Direct Electronic Load Control for Demand Response in a DC Microgrid Using a Virtual Internal Impedance Screening Model and PID Controller
 757 Downloads
 1 Citations
Abstract
To reduce peak loads, direct and indirect load control are common strategies used to change demand during peak hours. Voltage dependent demand response (DR) is a direct load control for changing loads in a DC mircogrid. The characteristics of electronic loads can be controlled with a switchmode DC boost or buck converter. They have faster response to maintain stable output voltage under the fluctuating load condition and heavy load condition. Applying a fast load step to voltage regulator can maintain a well regulated voltages and load currents. The increased load resistance will cause voltage drop when load current is increased during heavy loads. Thus, their adjustable internal load impedances can change the absorbed currents by regulating the duty ratio. In this study, a screening model is employed to estimate the virtual internal impedances of power electronic loads. Then, the desired duty ratio can be determined to perform the DR program, while the boost converter acts to stepup or stepdown the load voltages using the PID (proportionalintegralderivative) controller. For a DC microgrid, simulation results show the feasibility of the proposed methods: (1) exact control of load voltage at both the power source side and load sides and (2) regulation of absorbed currents to modify load voltages and reduce line voltage drops and line losses during heavy loads.
Keywords
Demand response Direct load control Virtual internal impedance Power electronic load Proportionalintegralderivative controllerIntroduction
Power electronic loads are used in DC or AC microgrids and distribution networks, such as naval ships, plugin hybrid electric vehicle charging stations, industrial systems, and smart buildings / houses. DC microgrids have no frequency and reactive power controls and have a good interface connection with the main grid and renewable energy sources, energy storage devices, and power electronic loads [1, 2, 3]. In a DC microgrid, renewable energy sources, energy storage devices, and electronic loads can be directly connected without ACDC converters. DC distributed generations (DGs), such as in photovoltaic (PV) energy, wind power, and fuel cells, and power electronic loads are connected with DC bus via the DCDC converters. Therefore, energy storage and power electronic loads are easy to control the variable demands and to balance the DC DGs. A DC microgrid can also operate in a standalone mode as a single aggregated system with DGs, and can meet the local demands without requiring long transmission lines. Because DC power is sent near the demand site, thus transmitted DC power can increase the efficiency as comparing with AC based microgrids. DGs can be easily integrated into an entire DC power source to supply local loads [4, 5], while line losses and line voltage drops can be decreased. In addition, the microgrid is also connected to the main grid through a bidirectional AC–DC converter. The gridconnected mode is required to be available for local demands during peak hours or DGs blackout. Hence, power stability and uninterruptible power supply can be further improved. Traditionally, regular loads are usually constant powers and constant impedances. During peak hours, energy mediators or aggregators [6, 7, 8] allow the demand response (DR) programs to directly switch off the uncontrolled and lower priority loads, or indirectly control the loads using contractual and intensive DR strategies [9, 10, 11]. With the increasing usages of power electronic loads, these loads are supplied with the DC–DC converters. Therefore, a power electronic load with the switchmode converter is a variable impedance load [12, 13, 14] and can be controlled to affect the power absorption from the DG sources, such as PV energy, wind energy, and battery energy storage [15, 16]. We need to develop a DC DR to adjust the internal parameters of power electronic loads during peak hours [17, 18, 19]. For direct load control in DC microgrid, an aggregator integrates a DR and DGs to adjust the controllable power electronic load, according to the collections of each load current and voltage. Hence, a screening model is designed to estimate the desired effective impedance and duty ratio of power electronic loads with the load voltages and currents. Then, the aggregator announces the desired effective impedance to each load for performing the DR. Finally, each load will be adjusted the duty ratio of DCDC converter accordingly by the controller [15]. Therefore, this study intends to propose a virtual internal impedance screening model to determine the effective impedance. Each power electronic load will adjust the duty ratio of DCDC converter that participates the DR program using the PID controller. Therefore, the proposed method can keep power balance in a DC microgrid by absorbing power from DGs during peak hours.
Power electronic loads are connected with the PWM (pulsewidth modulation) DC–DC converters and DC–AC inverters in DC microgrids or AC distribution networks [4, 17, 20, 21]. DGs can synchronously store energy in the storage devices and supply DC or AC loads. One advantage is that their internal load characteristics can be controlled as variable resistor loads in a DC microgrid and variable impedances in an AC microgrid [17, 22, 23]. When heavy current occurs at the load, the voltage at the load bus will drop due to line resistance and internal impedance of the DC–DC converter or DC–AC inverter. We can control the variable resistors for the power electronic loads. Therefore, absorbed powers from the DGs can be regulated by switchmode converters with PWM controls in a DC microgrid To reduce the DG supply variations, DC–DC boost converters modulate the absorbed powers by increasing the load voltages through the duty ratio regulation [24]. The adopted range (0.95 – 1.05 in perunit value) of load voltages can be fixed or adjustable by using the variable resistors to set the desired load voltage Under the AMI (Advanced Metering Infrastructure) environment, distributed information can be available to synthesize direct load control with adjusting the effective impedance of power electronic load. Therefore, each load can be adjusted to control the power absorption from DG sources and modify the load voltage for achieving the DR program.
In order to reduce the voltage drops and power absorption a screening model need to be incorporated to estimate the internal load impedance. In this study, a voltage dependent DR strategy will be used to directly control power electronic loads during heavy loading These power electronic loads are supplied with the DC–DC converter. Therefore, each power electronic load is equivalent to a variable resistor load. Its equivalent impedance is the correlation with the internal impedance, including the impedance of a converter and static load resistor. The virtual internal impedance screening model, a key technique, is proposed to estimate the effective impedance of power electronic loads during peak hours. Its screening model is derived from nodal voltage equations, Newton–Raphson method, and DC power flow [25, 26, 27]. Nodal voltage equations are used to model the whole DC microgrid and to express the variable resistor of each power electronic load. Therefore, the “virtual internal impedance” is a screening model in term of the voltages to estimate the equivalent impedance of each power electronic load. The virtual internal impedance can be estimated using the whole nodal voltages from the online metering voltages in a DC microgrid. While the metering nodal voltages changes, the estimated virtual internal impedance is sensitively used to identify the heavy loads during peak hours. A DC power flow with the current injection method [27] and the Newton–Raphson method [25, 26] is employed to validate the proposed screening model. Therefore, the equivalent impedance of each power electronic load can be measured and directly controlled at the common coupling point. By controlling the variable resistor of power electronic loads, the power absorption delivered to each electronic load can be regulated while participates in DR. The duty ratio deviation is determined to adjust the boost converter by using the voltage conditions within its maximum and minimum permissible duty ratios. When the load voltages exceed the critical threshold values, 0.95 − 1.05 in perunit value, the desired duty ratio is estimated to adjust the boost converter through the controller. The proposed screening model and controller scheme intend to perform the direct load control, while modify the load voltage at each load and reduce the power loss on each distribution feeder.
PI, PID, and fuzzyPID controllers [28, 29, 30] can regulate the duty ratio to the desired operating point of a DCDC converter or a DCAC inverter. However, a limitation of PI and PID controllers is that you need to tune the controller parameters to improve the control performance to meet various operating conditions. Fuzzybased control methods can automatically tune the controller parameters. However, these methods require the design of inference rules or a lookup table for the determination of the controller parameters. Therefore, a Ziegler–Nicholasbased [30, 31, 32] tuning method is used to design the three control parameters, including proportional (P), integral (I), and derivative (D) gains. This avoids the trialanderror design procedure, minimizes overshoot, improves transient responses, decreases steadystate errors, and improves control performances. In addition, selftuning based optimization methods [33, 34] are also used to determine the optimal control parameters to improve control performance and transient responses, such as particle swarm optimizationPID, evolutionary programmingfuzzy control, and genetic algorithmPI. However, these methods are used only to tune the optimal control parameters, but they can not estimate the desired duty ratio of f a converter or an inverter. Based on direct load control mode, the switchmode converters with PWM controls are suffice to regulate power electronic loads for DR program. The proposed “virtual internal impedance” screening model with a tuned PID controller can achieve the intended DR aim. For a DC microgrid, simulation results show that the proposed methods can act on the DR program to reduce demand and that exact load voltages can be accurately regulated in a specific range. The proposed screening model and control scheme can also be easily implemented in an embedded system or an intelligent/a smart meter.
The remainder of this paper is organized as follows. Section “Methodology” describes the methodology, including the DC microgrid model, virtual internal impedance screening model, PID controller, and the procedure of electronic load DR. Sections “Simulation Results and Discussions” and “Conclusion” present simulation results, discussions, and conclusion demonstrating the efficiency of the proposed methods and conclusions, respectively.
Methodology
DC Microgrid Model
A DC microgrid has a radial configuration comprising distributed energy sources, distribution feeders, storage devices, and local communication systems. It can be connected to the main grid through an AC–DC converter at the point of common coupling. For regular DC loads, demands, such as PV energy, smallscale wind energy, and storage devices, come directly from the distributed energy sources at a DC bus. The PV output power and voltages are easily influenced by atmospheric conditions such as temperature, solar radiation, rain, and moderatetoheavy cloud cover. The maximum power point tracking (MPPT) algorithm is used to estimate the maximum output power and maximum power point voltage (MPPV) [35, 36, 37, 38]. The lumped output current, I_{S}, and lumped output power, P_{S}, for a PV array with p identical PV panels connected in parallel can be expressed as follows:
Virtual Internal Impedance Screening Model
As seen in Fig. 2b, intelligent/smart meters are used to gather information about voltages, currents, and powers in a DC microgrid. In AMI environment, head end systems are specialized software for connecting the meter data management (MDM) system and intelligent/smart meters. Metering data from each consumer allows a power utility to perform the DR program, including direct load control, indirect load control, and incentive control during peak hours. Hence, power utility can deliver commanded messages for controlling smart appliances with remote switches in each consumer. The AMI can also provide available information for DR, including the load profiles, voltages, and currents [10, 38]. By the combining the automatic direct load control method, the proposed “virtual internal impedance screening model” is employed to estimate the effective impedance of power electronic loads during peak hours with the load voltages and currents. When the load voltage drop is sensed, the boost converter increases the duty ratio to adjust the internal impedance, and the absorbed current will decrease to meet the DR. This can maintain well regulated voltage to control the power absorption for each electronic load during peak hours.
Regulate Duty Ratio with PID Controller
Controller parameter selections for ZieglerNicholas step response method
K _{ P}  K _{ I}  K _{ D}  

P  k_{1}/ 2  —  — 
PI  k_{1}/ 2  K_{P}/ k_{1}  
PD  k_{1}/ 2  —  K_{P} ×(T_{2} − T_{1}) 
PID  k_{1}/ 2  K_{P}/ k_{1}  K_{P} ×(T_{2} − T_{1}) 
The Procedure of Electronic Load Demand Responses
Simulation Results and Discussions
The Results of Virtual Internal Impedance Screening
For a DC microgrid as in Fig. 5, DC power flow analysis was used to simulate the normal load and heavy load using the current injection and Newton–Raphson methods, as seen by the bus voltages and absorbed load currents in Fig. 8a and b. With a supposed demand increase on the power electronic loads, 1# to 3#, at busses, 2# to 4#, the bus voltages drop at each load bus due to absorbed load current and line voltage drop increases. While the load voltages were below the critical threshold value, 0.95 pu, the proposed virtual impedance model was employed to estimate the internal load changes, as shown in Fig. 8c. It can be seen that the internal impedances had large deviations at busses 2#, 3#, and 4# (red dash line). The procedure for the virtual internal impedance estimation was as follows:
 Step 1)

obtain the microgrid parameters, including the injection current, line resistors, and load internal resistors, then perform the DC power flow to obtain whole nodal voltages in a DC microgrid
 Step 2)

obtain the load voltages as seen in Fig. 8a and identify the voltage levels,
 Step 3)

estimate the virtual internal impedances as the voltage level was less than 0.95 pu.
It can be seen that the original internal impedances were R_{2} = 0.98 pu, R_{3} = 0.98 pu, R_{4} = 0.98 pu, R_{5} = 1.00 pu, and R_{6} = 0.98 pu. Without regulating the boost converters, the load voltages had deviations, [ΔV_{12}, ΔV_{13}, ΔV_{14}, ΔV_{15}, ΔV_{16}, ΔV_{17}]=[0.0488, 0.0589, 0.0589, 0.0475, 0.0574, 0.0568] per unit value, and the absorbed load currents gathered at the 2#, 3#, and 4# busses. The estimated virtual internal impedances were computed using Eqs. 18 and 19, as [R_{2}, R_{3}, R_{4}, R_{5}, R_{6}, R_{7}]=[0.88*, 0.90*, 0.90*, 1.00, 0.97, 1.00] in Fig. 8c. The absorbed load currents could be computed using Eq. 20, as [I_{2}, I_{3}, I_{4}, I_{5}, I_{6}, I_{7}]=[1.0809*, 1.0457*, 1.0457*, 0.9525, 0.9718, 0.9432] per unit value, during peak hours. Thus, the power electronic loads, 1# to 3#, were required to regulate by the DCDC boost converters (24VDC/48VDC). The regulated values of duty ratios were estimated using Eq. 24, as [\({\Delta } D_{2}^{\mathrm {}}\), \({\Delta } D_{\mathrm { 3}}^{\mathrm {}}\), \({\Delta }D_{4}^{\mathrm {}}\), \({\Delta } D_{5}^{\mathrm {}}\), \({\Delta } D_{6}^{\mathrm {}}\)]=[0.0524*, 0.0417*, 0.0417*, 0.0000, 0.0051]. In this study, no critical loads needed to switch off when the voltage sagged during the heavy load. Voltage dependent DR was used to directly control the loads and to change the absorbed currents to each power electronic load using the boost converters. After the direct load control process, the load voltage levels could be raised the specified range, > 0.95 pu, using the PID controller. Then, the internal load impedance of loads, 1# to 3#, increased to reduce the absorbed currents of loads, as seen in Fig. 8b and c. The final duty ratios of loads, 1# to 3#, were 0.5524, 0.5417, and 0.5417, respectively.
When a DC microgrid operated in a standalone mode, DG sources could completely supply local loads without main grid connection. However, renewable energy sources were variable because of environmental conditions. Hence, energy storage devices were used to provide backup capacity for the microgrid and to enhance the system stability and reliability. When DG resources was greater than the local load demand, extra energy would charged into batteries. In the other hand, when DG resources were less than load demand, then energy storage would be discharged. Then, the proposed virtual internal impedance screening model acted to identify the heavy loads. The PID controllers also acted to modify the absorbed currents from the DG sources, or nonpriority load (such as Load 6#) needed be disconnected to keep the power supply continued for controllable power electronic loads. The feasibility of virtual internal impedance screening was validated through simulation tests.
The Results of Voltage Dependent DRs for Electronic Loads
According to the changes in the virtual internal load impedances, power electronic loads 1# to 3# had large deviations to regulate the duty ratios of boost converters. The procedure of DR for the power electronic loads was

the virtual internal load impedance can be estimated by offline analysis using the DC power flow, and online analysis using the measurement data from smart meters in an AMI environment,

the control parameters of the PID or PI controller can be easily determined with the Ziegler–Nicholasbased tuning rule,

the exact load voltages can be accurately regulated in the specific range at both the power source and load sides.
We provide a promising method for changing the internal impedance of power electronic loads, then controlling the power flow from the DC power source to each load in the DR strategy. The feasibility of the proposed methods has been validated.
Conclusion
Voltage dependent DR with a virtual internal impedance model and a PID Controller was established in a DC microgrid. A virtual impedance model was used to estimate the internal impedance changes in power electronic loads. According to the internal impedance changes, the desired duty ratio could be determined. Based on direct load control, the PID or PI controller regulated the boost converter to change the internal impedances, and reduced the heavy loads with the voltagemode boost converter operating in continuous conduction mode. Through the boost converter, the absorbed currents could be regulated from the DG source to each load side during peak hours. Hence, bus voltages, line voltage drops, and power losses were improved. For a DC microgrid, simulation results showed the feasibility of the proposed procedure for a DR program. In this study, DC power flow analysis was used to validate the results: (1) virtual impedance screening and (2) voltage dependent DRs for power electronic loads.
The simulation results confirmed that the proposed methods can be extended to a real smart microgrid. They ensure stable operation, keeping the bus voltages and power flow running flexibly within the limits for energy management applications. Under an AMI environment, the proposed methods could be further embedded into the existing MDM system, which gather voltage, current, and power from the whole DC microgrid. Metering data and bidirectional communication support the online applications in small or largescale microgrids. Thus, the proposed virtual impedance screening model has the capability to estimate the changes in internal impedances and duty ratios. Based on direct load control, the tuned PID controller can rapidly regulate the absorbed currents. In addition, the proposed methods can be easily implemented in an embedded system, a pcbased monitor, or an intelligent / a smart meter. Based on cloud computing, the wire / wireless communication technique is used to connect a network including one or more meters and a MDM system, which transmits metering data for identifying the heavy loads. Based on direct load control mode, the proposed methods and cloud computing can be integrated to control the heavy loads to keep the power supply continued for controllable loads during peak hours. With its feasibility evaluations, this technology support indicates that the proposed models can be easily implemented with inexpensive software and an embedded design device.
Notes
Acknowledgments
This work is supported in part by the Ministry of Science and Technology (MOST), Taiwan, under contract number: MOST 1042221E244010 and MOST 1052221E244010, duration: August 1 2015 ∼ October 31 2017.
References
 1.Dragicevic T, Lu X, Vasquez JC, Guerrero JM (2015) DC microgridsPart I: a review of control strategies and stabilization techniques. IEEE Trans Power Electron 31(7):4876–4891Google Scholar
 2.Dragicevic T, Lu X, Vasquez JC, Guerrero JM (2015) DC microgridsPart II: a review of power architectures, applications, and standardization issues. IEEE Trans Power Electron 31(5):3528–3549CrossRefGoogle Scholar
 3.Che L, Shahidehpour M (2014) DC microgrid: economic operation and enhancement of resilience by hierarchical control. IEEE Trans Smart Grid 5(5):2517–2526CrossRefGoogle Scholar
 4.Reddy KS, Kumar M, Mallick TK, Sharon H, Lokeswaran S (2014) A review of integration, control, communication and metering of renewable energy based smart grid. Renew Sustain Energy Rev 38:180–192CrossRefGoogle Scholar
 5.Chauhan RK, Phurailatpam C, Rajpurohit BS, GonzalezLongatt FM, Singh SN (2017) Demandside management system for autonomous DC microgrid for building. Technol Econ Smart Grids Sustain Energy 2:4CrossRefGoogle Scholar
 6.Pacific Gas and Electric Company, Aggregator Programs, Demand Response Fact sheet (2013)Google Scholar
 7.RodriguezMolina J, MartinezNunez M, Martinez JF, PerezAguiar W (2014) Business models in the smart grid: challenges, opportunities and proposals for prosumer profitability. Energies 7:6142–6171CrossRefGoogle Scholar
 8.Gulich O (2010) Technological and business challenges of smart gridsaggregator’s role in current electricity market. Master’s thesis, Lappeenranta University of Technology Faculty of Technology and Electrical EngineeringGoogle Scholar
 9.Lu N (2012) An evaluation of the HVAC load potential for providing load balancing services. IEEE Trans Smart Grid 3(3):1263–1270CrossRefGoogle Scholar
 10.Wang Z, Paranjape R, Sadanand A, Chen Z (2013) Resiential demand response: an overview of recent simulation and modeling applications.. In: The 26th annual IEEE Canadian conference on electrical and computer engineering, pp 1–6Google Scholar
 11.Chang LY, Chung Y, Chen SJ, Kuo CL, Lin CH (2016) Demand response and ancillary service management using fractionalorder integral indicator and dynamic game model for an aggregator program in smart grids. Technol Econ Smart Grids Sustain Energy 1(16):1–12Google Scholar
 12.Weaver W (2011) Dynamic energy resource control of power electronics in local area power networks. IEEE Trans Power Electron 26(3):852–859CrossRefGoogle Scholar
 13.Kazemlou S, Mehraeen S, Saberi H, Jagannathan S (2017) Stability of the smallscale interconnected DC grids via outputfeedback control. IEEE J Emerg Sel Top Power Electron 5(3):960–970CrossRefGoogle Scholar
 14.Negri S, Tironi E, Danna DS (2017) Integrated control strategy for island operation in smart grids: virtual inertia and ancillary services.. In: 2017 international conference on environment and electrical engineering and 2017 IEEE industrial and commercial power system Europe, pp 1–6Google Scholar
 15.Nguyen KL, Won DJ, Ahn SJ, Chung IY (2012) Power sharing method for a grid connected microgrid with multiple distributed generators. J Electr Eng Technol 17(4):459–467CrossRefGoogle Scholar
 16.Basic H, Dragicevic T, Pandzic H, Blaabjerg F (2017) DC microgrids with energy storage systems and demand response for providing support to frequency regulation of electrical power systems.. In: 2017 19th European conference on power electronics and applicationsGoogle Scholar
 17.MohsenianRad H, Davoudi A (2014) Towards building an optimal demand response framework for dc distribution networks. IEEE Trans Smart Grid 5(5):2626–2634CrossRefGoogle Scholar
 18.Mackay L, Kolios P, RamirezElizondo L, Bauer P (2015) Voltage dependnt demand response with dynamic hysteresis thresholds in DC microgrids. In: 2015 IEEE Eindhoven power techGoogle Scholar
 19.RamirezFonseca I, Mackay L, Van der Blij NH, Hailu Tg, RamirezElizondo L, Bauer P (2016) Impact of voltage dependent demand response on the dynamic of DC microgrids.. In: International conference on sustainable green building and communitiesGoogle Scholar
 20.Nasir M, Khan HA (2016) Solar photovoltaic integrated building scale hybrid AC/DC microgrid.. In: 2016 5th IET international conference on renewable power generation, pp 1–6Google Scholar
 21.Pavan Kumar YV, Bhimasingu R (2016) Performance analysis of static versus rotary DC/AC power converter for hybrid renewable energy based microgrid applications.. In: 2016 IEEE Region 10 conference, pp 1456–1461Google Scholar
 22.Mohamed A, Mohammed O (2010) Power flow control in dc distribution systems. In: Proceedings of the IEEE NAPS. Arlington, pp 1–7Google Scholar
 23.MohsenianRad H, Davoudi A (2013) Optimal demand response in dc distribution network. In: IEEE international conference on smart grid communication. Vancouver, pp 564–569Google Scholar
 24.Maknouninejad A, Qu Z, Lewis FL, Davoudi A (2014) Optimal, nonlinear, and distributed designs of droop controls for DC microgrids. IEEE Trans Smart Grid 5(5):2508–2516CrossRefGoogle Scholar
 25.Glover D, Sarma M Power system analysis and design. PWS Publishing Company, Boston. ISBN0534939600Google Scholar
 26.Brown HE (1975) Solution of large network by matrix methods. Wiley, New YorkGoogle Scholar
 27.Ma Y, Karady GG (2009) Investigating grounding grid integrity based on the current injection method.. In: 2009 North American power symposium, pp 1–5Google Scholar
 28.Kuo CL (2007) Design of an adaptive Fuzzy slidingmode controller for chaos synchronization. Int J Nonlinear Sci Numer Simul 8(4):631–636CrossRefGoogle Scholar
 29.Meza JL, Santibaenz V, Soto R, Llama MA (2012) Fuzzy self tuning PID semi global regulator for robot manipulators. IEEE Trans Ind Electron 59:2391–2401CrossRefGoogle Scholar
 30.Singhal R, Padhee S, Kaur G (2012) Design of fractional order PID controller for speed control of dc motor. Int J Sci Res Publ 2(6):1–8Google Scholar
 31.Ziegler JG, Nichols NB (1942) Optimum settings for automatic controllers. Trans ASME 64:759–768Google Scholar
 32.Singhal R, Padhee S, Kaur G (2012) Design of fractional order PID controller for speed control of dc motor. Int J Sci Res Publ 2(6):1–8Google Scholar
 33.Chen GY, Perng JW, Ma LS (2015) DSP based BLD motor controller design with auto tuning PSOPID algorithm.. In: 2015 IEEE/SICE international symposium on system integrationGoogle Scholar
 34.Arulmozhiyal R (2012) Design and implementation of fuzzy PID controller for BLDC motor using FPGA.. In: 2012 international conference on power electronics, drives and energy systemsGoogle Scholar
 35.Kuo CL, Lin CH, Yau HT, Chen JL (2013) Using selfsynchronization error dynamics formulation based controller for maximum photovoltaic power tracking in microgrid systems. IEEE J Emerg Sel Top Circ Syst 3(3):459–467CrossRefGoogle Scholar
 36.Kuo CL, Chen JL, Chen SJ, Kao CC, Yau HT, Lin CH (2017) Photovoltaic energy conversion system fault detection using fractionalorder color relation classifier in microdistribution systems. IEEE Trans Smart Grid 8(3):1162–1172CrossRefGoogle Scholar
 37.Wang Z, Paranjape R, Sadanand A, Chen Z (2013) Resiential demand response: an overview of recent simulation and modeling applications.. In: 26th annual IEEE Canadian conference on electrical and computer engineering, pp 1–6Google Scholar
 38.Brusco G, Burgio A, Menniti D, Pinnarelli A, Sorrentino N (2014) Energy management for an energy district with demand response availability. IEEE Trans Smart Grid 5(5):2385–22393CrossRefGoogle Scholar
 39.Chen JL, Kuo CL, Chen SJ, Kao CC, Zhan TS, Lin CH, Chen YS (2016) DCside fault detection for photovoltaic energy conversion system using fractionalorder order dynamic error based fuzzy petri net integrating with intelligent meters. IETRenew Power Gener 10(9):1318–1329CrossRefGoogle Scholar
 40.Marasco K (2011) How to apply dctodc stepup (boost) regulator successfully, Analog Dialogue 4509 Back Burner, pp 13. www.analog.com/analogdialogue