Design and Evaluation of SunSpec-Compliant Smart Grid Controller with an Automated Hardware-in-the-Loop Testbed
- 726 Downloads
With increasing penetrations of inverter-based, renewable energy resources on electrical grids around the world, new distributed energy resource (DER) interconnection and interoperability requirements have been introduced to address emerging power system operator needs. The inverter-based power conversion systems are capable of communicating with grid operators, providing voltage and frequency support, and supporting the grid during faults. However, DER vendors are under pressure to quickly and reliably update the interoperability and electrical capabilities of their equipment for different jurisdictions with the rapidly changing landscape of disparate codes and standards. The necessary power hardware required for testing power systems under the wide variety of operational conditions may be untenable for many organizations. Therefore, we introduce an approach for the concurrent development of controls and application software through a controller hardware-in-the-loop (CHIL) testbed integrated with an automated testing platform that allows for the cost-effective, flexible evaluation of advanced grid support functions without the need for large and expensive power hardware. We show this CHIL capability through the demonstration and automation of interconnection tests with a 34.5 kW Austrian Institute of Technology (AIT) smart grid converter (SGC) connected to a Typhoon HIL system. We have demonstrated the CHIL system with regards to connect/disconnect, active power curtailment, fixed power factor, reactive power control, volt-var, and frequency-watt advanced grid functionality tests. For all tests, the automated CHIL testing protocols for advanced functions were sufficient to demonstrate and evaluate the grid support behavior of the equipment under test.
KeywordsSystems integration Grid integration Inverter design Advanced grid-support functions Controller hardware-in-the-loop DER interoperability
Recently, distributed energy resource (DER) interconnection and interoperability codes and standards around the world are being revised to provide grid operators with tools for providing frequency, voltage, and protection services [1, 2, 3]. This rapid evolution is driven by grid operator needs as greater penetrations of distributed renewable energy resources are displacing traditional thermal generation. The widespread adoption and distributed nature of DER is causing voltage regulation challenges for distribution circuits ; greater frequency deviations due to reduced inertia in power systems ; and new protection challenges from fuse, relay, and circuit breaker desensitization . In order to maintain a safe, stable power system, DERs must actively participate in grid operations.
DERs can provide grid services through both programmable autonomous functions as well as remotely commanded actions. Many of these functions were described in an EPRI report  and later formalized in IEC Technical Report 61850-90-7 —soon to be standardized in IEC 61850-7-420 . Many of these same functions—or variations on them—have been required in Europe [2, 3], and more recently in California and Hawaii in the U.S. In its recent full revision currently undergoing the final ballot phase, the U.S. national interconnection standard, IEEE Std. 1547 , added many of these functions and interoperability requirements. With the addition of these requirements, there are two emerging needs: (a) equipment vendors must redesign their equipment to meet new grid standards by systematically validating DER performance and (b) standards development organizations (SDOs) must establish certification protocols (e.g., IEEE 1547.1  and UL 1741 ) to list equipment.
Validating smart inverter grid-support functions without expensive power laboratory equipment, using low-voltage benchtop equipment,
Executing certification tests to verify controller operation prior to hardware integration,
Allowing quick design iterations of the communication system to provide interoperability for a range of standards , and
Quickly refining SDO draft interconnection and interoperability codes and standards prior to publication.
CHIL methodology provides key benefits over traditional full-scale power laboratory testing by minimizing the power equipment required to evaluate the system while also evaluating control logic and interoperability interfaces prior to integration with hardware. By eliminating power requirements, the CHIL test setup has the flexibility to easily operate for a range of systems (e.g. single and three-phase devices, different nameplate ratings, grid functions, and operating capabilities), control schemes, and grid conditions. CHIL has been demonstrated in a wide variety of DER utilized grid topologies, including Medium Voltage DC equipment , microgrids [22, 23], and smart grids  and is widely accepted as a cost-effective method to determine the behavior of power systems under a variety of grid operating conditions.
With high demand for certification lab time equipment and the short timelines for equipment listing, a high-throughput testing method is sorely needed for rapid deployment of smart grid technologies. Power hardware-in-loop (PHIL) has previously been used to determine PV inverter behavior to certification requirements  but CHIL is more slowly entering certification standards as an acceptable alternative to power system testing. Standards development organizations have recognized that it becomes increasingly difficult to test full-scale equipment as power electronics equipment continues to grow to megawatt-scale devices or networks of devices. The IEEE 2030.8 standard for microgrid controller testing  will likely include a CHIL testbed and a newly started IEEE P2004 standard  will include recommended practices for HIL testing of electric power apparatuses and controls. In January 2014, NREL released a test protocol for voltage and frequency trip and ride through experiments that allowed signal injection . Signal injection is a type of CHIL experiment in which the power system is not perturbed, but rather the pertinent DER measurements are changed to reflect the grid conditions of the test. For instance, if a high voltage trip test needed to be completed on a 2 MW inverter, a 2 MVA or larger grid simulator would not need to generate the high voltage test conditions, but rather the equivalent scaled DER voltage measurement signal would be injected into the controller to represent the high voltage condition. In the IEEE 1547 revision process , signal injection was discussed at length and in the balloted version it is allowable for type tests “provided that the completeness of the required test is not compromised.” At this time, it is unclear how many DER vendors or Nationally Recognized Testing Laboratories (NRTLs) will use this technique; however, inclusion of this option indicates a shift in testing toward CHIL certification testbeds.
One final goal of this project is to provide institutions in emerging economies, universities, and utilities with a low-cost, low-voltage platform for conducting DER grid-support research. As emerging economies begin to experience rapid growth in power demand and integrate higher penetrations of renewables, there is a need to establish DER requirements for grid support functions. While laboratories in countries with a significant history in DER integration possess extensive testbeds for evaluating the performance of DER equipment with grid simulators, PV/battery simulators, data acquisition systems, meters, and communication infrastructure, in many cases, especially for emerging economies such as India, Mexico, and South Africa, expensive power systems testing and evaluation infrastructure for full-scale unit testing is limited. These countries require a means to quickly develop results-based interconnection standards and evaluate equipment to these requirements. Therefore, versatile and flexible testing methodologies are needed to understand system response without the risk and expense of full-scale power system evaluation. Using the CHIL benchtop system, universities, research laboratories, regulators, utilities, and equipment vendors could collaborate to develop comprehensive interconnection and interoperability standards for their country.
In this paper, the design and use of a smart inverter CHIL (Si-CHIL) platform consisting of an integrated SunSpec-compliant server, smart grid controller, CHIL hardware/software system, and automated test platform is presented. The testing methodology along with results of a number of advanced grid-support functions including connect/disconnect, active power curtailment, fixed power factor, reactive power, volt-var, and frequency-watt are provided.
Laboratory Testbed Configuration
The EUT represents a 34.5 kW grid-tie photovoltaic inverter with full four-quadrant operation, capable of providing a broad range of advanced grid support capabilities via the AIT SGC controller. The SGC uses a propriety suite of algorithms for advanced inverter controls. The details of the algorithms, their capabilities, and disadvantages are not discussed here (but covered in [17, 18, 19]), as the purpose of the experimental setup described herein is to demonstrate the flexibility of evaluating a wide variety of control schemes and algorithms.
Although the EUT is capable of four-quadrant operation, in these tests, only positive active power operation was witnessed because and no storage was present. The DC power was provided by a simulated PV array with a maximum power point (P mp) of 36.24 kW at 1000 W/m2. The EUT response to different SunSpec settings was initially assessed using the Typhoon HIL Control Center and the SunSpec Dashboard  to determine the EUT functional limitations (e.g., minimum and maximum grid frequency and voltage) and available grid support functions. These limitations where observed when conducting the automated experiments.
The Si-CHIL setup is capable of testing the EUT compliance to any number of grid codes and standards using the SVP. For this work, simple experiments were scripted to evaluate the grid-support capabilities of the EUT. Data was collected from the Typhoon HIL through the Typhoon HIL Python API every 200 ms from analog signals representing the AC and DC current and voltage, and from calculated CHIL channels including root mean square (RMS) AC power, RMS reactive power, and power factor. In the experiments, the PV power was adjusted by setting the simulated PV irradiance level, and the grid voltage and frequency were changed for all three single-phase voltage sources simultaneously via the Typhoon API.
The connect/disconnect function (IEC 61850-90-7 INV1) isolates the DER from the grid. Typically, isolation is created by gate blocking the H-bridge semiconductor switches, but it could also be accomplished by actuating a contactor to provide galvanic isolation.
Active Power Curtailment
Fixed Power Factor
As shown by the CHIL experiments, test protocols can be quickly scripted and automated using the SunSpec SVP. The CHIL-SVP test configuration successfully enabled, adjusted, and executed six grid-support function certification tests using the AIT SGC as the EUT. The results show the effectiveness of using the CHIL approach to assist programmers in designing DER firmware to catch design mistakes prior to deployment in hardware. The setup and operation of this type of testbed is significantly quicker and less expensive than running the experiments with power equipment.
The combination of the SVP and CHIL platforms are particularly useful for testing EUTs to certification protocols requiring a number of operating modes and/or settings. This capability reduces the burden on test engineers by automating the experiments and data collection, while still validating the functionality of the EUT early in the design process. Furthermore, coupling the interoperability (i.e., communications) tests with the electrical behavior testing is effective for certifying the equipment for both sets of requirements [33, 34]. In this case, the EUT was shown to properly understand and update its behavior when receiving standardized SunSpec Modbus commands. Additional communications protocols such as IEEE 2030.5 (Smart Energy Profile 2.0), IEEE 1815 (DNP3), or IEC 61850 could be easily substituted in the SunSpec SVP to validate other communication protocols.
Complete certification experiments with limited power system hardware, e.g., no grid simulator, PV simulator, data acquisition system, load banks, etc.
Test large EUT controllers prior to integration with power equipment.
Accelerate the DER design cycle for interconnection and interoperability compliance.
Create optimized testing protocols for certification standards.
In this work, we have shown this CHIL capability through the demonstration and automation of advanced grid support tests with a 34.5 kW AIT SGC connected to a Typhoon HIL simulated power converter. We have demonstrated CHIL system response to connect/disconnect, active power curtailment, fixed PF, reactive power, VV, and FW advanced grid functions.
However, significant work remains to make this method of experimentation mainstream. As a first step, Sandia and SunSpec regularly release SVP test scripts in an online repository  for DER vendors, NRTLs, and other interested parties. Through the collaboration within ISGAN-SIRFN the partners also plan to actively contribute the work to national and international standards to introduce advanced CHIL methodologies as essential part of future DER certification testing.
Additionally, it is the intention of the team to provide the integrated CHIL certification platform to academic and research institutions around the world—especially in emerging economies where access to costly power equipment may be limited. In these markets, it will be particularly useful for Si-CHIL users to develop and refine interconnection and interoperability certification standards using the results from the integrated platform without the added time, electrical exposure, and expense of conducting full-scale power systems testing.
Sandia National Laboratories is a multimission laboratory managed and operated by National Technology and Engineering Solutions of Sandia, LLC, a wholly owned subsidiary of Honeywell International, Inc., for the U.S. Department of Energy’s National Nuclear Security Administration under contract DE-NA0003525.
The participation of AIT within ISGAN-SIRFN is funded in the frame of the IEA Research Cooperation program by the Austrian Ministry for Transport, Innovation and Technology under contract no. FFG 839566. The development of the AIT SGC was supported by the Austrian Ministry for Transport, Innovation and Technology (bmvit) and the Austrian Research Promotion Agency (FFG) under the “Energy Research Program 2015” in the SPONGE project (FFG no. 848915)
- 2.Rosewater D, Johnson J, Verga M, Lazzari R, Messner C, Bründlinger R, Johannes K, Hashimoto J, Otani K (2015) International development of energy storage interoperability test protocols for renewable energy integration. EU PVSEC, Hamburg, 14–18 SeptGoogle Scholar
- 3.Bründlinger R Advanced smart inverter and DER functions requirements in latest European grid codes and future trends. Solar Canada, 8 Dec. 2015Google Scholar
- 4.Palmintier B, Broderick R, Mather B, Coddington M, Baker K, Ding F, Reno M, Lave M, Bharatkumar A (2016) On the path to sunshot: emerging issues and challenges in integrating solar with the distribution system. National Renewable Energy Laboratory, NREL/TP-5D00-65331Google Scholar
- 6.Seguin R, Woyak J, Costyk D, Hambrick J, Mather B (2016) High-penetration PV integration handbook for distribution engineers. NREL Technical Report NREL/TP-5D00-63114Google Scholar
- 7.Seal B (2014) Common functions for smart inverters, version 3. EPRI Report 3002002233, 21 FebGoogle Scholar
- 8.IEC Technical Report IEC 61850-90-7 (2013) Communication networks and systems for power utility automation–part 90-7: object models for power converters in distributed energy resources (DER) Systems. Edition 1.0Google Scholar
- 9.IEC 61850-7-420 (2009) Communication networks and systems for power utility automation—part 7-420: basic communication structure—distributed energy resources logical nodesGoogle Scholar
- 10.IEEE Standard 1547-2003 (2003) Standard for interconnecting distributed resources with electric power systemsGoogle Scholar
- 11.IEEE Standard 1547.1-2005 (2005) Standard for conformance test procedures for equipment interconnecting distributed resources with electric power systemsGoogle Scholar
- 12.Underwriters Laboratories 1741 Ed. 2 (2010) Inverters, converters, controllers and interconnection system equipment for use with distributed energy resourcesGoogle Scholar
- 13.Johnson J, Bründlinger R, Urrego C, Alonso R (2014) Collaborative development of automated advanced interoperability certification test protocols for PV smart grid integration. EU PVSEC, Amsterdam, Netherlands, 22–26 SeptGoogle Scholar
- 14.Verga M, Lazzari R, Johnson J, Rosewater D, Messner C, Hashimoto J (2016) SIRFN draft test protocols for advanced battery energy storage system interoperability functions. ISGAN Annex #5 Discussion PaperGoogle Scholar
- 15.SunSpec Alliance. SunSpec System Validation Platform (SVP), software, http://sunspec.org/sunspec-svp/
- 16.Johnson J, Fox B (2014) Automating the Sandia advanced interoperability test protocols. In: 40th IEEE PVSC, Denver, 8–13 JuneGoogle Scholar
- 17.Miletic Z. AIT Smart Grid Converter (SGC) control platform: using controller hardware in the loop for the AIT Smart Grid Converter (SGC) control platform, Webinar. http://info.typhoon-hil.com/recorded-webinar-ait-smart-grid-converter-control-platform-and-controller-hardware-in-the-loop
- 18.Bründlinger R. SunSpec and AIT Smart Grid Converter (SGC) control platform: using controller hardware in the loop to implement SunSpec protocols in the AIT SGC control platform, WebinarGoogle Scholar
- 19.Bründlinger R, Ablinger R, Miletic Z (2016) AIT Smart Grid Converter (SGC) controller featuring SunSpec protocol support utilizing Hardware-in-the-Loop (HIL) technology, SunSpec Meeting, September 13Google Scholar
- 20.Johnson J, Ablinger R, Bruendlinger R, Fox B, Flicker J (2017) Interconnection Standard Grid-Support Function Evaluations using an Automated Hardware-in-the-Loop Testbed, IEEE PVSC, Washington, DC, 25–30 JuneGoogle Scholar
- 23.Panwar M, Lundstrom B, Langston J, Suryanarayanan S, Chakraborty S (2013) An overview of real time hardware-in-the-loop capabilities in digital simulation for electric microgrids. In: 2013 North American Power Symposium (NAPS), Manhattan, pp 1–6. https://doi.org/10.1109/NAPS.2013.6666861
- 24.Lundstrom B, Chakraborty S, Lauss G, Bründlinger R, Conklin R (2016) Evaluation of system-integrated smart grid devices using software- and hardware-in-the-loop. In: 2016 IEEE power & energy society innovative smart grid technologies conference (ISGT), Minneapolis, pp 1–5. https://doi.org/10.1109/ISGT.2016.7781181
- 25.Lundstrom B, Shirazi M, Coddington M, Kroposki B (2013) An advanced platform for development and evaluation of grid interconnection systems using hardware-in-the-loop: part III—grid interconnection system evaluator. In: 2013 IEEE green technologies conference (GreenTech), Denver, pp 392–399. https://doi.org/10.1109/GreenTech.2013.67
- 26.IEEE Project. P2030.8—standard for the testing of microgrid controllers. https://standards.ieee.org/develop/project/2030.8.html
- 27.IEEE Project. P2004—hardware-in-the-Loop (HIL) simulation based testing of electric power apparatus and controls. https://standards.ieee.org/develop/project/2004.html
- 28.Hoke A, Chakraborty S, Basso T, Coddington M (2014) Beta test plan for advanced inverters interconnecting distributed resources with electric power systems. NREL Technical Report NREL/TP-5D00-60931Google Scholar
- 29.Electric Power Research Institute (2017) IEEE 1547—new interconnection requirements for distributed energy resources: fact sheet. Report 3002011346Google Scholar
- 30.SunSpec Alliance. SunSpec Dashboard, software, http://sunspec.org/sunspec-dashboard/
- 31.Johnson J, Schenkman B, Ellis A, Quiroz J, Lenox C (2012) Initial operating experience of the 1.2-MW La Ola photovoltaic system. In: 38th IEEE PVSC, Austin, TX, 4 JuneGoogle Scholar
- 32.VDE Reference (2008) VDE-AR-N 4105 power generation systems connected to the low voltage distribution network -technical minimum requirements for the connection to and parallel operation with low voltage distribution networksGoogle Scholar
- 33.Gonzalez J, Johnson S, Ralph ME, Ellis A, Broderick R (2013) Test protocols for advanced inverter interoperability functions—main document. Sandia Technical Report SAND2013-9880Google Scholar
- 34.Gonzalez J, Johnson S, Ralph ME, Ellis A, Broderick R (2013) Test protocols for advanced inverter interoperability functions—appendices. Sandia Technical Report SAND2013-9875Google Scholar
- 35.System Validation Platform Github Repository, https://github.com/sunspec/svp_directories