Programmable protective device for LV distribution system protection
High quality electric power supply is the prime goal in the modern power systems around the world. One of the main ways to achieve this is the protection of the system which needs to be fast, reliable and cost effective. The objective of this paper is to provide protection of equipments in low voltage (LV) distribution system and thereafter to avoid their failure due to abnormal operating conditions. The proposed device provides protection for industrial, commercial and residential equipments by monitoring under voltage, over voltage and over current conditions using microcontroller, transistor and other discrete components. The microcontroller is the heart of this protective device which performs the major control of the device. The designed circuit can withstand the loads and the set voltage range so as to supply the connected load for any voltage variation between 220 and 240 Volts. It can be used to protect loads such as refrigerator, TV, VCR/DVD player etc. against undesirable over and under voltage conditions as well as surges caused due to sudden failure of power supply mains. This device can also be used directly as standalone equipment between the supply mains and the load. The over/under voltage and over current cut-off with time delay provides over/under-voltage and over current protection and also protection against any transients.
KeywordsDistribution system Protective device Microcontroller Over -under voltage Over current
The purpose of the electrical power distribution system is to supply good quality, safe and reliable power to the consumers, load centres, industrial plants, etc. Now-a-days high quality power is basic need of highly automated industries and home appliances (, https://en.wikipedia.org/wiki/Automation). The quality and security of power system are disturbed due to faults and failures occurring. Protection against sudden over voltages in substations is a vital part of the overall reliability of power systems [2, 3]. The protection against over voltage is mainly necessary for human being because the people will lose their life due to overvoltage shock. The degree of surge protection provided to a station is governed by the reliability requirement and the economics to obtain such reliability. Since major stations generally include strategic and highly valuable power equipment, surge protection is essential to avoid or minimize major system disturbances as well as major equipment failures. Transient over voltages occurring in the power systems can cause operational breakdown and also cause failure in industrial and household equipments as well.
Voltage irregularities are one of the greatest power quality issue faced by industry and domestic appliances is responsible for damaging valuable electrical equipments. Electrical Power System protection is required for protection of both user and the system equipment from faults; hence electrical appliances are not allowed to operate without any protective device installed. Power System fault is defined as undesirable condition that occurs in the power system like short circuit, current leakage, ground short, over current, under and over voltage, etc.
The ability of protection system is demanded not only for economic reason but for expert and reliable service. Technically speaking, an over/under voltage and over current condition is reached when the voltage exceeds or lags the nominal voltage and current exceeds the normal rated current, respectively. Under voltage might result into burn out, distortion or permanent damage while over voltage in the form of spikes and surges could cause distortion, burn-out, meltdown and fire, electro-pulsing and permanent damage. Owing to the incessant damages done by fluctuations in the power supply, there is urgent need to address the problem through other alternatives, which give birth to design and construction of an equipment to protect the connected loads against under and/over voltage and over current conditions. Under/over voltage and over current protection is essential between supply terminal and the appliances (connected loads).
Actually sudden fluctuation in the voltage is very high and causes serious problems in industries and home appliances and it also causes power loss in the electrical circuits. These losses cause low power factor in the supply and due to this much amount of power is going to be wasted. Further, these fluctuations may significantly impact the power quality as well as the reliability of other voltage controlling devices and various costly and precious equipments may get damaged.
When the RMS voltage or current drops between 0.1 and 0.9 pu at power frequency for duration of 0.5 cycles to 1 min, then it is said to be sag condition. The swell condition will occur when RMS voltage or current rises between 1.1 and 1.8 pu at power frequency for the duration of 0.5 to 1 min, and above 1.8 pu and below 0.9 pu is called over voltage and under voltage conditions, respectively . Voltage sags and under voltage conditions are caused by abrupt increase in loads due to short circuit and faults or it is caused by abrupt increase in source impendence caused by loose connection. Voltage swell and over voltage conditions are always caused by an abrupt decrease in load on a circuit with a poor or damaged voltage regulator, although they can also be caused by a damaged or loose neutral connection.
Majority of the papers available in literature on LV distribution system protection considers only over or under voltage or over current protection or over and under voltage protection. But the method proposed in this paper considers all in together. The aim of this work is to develop a protective system that monitors the abnormal conditions that taking place in LV distribution systems and provide breakpoint based on low/ high voltage and over current tripping mechanism; that avoids any damage to the load, various industrial and domestic appliances consisting of fluctuation in the AC mains. The proposed protection device is capable to protect domestic equipments like: refrigerator, induction motor (IM) and other electrical appliances from abnormal conditions.
The methodology proposed in this work consists of development of block diagram of the protective device, background to the most commonly arising problems in the power system network and a brief discussion about the micro controller used in this work.
2.1 Functional block diagram of proposed protection scheme
2.2 Over voltage
2.3 Under voltage
Under voltage is defined as a sudden drop in the root mean square (r.m.s.) voltage and is usually characterized by the remaining (retained) voltage . Under voltage is thus, short duration reduction in r.m.s. voltage, caused mainly by short circuit, starting of large motors and equipment failure. Under voltages are the most common power disturbance whose effect is quite severe especially in industrial and large commercial customers such as the damage of the sensitivity equipments and loss of daily productions and finances. The examples of the sensitive equipments are Programmable Logic Controller (PLC), Adjustable Speed Drive (ASD) and Chiller control. Under voltage at the equipment terminal can be due to a short circuit fault hundreds of kilometers away in the transmission system.
2.4 Over current
In an electric power system, over current or excess current is a situation where the value larger than intended electric current exists through a conductor, leading to excessive generation of heat which leads to the risk of fire or damage to equipment [5, 6, 7]. Possible causes for over current include short circuit, excessive load, incorrect design, or a ground fault. Fuses, circuit breakers, temperature sensors and current limiters are commonly used protection mechanisms to control the risks of over current. Over current protection also includes the protection against over loads and this is most widely used protection. Over loading of a machine (or equipment) means the machine is taking more current than its rated current. Hence, with overloading there is an associated temperature rise. The permissible temperature rise has a limit based on insulation class and material. Over current protection against overload is generally provided by thermal relays. Over current protection also includes protection against short-circuit. Short circuits may leads to phase faults, earth faults or winding faults. Short circuit currents are generally several times more than full load current. Hence fast fault clearance is always desirable at the time of short-circuits.
An 8 or 16 bit microprocessor as central processing unit (CPU).
A small amount of RAM.
Programmable ROM and/or flash memory.
Parallel and/or serial I/O.
Timers and signal generators.
Analog to Digital (A/D) and/or Digital to Analog (D/A) conversion.
Often used to run dedicated code that controls one or more tasks in the operation of a device or a system.
Also known as embedded controller because the microcontroller and supporting circuits are often built into, or embedded in, the devices they control.
Devices that utilize microcontrollers include car engines, consumer electronics (VCRs, microwaves, cameras, pagers, cell phones), computer peripherals (keyboards, printers, and modems), test/measurement equipment (signal generators, multimeters, and oscilloscopes).
Microcontrollers usually must have low-power requirements (~ 0.05–1 W compared to ~ 10–50 W of general purpose desktop CPUs) since many devices they control are battery operated.
The microcontroller performs the major functions of decision and control. The input supply voltage is fed to the microcontroller via current measuring unit and voltage measuring unit. The microcontroller was used in this circuit in order to reduce the complexity of the design and to ensure an easy interface with a liquid crystal display (LCD).
3 Development of the proposed methodology
This section deals with description of flow chart, working of the proposed protective device and result discussion.
3.1 Description of flow chart
Mode 1: The mode 1 operation is the default operation.
Mode 2: This mode is used for selections of over voltage. In this mode the desired value of over voltage is selected.
Mode 3: This mode is used for selections of low voltage. In this mode the desired value of low voltage is selected.
Mode 4: This mode is used for selections of over current. In this mode the desired value of over current is selected.
3.2 Main voltage monitoring
The signal from the peripheral initialization is fed to this module. The required operating voltage for monitoring is 120 V. If the voltage is less than 120 V the power will flows to the power off module and then to supply monitor and after monitoring, the signal flows to the start. If the voltage is above 120 V, the supply will be fed to the current and voltage calculation module followed by the main voltage monitoring. In the current and voltage calculation module the under voltage, over voltage and over current parameters are adjusted according to the applications required and the signal is fed to voltage and current set parameter module. In this module the reference voltage is adjusted according to the requirement. When the voltage and current exceeds or lesser than the refe rence value, it gives signal to the relay driver circuit in which the relay in normally closed condition becomes normally open condition. Otherwise, if the voltage or current value is equal to reference value the relay will be in normally closed condition. For every 10 s the signals from relay driver circuit is fed to the current or voltage calculation module for continuous operation.
The proposed protection scheme which provides protection to the circuit against the common problem of power system analysis like: under voltage, over voltage and over current is as shown in Fig. 1. Single phase supply is considered and protection is provided against the abnormalities those taking place in single phase system.
Normal working voltage for the single phase AC system is 220 V and + or - 10% tolerance is considered. This supply is converted into DC with the help of AC- DC converter followed by the RLC filter. The filter circuit removes the ripples which present in the DC. The output of the filter is DC and this is given as input to the regulator, where the voltage can be varied up to 440 V. The regulator provides constant supply required for the microcontroller and relay system even though there is any changes that has happens in the input side of regulator. The normal supply obtained at the output side of regulator is 12 V. When over current fault occurs the current transformer connected to the supply side converts that high value of current into low value and supply it to the microcontroller through analog to digital converter (ADC). In case when over voltage condition occurs the high values of voltage is reduced to low value of voltage and send that signal to ADC. The ADC converts analog signal into digital signal which is understood by the microcontroller.
The reference value of voltage and current are fed by software ( https://www.nxp.com/docs/en/data-sheet/8XC51_8XC52.pdf, http://www.datasheetcatalog.org/datasheet/maxim/MAX232.pdf, http://www.enwikipedia.org/wiki/GSM., www.aimglobal.org/technologies/rfid/what_is_rfid.asp, http://www.alldatasheet.com, http://www.nkelectronics.com, http://www.microelectronics.com) to the microcontroller. The reference voltage that was set in the micro controller is compared with the signal from current and voltage transformers. If it is greater or lesser than the reference voltage or current it gives signal to the relay driver circuit to trip the relay. The LCD is used to display the values of current and voltage. The keypads are used to set the reference voltage and current as per standard. So, the problems occurred due to sag, swell, over / under voltage and over current conditions can be detected and protected by the device.
In this work implementation of a protective circuit is done which helps to detect the voltage below 198 V (which is 0.9 times the rated voltage of 220 V) and it is a sag and under voltage condition) and above 242 V it is over voltage and swell condition. During under voltage condition, the proposed circuit will remain in open condition so there will not be any passage of current. In this condition lower relay of the circuit will remain open. When the voltage rises above 242 V (which is 1.1 times the rated voltage of 220 V and it is a swell and over voltage condition). Under this situation the circuit will remain open because during that time the upper relay in the circuit will remain open. Thus we can protect the costly equipment’s by disconnecting the supply to the circuit during abnormal conditions.
The protection circuit proposed in this paper can be used to protect the costly electrical appliances from abnormal conditions like sag, swell, under voltage, over voltage, over current and able to avoid appliances being get damaged from harmful effects. The advantages of this protective device are: highly sensitive, fit and forget system, low cost and reliable circuit, complete elimination of manpower, can handle heavy loads up to 7A, auto switch OFF during abnormal conditions and auto switch ON at the time of normal conditions. The applications of this protection device are in industrial machinery, house hold appliances like: TV, refrigerator, air conditioner, agriculture motors, and water pumps. This device can also be used directly as standalone equipment between the supply mains and the load. The over/under voltage and over current cut-off with time delay provides over/under-voltage and over current protection and also protection against any transients. If tap changing transformer is used and is automatically controlled, then the device can operate the load normally during under voltage and over voltage condition. Hence, we can protect as well as operate the load in abnormal conditions also. The proposed system can be further improved by integrating it with GSM modem that alerts user by sending an SMS about the tripping status.
The authors would like to express the deepest thanks to the principal, PESCE, Mandya, and the Management, PET ®, Mandya, for their timely support and constant encouragement in successful completion of this research work.
TEQIP fund PESCE. Mandya.
Availability of data and materials
Data sharing not applicable to this article.
About the authors
S. Gopiya Naik(1968-), male, PHD and Associate Professor, Major in the planning of distribution system, renewable energy sources.
GNS identified the problem and monitored the whole research work, VR formulated the methodology and RA together with VR implemented, designed and tested the proposed scheme and ensured the results successively. All authors read and approved the final manuscript.
The authors declare that they have no competing interests.
- 1.Lucas, J.R. (2005). Power system analysis; faults, EE423.Google Scholar
- 2.Butto, G. M., Jensen, B. B., et al. (2013). Protection of low voltage CIGRE distribution network. Smart grid and renewable energy (Vol. 4, pp. 489–500).Google Scholar
- 3.Manish, P., Antara, C., & Snigdha, S. (2015). Hardware implementation of over voltage and under voltage protection. International journal of innovative research in electrical, electronics. Instrum Control Eng, 3(6), 140–144.Google Scholar
- 4.IEEE Recommended practice for monitoring electric power quality. (1995). IEEE Std. In 1159–1995.Google Scholar
- 5.Vithalani, C.H. (2017). Over-under voltage protection of electrical appliances. Electronics for You.Com, March 1.Google Scholar
- 6.Eur Ing, G.S., Eur Ing, J.B. (2009). A practical guide to wiring regulations. (Ch.7), 4th edition, Wiley online library.Google Scholar
- 7.From Wikipedia, the free encyclopedia.Google Scholar
- 8.Lee, C. V. (1995). Mobile cellular telecommunications analog and digital systems (2nd ed.). Lisbon: Mc-Graw Hill.Google Scholar
- 9.Gibson, J. D. (1999). The mobile communication handbook (2nd ed.). USA: CRC Press Ltd..Google Scholar
- 10.Spacor, P. (1993). Microcontroller technology. USA: Prentice Hall.Google Scholar
- 11.Michael, B. Embedded C coding standard.Google Scholar
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.