Awards No. 1033498 and 1336650), and the Institute for Critical Technology and Applied Science Center for Science and Engineering of the Exposome.
Availability of data and materials
The sequencing data generated in this study are available in the European Nucleotide Archive under project accession number PRJEB11665. All other data is available in this publication.
CP contributed to the study design, produced the data, and contributed to the data analysis and manuscript writing. DD analyzed the data, produced the figures, and contributed to the manuscript writing. ME and AP contributed to and oversaw the study design, data analysis, and manuscript writing and editing. All authors read and approved the final manuscript.
Ethics approval and consent to participate
Consent for publication
The authors declare that they have no competing interests.
Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
- 3.Shakoor S, Beg MA, Mahmood SF, Bandea R, Sriram R, Noman F, et al. Primary amebic meningoencephalitis caused by Naegleria fowleri, Karachi, Pakistan. Emerg Infect Dis. 2011;17:258–61. Centers for Disease Control and Prevention, Available from: http://www.ncbi.nlm.nih.gov/pubmed/21291600.CrossRefPubMedPubMedCentralGoogle Scholar
- 4.Yoder JS, Straif-Bourgeois S, Roy SL, Moore TA, Visvesvara GS, Ratard RC, et al. Primary amebic meningoencephalitis deaths associated with sinus irrigation using contaminated tap water. Clin Infect Dis. 2012;55:e79–85. Oxford University Press. Available from: http://www.ncbi.nlm.nih.gov/pubmed/22919000.CrossRefPubMedGoogle Scholar
- 6.Dennis PJ. Legionella in the United Kingdom and water quality in buildings. ASHRAE Trans. 1991;1991:271–4.Google Scholar
- 7.Stout JE, Best MG, Yu VL. Susceptibility of members of the family Legionellaceae to thermal stress: implications for heat eradication methods in water distribution systems. Appl Environ Microbiol. 1986;52:396–9. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/3752999.PubMedPubMedCentralGoogle Scholar
- 8.Rhoads WJ, Ji P, Pruden A, Edwards MA. Water heater temperature set point and water use patterns influence Legionella pneumophila and associated microorganisms at the tap. Microbiome. 2015;3:67. Available from: http://www.pubmedcentral.nih.gov/articlerender.fcgi?artid=4666224&tool=pmcentrez&rendertype=abstract.CrossRefPubMedPubMedCentralGoogle Scholar
- 9.Wadowsky RM, Yee RB, Mezmar L, Wing EJ, Dowling JN. Hot water systems as sources of Legionella pneumophila in hospital and nonhospital plumbing fixtures. Appl Environ Microbiol. 1982;43:1104–10. American Society for Microbiology (ASM). Available from: http://www.ncbi.nlm.nih.gov/pubmed/7103477.PubMedPubMedCentralGoogle Scholar
- 12.Energy Star Program, US Environmental Protection Agency, US Department of Energy. Start saving now: ENERGY STAR. 2016 [cited 2016 Oct 2]. Available from: https://www.energystar.gov/campaign/waysToSave?tagIdList=Featured-Advice.Google Scholar
- 13.World Health Organization Europe. Policies to reduce unintentional injuries from falls, drowning, poisoning, fires and choking in children and adolescents. WHO Fact Sheet No. 2.6. 2007 [cited 2016 Oct 2]; Available from: http://www.euro.who.int/__data/assets/pdf_file/0004/97393/2.6.pdf?ua=1.Google Scholar
- 16.Inkinen J, Jayaprakash B, Santo Domingo JW, Keinänen-Toivola MM, Ryu H, Pitkänen T. Diversity of ribosomal 16S DNA- and RNA-based bacterial community in an office building drinking water system. J Appl Microbiol. 2016;120:1723–38. Available from: http://doi.wiley.com/10.1111/jam.13144.CrossRefPubMedGoogle Scholar
- 20.Rogers J, Dowsett AB, Dennis PJ, Lee JV, Keevil CW. Influence of temperature and plumbing material selection on biofilm formation and growth of Legionella pneumophila in a model potable water system containing complex microbial flora. Appl Environ Microbiol. 1994;60:1585–92. Available from: http://www.ncbi.nlm.nih.gov/pubmed/8017938.PubMedPubMedCentralGoogle Scholar
- 21.van der Kooij D, Veenendaal HR, Scheffer WJH. Biofilm formation and multiplication of Legionella in a model warm water system with pipes of copper, stainless steel and cross-linked polyethylene. Water Res. 2005;39:2789–98. Available from: http://www.sciencedirect.com/science/article/pii/S004313540500268X.CrossRefPubMedGoogle Scholar
- 23.Skjevrak I, Due A, Gjerstad KO, Herikstad H. Volatile organic components migrating from plastic pipes (HDPE, PEX and PVC) into drinking water. Water Res. 2003;37:1912–20. Available from: http://www.sciencedirect.com/science/article/pii/S0043135402005766.CrossRefPubMedGoogle Scholar
- 24.Shih H-Y, Lin YE. Efficacy of copper-silver ionization in controlling biofilm- and plankton-associated waterborne pathogens. Appl Environ Microbiol. 2010;76:2032–5. American Society for Microbiology (ASM). Available from: http://www.ncbi.nlm.nih.gov/pubmed/20080997. [cited 2016 Oct 2].CrossRefPubMedPubMedCentralGoogle Scholar
- 25.Lin YE, Stout JE, Yu VL. Controlling Legionella in hospital drinking water: an evidence-based review of disinfection methods. Infect Control Hosp Epidemiol. 2011;32:166–73. Cambridge University Press. Available from: http://www.journals.cambridge.org/abstract_S0195941700039898. [cited 2016 Oct 2].CrossRefPubMedGoogle Scholar
- 27.Leoni E, De Luca G, Legnani PP, Sacchetti R, Stampi S, Zanetti F. Legionella waterline colonization: detection of Legionella species in domestic, hotel and hospital hot water systems. J Appl Microbiol. 2005;98:373–9. Blackwell Science Ltd. Available from: http://doi.wiley.com/10.1111/j.1365-2672.2004.02458.x. [cited 2016 Oct 2].CrossRefPubMedGoogle Scholar
- 31.Hammes F, Berger C, Köster O, Egli T. Assessing biological stability of drinking water without disinfectant residuals in a full-scale water supply system. J Water Supply Res Technol - Aqua. 2010;2010:59.Google Scholar
- 32.Volk CJ, LeChevallier MW. Assessing biodegradable organic matter (PDF). J Am Water Works Assoc AWWA. 2000;92:64–76.Google Scholar
- 33.Zhang Y, Edwards M, Pinto A, Love N, Camper A, Rahman M, et al. Effect of nitrification on corrosion in the distribution system. Denver: Water Research Foundation; 2010.Google Scholar
- 34.Proctor CR, Gächter M, Kötzsch S, Rölli F, Sigrist R, Walser J-C, et al. Biofilms in shower hoses—choice of pipe material influences bacterial growth and communities. Environ. Sci. Water Res. Technol. 2016;2:670–82. The Royal Society of Chemistry. Available from: http://xlink.rsc.org/?DOI=C6EW00016A. [cited 2017 Apr 11].CrossRefGoogle Scholar
- 35.Williams K, Pruden A, Falkinham JO, Edwards M, Williams K, Pruden A, et al. Relationship between organic carbon and opportunistic pathogens in simulated glass water heaters. Pathog (Basel, Switzerland). 2015;4:355–72. Multidisciplinary Digital Publishing Institute (MDPI). Available from: http://www.ncbi.nlm.nih.gov/pubmed/26066310. [cited 2016 Dec 5].Google Scholar
- 38.Kuiper MW, Valster RM, Wullings BA, Boonstra H, Smidt H, van der Kooij D. Quantitative detection of the free-living amoeba Hartmannella vermiformis in surface water by using real-time PCR. Appl Environ Microbiol. 2006;72:5750–6. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/16957190 [cited 2016 Oct 2].CrossRefPubMedPubMedCentralGoogle Scholar
- 40.Suzuki MT, Taylor LT, DeLong EF. Quantitative analysis of small-subunit rRNA genes in mixed microbial populations via 5′-nuclease assays. Appl Environ Microbiol. 2000;66:4605–14. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/11055900. [cited 2016 Oct 2].CrossRefPubMedPubMedCentralGoogle Scholar
- 42.Leoni E, Legnani PP. Comparison of selective procedures for isolation and enumeration of Legionella species from hot water systems. J Appl Microbiol. 2001;90:27–33. Blackwell Science Ltd. Available from: http://doi.wiley.com/10.1046/j.1365-2672.2001.01178.x. [cited 2016 Oct 2].CrossRefPubMedGoogle Scholar
- 43.Caporaso JG, Lauber CL, Walters WA, Berg-Lyons D, Huntley J, Fierer N, et al. Ultra-high-throughput microbial community analysis on the Illumina HiSeq and MiSeq platforms. ISME J. 2012;6:1621–4. Nature Publishing Group. Available from: http://www.nature.com/doifinder/10.1038/ismej.2012.8. [cited 2016 Oct 2].CrossRefPubMedPubMedCentralGoogle Scholar
- 44.Props R, Kerckhof F-M, Rubbens P, De Vrieze J, Hernandez Sanabria E, Waegeman W, et al. Absolute quantification of microbial taxon abundances. ISME J. 2016; Nature Publishing Group. Available from: http://www.nature.com/doifinder/10.1038/ismej.2016.117. [cited 2016 Dec 18].
- 48.Proctor CR, Edwards MA, Pruden A. Microbial composition of purified waters and implications for regrowth control in municipal water systems. Environ. Sci. Water Res. Technol. 2015;1:882–92. The Royal Society of Chemistry. Available from: http://pubs.rsc.org/en/content/articlehtml/2015/ew/c5ew00134j. [cited 2016 Jan 2].CrossRefGoogle Scholar
- 49.Prosser JI, Head IM, Stein LY. The family Nitrosomonadaceae, The Prokaryotes. Berlin: Springer Berlin Heidelberg; 2014. p. 901–18. Available from: http://link.springer.com/10.1007/978-3-642-30197-1_372. [cited 2016 Oct 16].CrossRefGoogle Scholar
- 52.Wrighton KC, Agbo P, Warnecke F, Weber KA, Brodie EL, DeSantis TZ, et al. A novel ecological role of the Firmicutes identified in thermophilic microbial fuel cells. ISME J. 2008;2:1146–56. Nature Publishing Group. Available from: http://www.nature.com/doifinder/10.1038/ismej.2008.48. [cited 2016 Oct 19].CrossRefPubMedGoogle Scholar
- 53.Sohn JH, Kwon KK, Kang J-H, Jung H-B, Kim S-J. Novosphingobium pentaromativorans sp. nov., a high-molecular-mass polycyclic aromatic hydrocarbon-degrading bacterium isolated from estuarine sediment. Int J Syst Evol Microbiol. 2004;54:1483–7. Microbiology Society. Available from: http://ijs.microbiologyresearch.org/content/journal/ijsem/10.1099/ijs.0.02945-0. [cited 2016 Oct 16].CrossRefPubMedGoogle Scholar
- 54.Leroi AM, Bennett AF, Lenski RE. Temperature acclimation and competitive fitness: an experimental test of the beneficial acclimation assumption. Proc Natl Acad Sci U S A. 1994;91:1917–21. National Academy of Sciences. Available from: http://www.ncbi.nlm.nih.gov/pubmed/8127906. [cited 2017 Aug 4].CrossRefPubMedPubMedCentralGoogle Scholar
- 55.Gião MS, Wilks SA, Keevil CW. Influence of copper surfaces on biofilm formation by Legionella pneumophila in potable water. Biometals. 2015;28:329–39. Springer Netherlands. Available from: http://link.springer.com/10.1007/s10534-015-9835-y. [cited 2016 Oct 15].CrossRefPubMedGoogle Scholar
- 57.Scheikl U, Sommer R, Kirschner A, Rameder A, Schrammel B, Zweimüller I, et al. Free-living amoebae (FLA) co-occurring with Legionellae in industrial waters. Eur J Protistol. 2014;50:422–9. Elsevier. Available from: http://www.ncbi.nlm.nih.gov/pubmed/25062389. [cited 2016 Oct 16].CrossRefPubMedPubMedCentralGoogle Scholar
- 58.Marciano-Cabral F, Jamerson M, Kaneshiro ES. Free-living amoebae, Legionella and Mycobacterium in tap water supplied by a municipal drinking water utility in the USA. J Water Health. 2010;8:71–82. Available from: http://www.ncbi.nlm.nih.gov/pubmed/20009249. [cited 2016 Oct 16].CrossRefPubMedGoogle Scholar
- 60.Campbell BJ. The family Acidobacteriaceae, The Prokaryotes. Berlin: Springer Berlin Heidelberg; 2014. p. 405–15. Available from: http://link.springer.com/10.1007/978-3-642-38954-2_160. [cited 2016 Oct 16].Google Scholar
- 61.Oren A, Xu X-W. The family Hyphomicrobiaceae, The Prokaryotes. Berlin: Springer Berlin Heidelberg; 2014. p. 247–81. Available from: http://link.springer.com/10.1007/978-3-642-30197-1_257. [cited 2016 Oct 16].CrossRefGoogle Scholar
- 62.Teitzel GM, Geddie A, De Long SK, Kirisits MJ, Whiteley M, Parsek MR. Survival and growth in the presence of elevated copper: transcriptional profiling of copper-stressed Pseudomonas aeruginosa. J Bacteriol. 2006;188:7242–56. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/17015663. [cited 2016 Oct 16].CrossRefPubMedPubMedCentralGoogle Scholar
- 63.Buse HY, Lu J, Struewing IT, Ashbolt NJ. Preferential colonization and release of Legionella pneumophila from mature drinking water biofilms grown on copper versus unplasticized polyvinylchloride coupons. Int J Hyg Environ Health. 2014;217:219–25. Available from: http://www.sciencedirect.com/science/article/pii/S143846391300059X. [cited 2015 Jan 22].CrossRefPubMedGoogle Scholar
- 65.Lin Y-S, Vidic RD, Stout JE, Yu VL. Negative effect of high pH on biocidal efficacy of copper and silver ions in controlling Legionella pneumophila. Appl Environ Microbiol. 2002;68:2711–5. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/12039724. [cited 2016 Oct 15].
- 67.Wen G, Kötzsch S, Vital M, Egli T, Ma J. BioMig—a method to evaluate the potential release of compounds from and the formation of biofilms on polymeric materials in contact with drinking water. Environ Sci Technol. 2015;49:11659–69. American Chemical Society. Available from: http://pubs.acs.org/doi/10.1021/acs.est.5b02539. [cited 2015 Dec 2].CrossRefPubMedGoogle Scholar
- 68.van der Wielen PWJJ, van der Kooij D. Nontuberculous mycobacteria, fungi, and opportunistic pathogens in unchlorinated drinking water in The Netherlands. Appl Environ Microbiol. 2013;79:825–34. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/23160134. [cited 2016 Oct 16].CrossRefPubMedPubMedCentralGoogle Scholar
- 69.Meier T, Bendinger B. Survival of pathogens in drinking water plumbing systems: impact factors and sanitation options. Water Sci Technol Water Supply. 2016;2016:ws2016040. IWA Publishing. Available from: http://ws.iwaponline.com/cgi/doi/10.2166/ws.2016.040. [cited 2016 Jul 4].Google Scholar
- 70.Temmerman R, Vervaeren H, Noseda B, Boon N, Verstraete W. Necrotrophic growth of Legionella pneumophila. Appl Environ Microbiol. 2006;72:4323–8. American Society for Microbiology. Available from: http://www.ncbi.nlm.nih.gov/pubmed/16751547. [cited 2016 Oct 16].CrossRefPubMedPubMedCentralGoogle Scholar
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made. The Creative Commons Public Domain Dedication waiver (http://creativecommons.org/publicdomain/zero/1.0/) applies to the data made available in this article, unless otherwise stated.