Research on a new fiber-optic axial pressure sensor of transformer winding based on fiber Bragg grating
- 386 Downloads
Based on the principle of the fiber Bragg grating, a new type of fiber-optic pressure sensor for axial force measurement of transformer winding is designed, which is designed with the structure of bending plate beam, the optimization of the packaging process, and material of the sensor. Through the calibration experiment to calibrate the sensor, the field test results of the Taikai transformer factory show that the sensitivity of the sensor is 0.133 pm/kPa and the repeatability error is 2.7% FS. The data of the fiber-optic pressure sensor in different positions maintain consistent and repeatable, which can meet the requirement of the real-time monitoring of the axial force of transformer winding.
KeywordsTransformer winding pressure sensor fiber Bragg grating (FBG) axial force
This work was partly supported by the Natural Science Fund Plan of Shandong Province (No. 2016ZRC01104) and Natural Science Foundation Doctoral Fund of Shandong Province (No. ZR2016FB03).
- W. D. S. Fonseca, D. D. S. Lima, A. K. F. Lima, N. S. Soeiro, and M. V. A. Nunes, “Analysis of electromagnetic-mechanical stresses on the winding of a transformer under inrush currents conditions,” International Journal of Applied Electromagnetics and Mechanics, 2016, 50(4): 511–512.CrossRefGoogle Scholar
- A. Marinescu, G. Opran, M. Teodorescu, I. Dinu, and L. Tascau, “Fibre optic based clamping force monitoring system for power transformers,” in Proceeding of 13th International Conference on Optimization of Electrical and Electronic Equipment, Brasov, Romania, 2012, pp. 282–283.Google Scholar
- Z. F. Chen, C. H. Zhou, L. Y. Xu, W. Liu, and Z. B. Xu, “On-line monitoring method of transformer winding deformation based on optical fiber stress sensing technology,” Electric Age, 2014, 8: 74–76.Google Scholar
- Q. Z. Wen, J. H. Zhu, G. N. Li, J. B. Huang, and C. Yu, “The experimental study and structural design of fiber grating pressure sensor for pressure sensitivity enhancement,” Journal of Wuhan University, 2012, 58(5): 411–413.Google Scholar
- J. Huang, “Development and application of fiber Bragg grating pressure sensors,” M.S. dissertation, Wuhan University of Technology, Wuhan, China, 2013.Google Scholar
- A. Sun, X. G. Qiao, Z. A. Jia, T. Guo, and C. Y. Chen, “Strain response of a special cantilever-based fibre Bragg grating,” Journal of Optoelectronics Laser, 2004, 15(2): 153–154.Google Scholar
- T. Guo, Q. D. Zhao, L. H. Liu, G. L. Huang, L. F. Xue, G. Y. Li, et al., “Light intensity-referred and temperature-insensitive fiber Bragg grating dynamic pressure sensor,” Acta Optica Sinica, 2007, 27(2): 208–209.Google Scholar
- Y. Wang, T. G. Liu, L. N. Liu, and J. F. Jiang, “Study on fiber Bragg grating sensor encapsulated by the alloyed steel,” Optical Technique, 2006, 32(6): 923–924.Google Scholar
- C. C. Hu, D. S. Zhang, C. Y. Wen, and W. He, “Researches on fiber Bragg grating pressure sensor,” Journal of Wuhan University of Technology, 2007, 29(1): 52–54.Google Scholar
Open Access This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.