Abstract
Microgrids are supposed to provide stable power for seamless utilitygrid interaction under all conditions as stated by IEEE1547 standard. But, the use of power electronic inverter makes the microgrid sensitive to transients than synchronous generatorbased plants. This degrades the voltage/frequency responses during transients, which can lead to transient stability problem if not controlled properly. Hence, the design of effective closedloop voltage and current (V/I) controllers is highly desired to control the inverter output against the disturbances. The V/I controllers are based on PI (proportionalcumintegral) formulas. Thus, the effectiveness of V/I controllers relies on how accurate that their gain parameters are tuned. Many PItuning methods have been developed in the literature, but, it is yet difficult to identify a suitable method for an application. Also, only a few researchers have focused on the microgrids due to the complexity involved in its controller design by the presence of V/I cascaded dualloop. Hence, to address this problem, this paper proposes a novel way of designing V/I controller parameters by using polezero cancellation method. This method is implemented by deriving the microgrid’s smallsignal model. This improves the transient response through reduced system order and/or alleviated sluggish/marginalstable/unstable poles by adding zeros at same places where those poles are laid, to in effect cancel them. The efficacy of the proposed method over existing methods is assessed by plotting frequency and voltage responses under different test conditions. From the simulation results, it is witnessed that the proposed method relatively improved the transient characteristics of microgrids.
Article Highlights

Analyzes the applicability of conventional PI tuning methods for microgrid controllers’ design.

Proposes a novel small signal model based polezero cancellation method for the design of microgrid controllers.

Enhances the gain margin, which improves the stabilization capacity of the system when subjected to disturbances.

Improves the transient behavior of frequency and voltage responses, which ensure the safety of sensitive loads.
Introduction
The modern power system is facing profound changes by the integration of more and more renewable energy sourced microgrid (RESM) plants to the utilitygrid to get rid of issues with conventional fossil fuelbased energy. However, the fruitful operation of RESMs is majorly affected by the intermittent renewable energy availability and dependency on harmonic prone power electronic voltage source inverter (PEVSI). Further, as a generalpurpose utility grade plant, the RESM needs to be operated under typical industrial/residential load conditions that have a wider degree of variability. These variabilities mainly include imbalances in the loadbus voltage or utilitygrid voltage due to singlephase distribution systems, nonlinear load actions, momentary faults, disturbances, etc. Compared to synchronous generatorbased power plants, PEVSIbased RESMs possess negligible inertia and kinetic energy. So, RESMs are considered sensitive, which produce degraded voltage and frequency response during the variabilities mentioned above [1,2,3]. These degraded responses can further lead to transient stability problem if not controlled appropriately. To address the abovementioned issues, the stateoftheart solutions suggest, optimal use of storage devices to handle the irregularity in renewable energy availability [4,5,6], refined multilevel or modular PEVSI configurations with reduced complications (e.g., fault tolerant operations during switch failures, use of less number of circuit components, etc.) to handle harmonic distortion issues [7,8,9], and the development of different voltage and current (V/I) control methods [10,11,12] and droop control methods [13,14,15] to handle power quality and power sharing issues, respectively. All these solutions help to improve the RESM’s steadystate stability, but, the concerns of oscillatory responses during smallsignal disturbances are yet predominant. These transient response issues rely on the timely response and fidelity of the PEVSI’s controller, i.e., the V/I controllers.
In each closedloop control cycle, the V/I controllers produce the control (or reference/modulation) signal to the PWM generator as given in Fig. 1 by controlling the load variations and disturbances occurred at the loadbus. Based on this control signal, the PWM generator produces the necessary firing pulses to regulate the PEVSI output. The V/I controllers are the proportionalintegral controller (PIC)based algorithms. Therefore, the desired operation of V/I controllers to address the transient response issues depend on the accurate design of its PIC gain parameters.
To design gain parameters of PICs used in different applications, there are several tuning methods have been continuously evolving as discussed in [16,17,18,19,20,21,22,23,24]. Apart from these conventional methods, polezero cancellation (PZC) method is being used to design PICs in different applications such as, design of pulse pileup tracking system used in amplifiers to generate lower noises [25], design of harmonic controller for a STATCOM [26], in multistage amplifiers to decrease the size of compensation capacitor, output power transistor, and to increase the powerbandwidth efficiency [27], for reducing the forced vibration in an end milling process application [28], for high speed sample and hold circuit design used in pipeline analog–digital converters [29], design of CdTe diodebased radiation detectors [30], design of gain scheduling control method for DC/DC converter [31], design of low noise power amplifier used in UWB systems [32], for increasing the phase and gain margin in feedback systems [33], design of current controller for electric machines [34], design of 3phase synchronous reference frame PLLs [35], design of levitated object position controller for magnetic levitation systems [36], in CMOS transconductance operational amplifiers with the help of settling time computations [37], to expand the bandwidth of dualmass MEMS gyroscopes [38], in firstorder and timedelay systems for rate limiting of actuators [39], etc.
The concept of PZC method is to compensate the unstable poles (openloop righthalfplane poles) or sluggish/marginal stable poles (poles at or nearby origin) by adding zeros at the same locations where those undesired poles are laid, to in effect compensates the effect of those poles. Despite using the PZC method effectively in controller design for many applications, while, to the best of authors’ knowledge based on the abovereported literature, it has never been used to design the V/I controllers of RESMs. Hence, the applicability of PZC method for the design of dualloop V/I controllers for RESMs is worthy of serious consideration. With this objective, this paper proposes the “Small Signal Model Based PoleZero Cancellation (MPZC) method” to design the PIC parameters of V/I controllers used in RESMs. The contributions of this paper are outlined as follows.

Analyzing the applicability of conventional PIC tuning methods discussed in [16,17,18,19,20,21,22,23,24] for the design of RESM’s controller. A quantitative analysis is presented in Sect. 5.1. This analysis further helps to identify the best conventional method to compare with the proposed method to persuade the importance of the proposed method.

Design of the proposed MPZC methodology for the design of V/I controller gains to achieve the improved transient response in RESMs over the conventional methods.

Conducting adequate simulation analysis with different test conditions to judge the usefulness of the proposed method compared to the conventional methods.
The other sections of the paper are arranged as follows. Section 2 describes the V/I controller operation in RESMs. Section 3 describes the development of proposed small signal model of the RESM. Section 4 describes the development of conventional and proposed methods for designing the PIC parameters used in V/I controllers. Section 5 presents the comparative results, which also includes the analysis on the applicability of conventional tuning methods for the design of RESM’s V/I controller. To conclude, Sect. 6 provides the cumulative remarks and achievements of this paper.
Description of the V/I controller operation
The RESM schematic shown in Fig. 1 is an integrated entity of renewable sources with associated converters, storage units, PEVSI, V/I controllers, load, and utilitygrid connection. The V/I controller works in a closedloop between the AC (or load) bus and the PEVSI. This is formed with the cascaded connection of voltage and current controllers given in Fig. 2a and Fig. 2b [3]. The corresponding operational relations of V/I controller are given as (1)–(6), which produces the threephase reference signal to PWM generator as referred in (7), using the inverse park transformation formula. Based on this reference (or modulation) signal, the PWM generator produces the switching signals to control the PEVSI’s switches, which subsequently controls its output.
Further, from (5) and (6), it can be seen that the effectiveness of the reference PWM signal, thereby the V/I control system majorly depends upon the values of PIC gains (K_{PA}, K_{IA}, K_{PV}, K_{IV}). Hence, it is intoned that the operation of the V/I controller depends on the proper tuning of its PIC gains.
For the operation of V/I controller, the phaselocked loop (PLL) is used for the calculation of a phase angle for dq transformation and the frequency of input voltage waveform. The block diagram of PLL is given in Fig. 3. Here, abcdq transformation is used to get V_{qo}, V_{do}; the q and d components of \(V_{o}^{abc}\) (voltage measured at the load bus). The modeling specifications given in Table 1 are used to design the PLL.
Development of the proposed small signal model of the microgrid
The RESM schematic shown in Fig. 1 is represented as the simplified equivalent circuit shown Fig. 4 to develop its small signal model with respect to the assumptions given in Table 2. Here, UG and MG indicate the utilitygrid and microgrid terminals, respectively. The objective of this model is to implement the proposed MPZCbased design method for the V/I controller that controls the load voltage/outerloop voltage (\(V_{o}^{abc}\)), and PEVSI’s current/innerloop current (\(I_{i}^{abc}\)), whose singlephase parameters are represented as V_{o}(s) and I_{i}(s), respectively, and are related through (8)–(11). From (9) and (11), the uncontrolled microgrid plant model is obtained, as shown in Fig. 5, where the output and input are related as (12).
Transfer function of the inner current controller
The goal of the current controller is to regulate the current drawn from PEVSI (\(I_{i} (s)\)). So, to derive the transfer function of the current controlled inner loop, the influence of the voltage controlled outer loop is ignored. The current controller model is developed as given in Fig. 6, where, Fig. 6a gives the conceptual model to realize the current controller, Fig. 6b shows its total model, and Fig. 6c shows its simplified model. From Fig. 6c, the CLTF and thereby, the controlled current is obtained as given in (13) and (14), respectively.
Transfer function of the outer voltage controller
The goal of the voltage controller is to regulate the voltage across the load (\(V_{o} (s)\)). So, to derive the transfer function of the voltage controlled outer loop, the effect of the current controlled inner loop is ignored. The voltage controller model is developed as given in Fig. 7, where, Fig. 7a gives the conceptual model to realize the voltage controller, Fig. 7b shows its total model, and Fig. 7c shows its simplified model. From Fig. 7c, the CLTF and thereby, the controlled voltage is obtained as given in (15) and (16), respectively.
Transfer function of the overall microgrid system
The V/I controllers’ transfer function models are inserted into the uncontrolled plant model to develop the controlled plant model so that the controlled RESM plant model can be represented with a view of dualcontrol loops as denoted in Fig. 8. The output and input of this system are related through the transfer function given by (17). Equations (18) and (19) represent the OLTF and CLTF of the RESM plant, respectively. Hence, the small signal model of the microgrid plant is derived, as represented in Fig. 9, which is obtained based on (17)–(19). The integration of the three submodels, viz., uncontrolled plant model given in Fig. 5, the current controller model given by Fig. 6, and the voltage controller model given in Fig. 7 derive this overall model.
where;
Tuning of the V/I controller parameters
By the observation of small signal model shown in Fig. 9, the system control depends upon two parameters, viz., filter parameters (R_{f}, L_{f}, C_{f}, G_{f}) and PIC parameters of V/I controller (K_{PV}, K_{IV}, K_{PA}, K_{IA}). Hence, the proper design of these parameters improves the RESM’s response. With this intent, this section focuses on the tuning methods of controller parameters. The filter specifications are designed based on the relations expressed in (20) and (21) [40]. The computed values and the other considerations are given in Table 3.
where ∆V_{ac} and F_{r} are chosen as per the power quality requisites given by IEEE1547, IEEE519 standards.
Conventional methods for tuning V/I controller gain
Among many conventional tuning methods as discussed in Sect. 1, more suitable methods such as OLTR and EPI methods (which were widely used in the literature for similar applications and can exhibit tolerable transient stability responses) are chosen to validate the proposed method against them. These OLTR and EPI methods work on the plant’s openloop response with respect to design procedural steps given in Table 4 [17, 41, 42]. As the RESM’s controller involves V/I dualloops, the tuning steps given in Table 4 has to be repeated for those two loops. The limitations of these conventional OLTR and EPI methods are given as follows.

Due to the presence of interdependent dual control loops, as mentioned above, the use of these conventional methods for RESM application is quite questionable.

The measured parameters (T_{d}, τ_{c}, K_{s}, M) from the openloop response as described in Table 4 need to be more accurate for precise design of PIC gain parameters.

By considering the limitations described above, Sect. 5.1 gives a quantitative analysis to understand the applicability of these conventional methods to RESMs application.
Proposed method for tuning V/I controller gains
This section describes the development of the proposed MPZC method for the tuning of V/I controllers’ parameters as below.
Procedure for tuning current controller parameters
From the simplified current controller model realized in Fig. 6c, the OLTF for controlling the innerloop current or current drawn from the PEVSI (\(I_{i} (s)\)) is obtained as (22). From this, the openloop poles of the current controller model are obtained as (0) and (− R_{f}/L_{f}), where, one pole (s = 0) represents marginal stability, and another pole (s = − R_{f}/L_{f}) represents near marginal stability due to very lower (R_{f}) value for RESMs as explained in Table 2. Hence, these two poles lead to sluggish plant’s response and thereby, exhibits poor transient response during disturbances. The issue mentioned above can be alleviated by the proposed MPZC method. To achieve this, it is proposed to consider (23), so that the near marginal stable pole gets cancelled with the zero. The near marginal stable pole is a dominant pole, which is responsible for the system dynamics. The idea of compensating the effect of this dominant pole highly influences the dynamics of the closedloop system. The resultant OLTF is obtained as (24), where the secondorder system (22) is transformed to a firstorder system. This exhibits improved transient responses by damping out the natural oscillatory response of secondorder systems. Further, (25) denotes the CLTF of the current controller used to design its gain parameters.
where (τ_{1} = L_{f}/K_{PA}) represents the current controller’s time constant (or V/I controller’s innerloop time constant). Hence, from (23) and (25), current controller’s parameters (K_{PA}, K_{IA}) are computed by selecting proper filter parameters (R_{f}, L_{f}) as given in Table 3 and suitable lower time constant (τ_{1}). The resultant calculated values are given in Table 8.
Procedure for tuning voltage controller parameters
From the simplified voltage controller model realized in Fig. 7c, the OLTF for controlling the outerloop voltage or load voltage (\(V_{o} (s)\)) is obtained as (26). This includes G_{f} = 0 as given in Table 3, as it is already mentioned that the effect of G_{f} is negligible for RESMs application. Equation (26) represents a secondorder system transfer function with two poles at the origin. This leads to severe oscillatory responses due to having marginal stability characteristics, which may become unstable for specific conditions and stable for certain other conditions. The issue mentioned above can be alleviated by the proposed MPZC method. To realize this, it is proposed to consider (27), which cancels one pole at the origin. The resultant OLTF is derived as (28), where the secondorder system (26) is transformed to firstorder system. This exhibits improved transient response by damping out the severe oscillatory responses, as mentioned above. Further, (29) gives the CLTF of the voltage controller that is used to design its gain parameters.
Assume the Voltage controller’s Integral Gain
where (τ_{2} = C_{f}/K_{PV}) represents the voltage controller’s time constant (or V/I controller’s outerloop time constant). Hence, from (29), tuning of K_{PV} of the voltage controller is achieved by selecting suitable time constant (\(\tau_{2} \ge 5\tau_{1}\)) and filter parameter (C_{f}) given in Table 3. The resultant computed value is given in Table 8.
Rationale of the proposed MPZC method
The overall system’s CLTF given by (19) can be implemented with the parameter values obtained with respect to the conventional and proposed control methods discussed in Sects. 4.1 and 4.2. Hence, by substituting these parameter values given in Tables 3, 7, and 8, the system transfer function can be revised as given in (30) and (31) with respect to the conventional CC method and proposed MPZC method. From there, it can be understood that the use of the proposed MPZC method reduces the system size (order), which leads to the improvement of its transient response.
Comparative results and analysis
As per the objective of the paper, the results are segregated into two parts for the analysis, viz., (i) quantitative analysis on the applicability of conventional methods for RESMs, and (ii) comparative analysis of proposed and conventional methods subjected to various test conditions.
Analysis on the applicability of conventional tuning methods for microgrids
As discussed in Sect. 4.1, conventional methods, viz., OLTR (ZN1, WJC, CHR, CC) and EPI (ISE, ISTE, ISTSE, IATE) are tested for their applicability to RESM. The efficacy of these methods is assessed in two test modes, viz., one is when using for parameter tuning in the singleloop system, i.e., only the current controller (or innerloop) based RESM and another is when using for parameter tuning in dualloop system, i.e., for V/I controllerbased RESM. In both the test modes, timedomain and frequencydomain responses are plotted during the normal condition (no disturbance) as shown in Fig. 11 and Fig. 12 to understand the applicability of OLTR and EPI methods to RESMs. Various timedomain index (viz., delay time (T_{dt}), rise time (T_{rt}), settling time (T_{st}), peakovershoot (P_{ov})) and frequencydomain index (viz., phase margin (PM), gain margin (GM)) are computed to identify the superior method among these conventional methods. From these results, the following remarks could be noted.

For the singlecontrol loopbased system From Fig. 11, it is observed that all the conventional OLTR and EPI tuning methods worked satisfactorily as per the computed frequency/timedomain performance index.

For the dualcontrol loopbased system From Fig. 12a, c, it is observed that the OLTR methods worked satisfactorily. But, From Fig. 12b, d, it is clear that the EPI methods which worked well for singlecontrol loopbased system are failed for dualcontrol loop system and leads to instability.
The corresponding performance index is also undetermined from Fig. 12b, d. Hence, a polezero plot is drawn, as shown in Fig. 12e to observe the location of poles. Form this, it is seen that, EPI methods lead to the existence of openloop pole (or closedloop zero) located on the very far righthalf of splane, which represents an unstable system.
As it is advised by IEEE1547, IEEE519 standards to use both V/I control loops for robust RESM operation during transients, and based on the observations described above, it is concluded that the EPI methods are not suitable for RESMs application. Further, from Table 9, it is understood that the CC method shows better response in most of the index compared to other methods. Hence, the CC method is considered to assess the usefulness of the proposed MPZC method when subjected to different test conditions.
Comparative analysis of the proposed method and conventional method
To justify the efficacy of the proposed method, different test cases referred in Table 10 are applied, and the corresponding results of proposed MPZC method and conventional best (CC) method are compared. These test cases are considered in a way to resemble practical smoothly varying reactive load as well as largely varying nonlinear load (e.g., arc furnace, welding machines, etc.). The resultant simulation results are shown through Fig. 13, 14, 15 and 16 and the collective quantitative comparisons with respect to the standard tolerances are provided in Table 11.
Test caseT_{1} (of Table 10) is used to examine the stabilization capacity of the RESM system subjected to conventional and proposed methods. For analysis, timedomain and frequencydomain responses are plotted as given in Fig. 13. From Fig. 13a, it is seen that, even with more rise time, the proposed method leads to smooth response with faster settling time compared to the conventional method. Another major benefit is that it exhibits zero overshoot at startup, while it is dominant (18.5%) when using the conventional method. Similarly, from the frequencydomain response shown in Fig. 13b, it is witnessed that the phase margin is increased from 90° to 97.2° when using the proposed method. This increase in the stability margin boosts the RESM system’s stabilization capacity during transients.
Test casesT_{2} and T_{3} (of Table 10) are used to analyze the system response during disturbances. For the analysis, various voltage characteristic index [viz., waveshape, rate of change of voltage (dv/dt), overvoltage, undervoltage, total harmonic distortion (THD)] and frequency characteristic index [viz., underfrequency, overfrequency, rate of change of frequency (df/dt)] are obtained. In Test caseT_{2}, a disturbance of very low frequency (10 Hz) compared to nominal frequency (50 Hz) is injected as shown in Fig. 14a and in Test caseT_{3}, a nonlinear disturbance of ± 1 pu varying magnitude is injected as shown in Fig. 16a for the comparative study of conventional and proposed methods. From the frequency characteristics given in Figs. 14b and 16b, it is witnessed that the proposed method noticeably decreased the frequency deviation from its rated value compared to the conventional method. Also, from Fig. 14b, it is noticed that the use of conventional method causes a huge df/dt of 1.82 Hz/sec, which exceeds the standard limit of ± 1 Hz/sec as given in Table 11. This is a severe issue that can result in unwanted load shedding or loss of utilitygrid connection, concerns with phase balancing, realpower balancing, power hums/electromagnetic interferences for domestic appliances, etc. On the other side, the proposed method reduced the df/dt from 1.82 to 0.61 Hz/sec, which adheres the standard limit of ± 1 Hz/sec. This helps in improving the transient frequency response and can address the majority of the concerns mentioned above. Also, from Fig. 14c, it is noticed that the dv/dt is significantly reduced when using the proposed method.
As noted in Table 11, the dv/dt obtained with the conventional method violated the standard limit of ± 3 V/sec, which can damage the sensitive electric/electronic devices connected to the system. Similarly, in the 3phase voltage profile given in Fig. 15a, b, a reactive load disturbance resulted in 4.92% of overvoltage and 9.05% of undervoltage with the conventional method, which got noticeably reduced to 1.19% and 1.75%, respectively, with the proposed method. Control of over/under voltages is very vital as these can transform to high impact swell/sags. Also, from Fig. 16c, d, it is noticed that the conventional method leads to a huge variation in voltage profile for a nonlinear load variation, while, the proposed method improved the voltage profile and exhibits smooth response. The voltage deviations further lead to harmonic distortion, which is measured as THD [3]. From Figs. 15c and 16e, it is noticed that the proposed method exhibits low THD value of 0.77% and 1.21%, and the conventional method exhibits high THD of 3.30% and 5.37%, respectively, for the reactive and nonlinear load variations. Thus, the conventional method violated the standard limit of 5% as notified in Table 11. Having lower THD, the proposed method helps in preserving the voltage waveform shape during disturbances, which is a critical requisite for the integration of RESM and utilitygrid.
Conclusions
The fruitful operation of RESMs majorly depends upon the effectiveness of its V/I controllers. It should precisely control such that the system response should recover quickly within allowable tolerances to deliver nonsluggish and safe supply to the sustained load demands in realtime. From the literature, it is observed that even though, there are many controller design methods are available for different applications, their applicability to RESMs is limited as quantified in Sect. 5.1. So, to overcome the demerits of conventional methods and as a new way of controller parameters’ design for RESMs application, this paper proposes the MPZC method. The key merits of this method are outlined as follows.

The proposed method effectively improves the gain margin, which enhances the stabilization capacity of the system when subjected to disturbances.

The proposed method improves the transient behavior of both voltage and frequency characteristics, as reported in Table 11. This helps to ensure the safety of sensitive loads that are connected to the RESM plant in realtime.

Improvement of frequency and voltage transient response in the period of key disturbances helps in retaining the supply power quality requisites for the seamless interconnection of RESMs and utilitygrid as suggested by IEEE1547.
Hence, it is concluded that the proposed MPZC method is a better technique to effectively design the V/I controller parameters of RESM plants, which helps to improve the RESM performance in all critical conditions significantly.
Abbreviations
 CLTF:

Closedloop transfer function
 EPI:

Error Performance Index
 MG:

Microgrid
 MPZC:

Small signal model based polezero cancellation
 OLTR:

Openloop transient response
 OLTF:

Openloop transfer function
 PEVSI:

Power electronic voltage source inverter
 PIC:

Proportionalintegral controller
 PWM:

Pulse width modulation
 PZC:

Polezero cancellation
 RESM:

Renewable energy sourced microgrid
 THD:

Total harmonic distortion
 UG:

Utilitygrid
 V/I:

Voltage and current
 \(R_{f}^{abc} ,L_{f}^{abc}\) :

Series resistance (Ω), Series inductance (mH) of filter
 \(C_{f}^{abc} ,G_{f}^{abc}\) :

Shunt capacitance (µF), conductance (Ʊ) of filter
 \(R_{g}^{abc} ,L_{g}^{abc}\) :

Line resistance (Ω), Line inductance (mH) of grid
 \(V_{o}^{abc} ,I_{o}^{abc}\) :

Load bus measurements—voltage (V), current (A)
 \(V_{pwm}^{ref}\) :

Reference input (V) given to PWM generator
 \(V_{s}^{abc}\) :

Inverter output voltage (V)
 \(V_{i}^{abc}\) :

Series branch voltage (V) of the filter
 \(I_{i}^{abc}\) :

Current (A) drawn from the Inverter
 \(V_{g}^{abc}\) :

Utilitygrid voltage (V)
 \(I_{c}^{abc}\) :

Current (A) flowing in shunt branch of Filter
 \(V_{o}^{dq}\) :

\(V_{do} ,V_{qo}\) = dq Equivalents of \(V_{o}^{abc}\) (V)
 \(I_{o}^{dq}\) :

\(I_{qo} ,I_{do}\) = qd Equivalents of \(I_{o}^{abc}\) (A)
 \(V_{do}^{ref} ,V_{qo}^{ref}\) :

Reference inputs given to voltage controller (V)
 \(I_{di}^{ref} ,I_{qi}^{ref}\) :

Reference current inputs of current controller (A)
 e _{d}, e _{q} :

dq Components of \(V_{pwm}^{ref}\) (V)
 \(I_{i}^{dq}\) :

\(I_{qi} ,I_{di}\) = qd Components of \(I_{i}^{abc}\) (A)
 \(I_{i}^{ref}\) :

\(I_{di}^{ref} or I_{qi}^{ref}\) = Reference current for \(I_{i}\) control (A)
 \(V_{o}^{ref}\) :

\(V_{do}^{ref} or V_{qo}^{ref}\) = Reference voltage for \(V_{o}\) control (V)
 R _{f}, L _{f} :

Single phase representation of \(R_{f}^{abc} ,L_{f}^{abc}\)
 C _{f}, G _{f} :

Single phase representation of \(C_{f}^{abc} ,G_{f}^{abc}\)
 R _{g}, L _{g} :

Single phase equivalent of \(R_{g}^{abc} ,L_{g}^{abc}\)
 V _{s}, V _{i}, V _{o} :

Single phase equivalent of \(V_{s}^{abc}\), \(V_{i}^{abc}\), \(V_{o}^{abc}\)
 I _{i}, I _{c}, I _{o} :

Single phase equivalent of \(I_{i}^{abc}\),\(I_{c}^{abc}\),\(I_{o}^{abc}\)
 \(V_{dc}^{mg} ,V_{ac}^{mg}\) :

Microgrid’s DC, AC bus voltages respectively (V)
 ω :

Angular frequency (rad/sec)
 K _{PV}, K _{IV} :

PIC components of voltage controller
 K _{PA}, K _{IA} :

PIC components of current controller
References
Cady ST, Garcia ADD, Hadjicostis CN (2015) A distributed generation control architecture for islanded AC microgrids. IEEE Trans Control Syst Technol 23(5):1717–1735
Eid BM, Rahim NA, Selvaraj J, Khateb AHE (2016) Control methods and objectives for electronically coupled distributed energy resources in microgrids: a review. IEEE Syst J 10(2):446–458
Kumar YVP, Bhimasingu R (2017) Electrical machines based DC/AC energy conversion schemes for the improvement of power quality and resiliency in renewable energy microgrids. Int J Electr Power Energy Syst 90:10–26
Beltran H, Bilbao E, Belenguer E, Otadui IE, Rodriguez P (2013) Evaluation of storage energy requirements for constant production in PV power plants. IEEE Trans Ind Electron 60(3):1225–1234
Xinda K, Lu N, Jin C (2015) Control and size energy storage systems for managing energy imbalance of variable generation resources. IEEE Trans Sustain Energy 6(1):70–78
Kerdphol T, Fuji K, Mitani Y, Watanabe M, Qudaih Y (2016) Optimization of a battery energy storage system using particle swarm optimization for standalone microgrids. Int J Electr Power Energy Syst 81:32–39
Ebrahimi J, Babaei E, Gharehpetian GB (2012) A new multilevel converter topology with reduced number of power electronic components. IEEE Trans Ind Electron 59(2):655–667
Kangarlu MF, Babaei E (2013) A generalized cascaded multilevel inverter using series connection of sub multilevel inverters. IEEE Trans Power Electron 28(2):625–636
Kumar YVP, Ravikumar B (2016) A simple modular multilevel inverter topology for the power quality improvement in renewable energy based green building microgrids. Electric Power Syst Res J 140:147–161
Mehrasa M, Pouresmaeil E, Mehrjerdi H, Jorgensen BN, Catalao JPS (2015) Control technique for enhancing the stable operation of distributed generation units within a microgrid. Energy Convers Manag 97:362–373
Moradi MH, Eskandari M, Hosseinian SM (2016) Cooperative control strategy of energy storage systems and micro sources for stabilizing microgrids in different operation modes. Int J Electr Power Energy Syst 78:390–400
Tucci M, Riverso S, Vasquez JC, Guerrero JM, Trecate GF (2016) A decentralized scalable approach to voltage control of DC islanded microgrids. IEEE Trans Control Syst Technol 24(6):1965–1979
Ali B, Davoudi A (2012) Hierarchical structure of microgrids control system. IEEE Trans Smart Grid 3(4):1963–1976
Li D, Zhu Q, Lin S, Bian XY (2017) A selfadaptive inertia and damping combination control of VSG to support frequency stability. IEEE Trans Energy Convers 32(1):397–398
Trivedi A, Singh M (2017) Repetitive controller for vsis in droopbased ACmicrogrid. IEEE Trans Power Electron 32(8):6595–6604
Ziegler JG, Nichols NB, Rochester NY (1942) Optimum settings for automatic controllers. Trans ASME 64:759–768
Murthy BV, Kumar YVP, Kumari UVR (2012) Application of neural networks in process control: automatic/online tuning of PID controller gains for ± 10% disturbance rejection. In: IEEE Int. Conf. on advanced communication control and computing technologies, pp 348–352
Wu H, Su W, Liu Z (2014) PID controllers: design and tuning methods. In: 9th Conf. on industrial electronics & applications, pp 808–813
Shamsuzzoha M (2013) Closedloop PI/PID controller tuning for stable and integrating process with time delay. Ind Eng Chem Res J 52(36):12973–12992
Bazanella AS, Pereira LFA, Parraga A (2017) A new method for PID tuning including plants without ultimate frequency. IEEE Trans Control Syst Technol 25(2):637–644
Lee JY, Jin M, Chang PH (2014) Variable PID gain tuning method using backstepping control with timedelay estimation and nonlinear damping. IEEE Trans Ind Electron 61(12):6975–6985
Dai A, Zhou X, Liu X (2017) Design and simulation of a genetically optimized fuzzy immune PID controller for a novel grain dryer. IEEE Access 5:14981–14990
Awouda AEA, Mamat RB (2010) Refine PID tuning rule using ITAE criteria. In: Computer & automation engineering, Singapore, vol 5, pp 171–176
Mallesham G, Mishra S, Jha AN (2011) ZieglerNichols based controller parameters tuning for load frequency control in a microgrid. In: IEEE Int. Conf. on energy, automation, and signal, Bhubaneswar, India.
Grybos P, Szczygiel R (2008) PoleZero cancellation circuit with pulse pileup tracking system for low noise chargesensitive amplifiers. IEEE Trans Nucl Sci 55(1):583–590
Chen BS, Hsu YY (2008) A minimal harmonic controller for a STATCOM. IEEE Trans Ind Electron 55(2):655–664
Tan MT, Chan PK, Lam CK, Ng CW (2010) ACBoosting frequency compensation with double polezero cancellation for multistage amplifiers. Circuits Syst Signal Process 29(5):941–951
Huang CY, Wang JJ (2010) A pole/zero cancellation approach to reducing forced vibration in end milling. Int J Mach Tools Manuf 50(7):601–610
Mirhaj SA, Shirazi AN, Ashtiani SJ, Shoaei O (2011) High speed sample and hold design using closedloop polezero cancelation. Microelectron J 42(12):1353–1358
Seino T, Takahashi I, Ishitsu T, Ueno Y, Kobashi K (2012) An alternative pulse height correction method for pole zero cancellation circuitry. J Nucl Instrum Methods Phys Res Sect A 675:133–138
Su JT, Liu CW (2012) Gain scheduling control scheme for improved transient response of DC/DC converters. IET Power Elec 5(6):678–692
Ding C, Zhang W, Jin D, Xie H, Shen P, Chen L (2013) A novel low power UWB cascode SiGe BiCMOS LNA with current reuse and zeropole cancellation. AEUInt J Electron Commun 67(4):323–328
Bayat FM (2013) Fractionalorder unstable polezero cancellation in linear systems. J Process Control 23(6):817–825
Yepes AG, Vidal A, Malvar J, Lopez O, Gandoy JD (2014) Tuning method aimed at optimized settling time and overshoot for synchronous proportionalintegral current control in electric machines. IEEE Trans Power Electron 29(6):3041–3054
Golestan S, Monfared M, Freijedo FD, Guerrero JM (2014) Performance improvement of a prefiltered synchronousreferenceframe PLL by using a PIDtype loop filter. IEEE Trans Ind Electron 61(7):3469–3479
Chopade AS, Khubalkar SW, Junghare AS, Aware MV, Das S (2018) Design and implementation of digital fractional order PID controller using optimal polezero approximation method for magnetic levitation system. IEEE/CAA J Automatica Sinica 5(5):977–989
Gianluca G, Palumbo G (2019) Indepth analysis of polezero compensations in CMOS operational transconductance amplifiers. IEEE Trans Circuits Syst I Regul Papers 66(12):4557–4570
Huiliang C, Zhang Y, Han Z (2019) Polezero temperature compensation circuit design and experiment for dualmass MEMS gyroscope bandwidth expansion. ASME Mechatron 24(2):677–688
Jie Y, Shumin F, Yang QC (2020) Compensation strategies based on Bode step concept for actuator rate limit effect on firstorder plus timedelay systems. Nonlinear Dyn 99:2851–2866
Prasad BS, Jain S, Agarwal V (2008) Universal singlestage gridconnected inverter. IEEE Trans Energy Convers 23(1):128–137
Wen T, Liu J, Tongwen C, Marquez HJ (2006) Comparison of some wellknown PID tuning formulas. Comput Chem Eng J 30(9):1416–1423
Aidan OD (2009) Handbook of PI and PID controller tuning rules, 3rd edn. Imperial College Press
Acknowledgements
This work was supported by Project Grant No: SRG/2019/000648, sponsored by the Startup Research Grant (SRG) scheme of Science and Engineering Research Board (SERB), a statutory body under the Department of Science and Technology (DST), Government of INDIA.
Author information
Authors and Affiliations
Corresponding author
Ethics declarations
Conflict of interest
The authors declare they have no conflict of interest.
Additional information
Publisher's Note
Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
Rights and permissions
Open Access This article is licensed under a Creative Commons Attribution 4.0 International License, which permits use, sharing, adaptation, distribution and reproduction in any medium or format, as long as you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons licence, and indicate if changes were made. The images or other third party material in this article are included in the article's Creative Commons licence, unless indicated otherwise in a credit line to the material. If material is not included in the article's Creative Commons licence and your intended use is not permitted by statutory regulation or exceeds the permitted use, you will need to obtain permission directly from the copyright holder. To view a copy of this licence, visit http://creativecommons.org/licenses/by/4.0/.
About this article
Cite this article
Pavan Kumar, Y.V., Bhimasingu, R. Design of voltage and current controller parameters using small signal modelbased polezero cancellation method for improved transient response in microgrids. SN Appl. Sci. 3, 836 (2021). https://doi.org/10.1007/s4245202104815x
Received:
Accepted:
Published:
DOI: https://doi.org/10.1007/s4245202104815x
Keywords
 Microgrids
 Voltage controller
 Current controller
 PI tuning
 Smallsignal model
 Transient response