A high-temperature gas-and-steam turbine plant operating on combined fuel
- 75 Downloads
A high-temperature gas–steam turbine plant (GSTP) for ultrasupercritical steam conditions is proposed based on an analysis of prospects for the development of power engineering around the world and in Russia up to 2040. The performance indicators of a GSTP using steam from a coal-fired boiler with a temperature of 560–620°C with its superheating to 1000–1500°C by firing natural gas with oxygen in a mixingtype steam superheater are analyzed. The thermal process circuit and design of a GSTP for a capacity of 25 MW with the high- and intermediate-pressure high-temperature parts with the total efficiency equal to 51.7% and the natural gas utilization efficiency equal to 64–68% are developed. The principles of designing and the design arrangement of a 300 MW GSTP are developed. The effect of economic parameters (the level and ratio of prices for solid fuel and gas, and capital investments) on the net cost of electric energy is determined. The net cost of electric energy produced by the GSTP is lower than that produced by modern combined-cycle power plants in a wide variation range of these parameters. The components of a high-temperature GSTP the development of which determines the main features of such installations are pointed out: a chamber for combusting natural gas and oxygen in a mixture with steam, a vacuum device for condensing steam with a high content of nondensables, and a control system. The possibility of using domestically available gas turbine technologies for developing the GSTP’s intermediate-pressure high-temperature part is pointed out. In regard of its environmental characteristics, the GSTP is more advantageous as compared with modern condensing power plants: it allows a flow of concentrated carbon dioxide to be obtained at its outlet, which can be reclaimed; in addition, this plant requires half as much consumption of fresh water.
Keywordsturbine coal mixture superheating regeneration reclaiming net cost
Unable to display preview. Download preview PDF.
- 4.V. V. Bushuev and A. A. Troitskii, “Results from monitoring the energy strategy of Russia: problems of its implementation and the energy efficiency of the economy,” Therm. Eng. 52 (2), 85 (2005).Google Scholar
- 5.V. V. Bushuev and A. A. Troitskii, “Monitoring of the implementation of the 'Energy Strategy of Russia to the Year 2020' in 2004,” Therm. Eng. 52 (12), 903 (2005).Google Scholar
- 10.A. A. Makarov, A Forecast for Development of Energy in Russia and Worldwide to 2040 (INEI RAN, Moscow, 2014) [in Russian].Google Scholar
- 11.“A gas–steam power installation with firing fuel in oxygen,” Therm. Eng. 57 (2), 175 (2010).Google Scholar
- 13.G. G. Ol’khovskii, “Technologies for thermal power plants,” Gazoturb. Tekhnol., No. 10, 4–7 (1999).Google Scholar
- 14.Thermal and Nuclear Power Plants: A Handbook, Volume 3, Ed. by A. V. Klimenko and V. M. Zorina (MEI, Moscow, 2003) [in Russian].Google Scholar
- 15.S. K’yaer, “Experience gained from design and operation of power units for supercritical parameters,” Persp. Energetiki 6, 241–251 (2002).Google Scholar