Management of a water distribution network by coupling GIS and hydraulic modeling: a case study of Chetouane in Algeria
- 2k Downloads
For more effective management of water distribution network in an arid region, Mapinfo GIS (8.0) software was coupled with a hydraulic model (EPANET 2.0) and applied to a case study region, Chetouane, situated in the north-west of Algeria. The area is characterized not only by water scarcity but also by poor water management practices. The results showed that a combination of GIS and modeling permits network operators to better analyze malfunctions with a resulting more rapid response as well as facilitating in an improved understanding of the work performed on the network. The grouping of GIS and modeling as an operating tool allows managers to diagnosis a network, to study solutions of problems and to predict future situations. The later can assist them in making informed decisions to ensure an acceptable performance level for optimal network operation.
KeywordsWater distribution network GIS Database Modeling EPANET
Geographic information systems (GIS) have become essential tools in the spatial and statistical analysis of water resources for more effective management (Tsihrintzis et al. 1996; Kalivas et al. 2003; Udovyk 2006). Vairavamoorthy et al. (2007) even reported that such systems have been employed for spatial data management and manipulation of spacewalks. Spatial data, also known as geospatial data, is information about a physical object that can be represented by numerical values in a geographic coordinate system. GIS provides a consistent environment for viewing of the display model and the input/output data results. This ability is very useful in the decision making process. In the field of urban hydraulics, for instance, Blindu (2004), Abdelbaki and Touaibia (2011, 2014), and Abdelbaki et al. (2012) demonstrated that the use of GIS allows for a more thorough awareness of a water distribution network; thus making it easier to update a system after a change. Furthermore, for a better management of a water distribution network (WDN) it is also possible to combine in a GIS database information, such as water quantity and quality in a specific territory. It is thus important to collect in the same computer support all the information related to a water system based on geographical location. This precise knowledge of the network will improve efficiency at both the technical and administrative management levels and will enhance the quality of service provided to subscribers (Gandin and Doutre 2007).
According to Tabesh and Delavar (2003), the development of a GIS model combined with the generation of information required for effective water services management is time consuming and expensive. It has become clear that all desired management goals cannot be reached in the application of GIS in water distribution systems without a link to hydraulic simulation models. Additionally, coupling GIS to external models enhances the overall management efficiency of water delivery systems (Bartolin et al. 2001, 2008; Argent 2004; Vairavamoorthy et al. 2007; Panagopoulos et al. 2012; Abdelbaki 2014).
Hydraulic model EPANET software (Rossman 2000) has been recognized as the standard for identifying key parameters. EPANET which first appeared in 1993 is a public domain, water distribution system modeling software package developed by the United States Environmental Protection Agency’s (EPA) Water Supply and Water Resources Division. The model performs extended period simulation of hydraulic and water-quality behavior within pressurized pipe networks and was designed to be a research instrument that advances our understanding of the movement and destiny of drinking water constituents within distribution schemes (Rossman 1999, 2000). Data to be analyzed has to be entered through a graphic interface by means of property dialogs (Bartolín et al. 2008). EPANET is employed in various fields of research, where there is a need for continuous improvement (Ardeshir et al. 2006; Martinez et al. 2007; Worm et al. 2010; Guidolin et al. 2010; Yu et al. 2010; Ramesh et al. 2012; Padilla et al. 2013; Abdelbaki 2014). For example, in Algeria a methodology for implementation of GIS coupled with EPANET for the Chetouane water distribution network (WDN) has been developed to take advantage of a powerful modeling environment.
The aim of this study was to develop a more effective management system for a water distribution network in an arid area by coupling Mapinfo GIS (8.0) software with a hydraulic model (EPANET 2.0) and then applying it to a case study region, Chetouane, situated in the north-west of Algeria. Specifically, network modeling was used to analyze and to comprehend the functioning of the distribution network better in terms of diagnosing problem areas, such as supply discontinuity, leakages and replacement of worn out pipes.
Description of case study area and water distribution network
The water distribution network of Chetouane is interconnected with branched extensions and serves 4642 subscribers (ADE 2012). The network length (main pipes) is 25 km with the pipe diameter varying between 33 and 500 mm (steel and galvanized steel). The water is distributed by gravity using four tanks whose capacities are, respectively, 3000, 1000, 300 and 250 m3. The primary network performance is 51 % and the linear loss index is in the range of 15 m3/day/km (ADE 2012).
Utilization of GIS for diagnosing the Chetouane water distribution network
The different available options in GIS allows for the acquisition of network maps and their associated characteristics (Ho et al. 2010). Each layer or level can be associated with a specific theme along with the associated alphanumeric information. These GIS systems are, therefore, particularly well adapted to the representation of drinking water supply systems (Blindu 2004).
Query results obtained were a form of diagnosis (Blindu 2004). By identifying places where malfunction events could occur, the operator may identify areas of the network with serious issues, and thereafter take decisions to improve the network status.
GIS-EPANET transfer and modeling of the Chetouane water distribution network
Results and discussion
The overall analysis indicated that the Chetouane water distribution network is not functioning ideally. Several actions are required to improve the performance and to reduce the rate of leakage in the network. Updating of the network should take into consideration the operating conditions (i.e., velocity, pressure, soil characteristics). It is important to note that the storage and updating of descriptive and spatial operations data allows the operators and managers to access the history of operating problems of specific parts of the network. Knowing where breaks have occurred, and where renewals have been made, for instance, is very useful for predicting future interventions in the network, and thus for budgeting purposes.
The results showed that the combination of GIS and modeling allows network operators to have a management tool that can analyze malfunctions with a response to any incident that may occur and facilitate understanding of the work performed on the network. Furthermore, the grouping of GIS and modeling as an operating tool allows managers to diagnosis the network, to study the solutions of problems and to predict future situations. The later can assist them in making more informed decisions to ensure an acceptable performance level for optimal network operation.
This study has shown a methodology for improved management of a water distribution network by coupling Mapinfo GIS 8.0 software with hydraulic modeling (EPANET2.0). By applying this methodology to a case study region of Chetouane in Algeria, it revealed which areas of the network are working properly and which areas need to be changed. In addition, the storage and updating of descriptive and spatial operations data allows operators and managers to access the history of operating problems of specific parts of the network. Knowing where fractures have occurred, and where renewals have been made, for instance, is very useful for predicting future interventions in the network, and thus for budgeting purposes.
The authors wish to thank the staff of the Operations Department of the Algerian water-Unit (ADE Tlemcen) for their help and cooperation.
- Abdelbaki C (2014) Modélisation d’un réseau d’AEP et contribution à sa gestion à l’aide d’un SIG-Cas du Groupement Urbain de Tlemcen, Thèse de Doctorat, Université de Tlemcen, pp 208. doi: 10.13140/2.1.4131.9207
- Abdelbaki C, Touaibia B (2011) Modélisation d’un réseau d’alimentation en eau potable et contribution à sa gestion à l’aide d’un SIG—Cas du groupement urbain de Tlemcen, Algérie, Proceeding du 4ème colloque international sur les ressources en eau et le développement durable, 22 et 23 février 2011, Alger, Algérie, pp 583–587Google Scholar
- Abdelbaki C, Benhamouda F, Chikh M (2012) SIG: Outils de gestion des réseaux d’alimentation en eau potable, Cas du réseau de la ville de Birtouta -Alger, Algérie, Editions universitaires européennes, AllemagneGoogle Scholar
- Algérienne Des Eaux ADE (2012) Rapport technique d’exploitation, pp 42Google Scholar
- Ardeshir A, Saraye M, Sabour F, Behzadian K (2006) Leakage management for water distribution system in GIS environment. World environmental and water resource congress, May 21–25, 2006, Omaha, Nebraska, USA, pp. 1–10. World Environmental and Water Resource Congress 2006: Examining the Confluence of Environmental and Water Concerns, pp 1–10. doi: 10.1061/40856(200)27
- Ayral PA, Sauvagnargues-Lesage S (2009) Systèmes d’Information Géographique: outil d’aide à la gestion territoriale. Techniques de l’ingénieur, France H7415:1–14Google Scholar
- Bartolin H, Martinez F, Monterde N (2001) Connecting ArcView 3.2 to EPANET 2. A full environment to manage water distribution systems using models. Water software systems: theory and applications. International Conference on Computing and Control for the Water Industry (CCWI’01). Montfort University, Leicester (UK), 6–9 September 2001, pp 355–368Google Scholar
- Bartolín H, Martínez F, Cortés J (2008) Bringing up to date WDS models by querying. An EPANET-Based GIS Geodatabase, Eighth Annual Water Distribution Systems Analysis Symposium (WDSA), Cincinnati, Ohio, USA, pp 1–17Google Scholar
- Blindu I (2004) Outil d’aide au diagnostic du réseau d’eau potable pour la ville de Chisinau par analyse spatiale et temporelle des dysfonctionnements hydrauliques. Thèse de doctorat, Ecole nationale supérieure des mines de Saint-Etienne, France, pp 304Google Scholar
- Bonnin J (1986) Hydraulique Urbaine Appliquée aux agglomérations de petite et moyenne importance. Edition Eyrolles, ParisGoogle Scholar
- DPAT (2008) Schéma d’aménagement de la commune de Chetouane, Note technique, pp 56Google Scholar
- Dupont A (1979) Hydraulique urbaine, Tome 2. Edition Eyrolles, ParisGoogle Scholar
- Gandin F, Doutre O (2007) Le SIG du SEDIF : un outil performant au service de la gestion de l’eau potable, L’eau, les nuisances. l’industrie 303: 53–56Google Scholar
- Gomella C (1985) Guide de l’alimentation en eau dans les agglomérations urbaines et rurales. Editions Eyrolles, ParisGoogle Scholar
- Guidolin M, Burovskiy P, Kapelan Z, Savić DA (2010) CWS Net: an object-oriented toolkit for water distribution system simulations, water distribution system analysis, WDSA2010, Tucson, AZ, USA, Sept. 12–15. doi: 10.1061/41203(425)2
- Padilla Sifontes V, Davila Quintero J (2013) Multi-agent geosimulation for a water distribution System, Computing Conference (CLEI), XXXIX Latin American, Naiguata: 7–11 Oct. 2013, pp 1–12. doi: 10.1109/CLEI.2013.6670651
- Ramesh H, Santhosh L, Jagadeesh CJ (2012) Simulation of hydraulic parameters in water distribution network using EPANET and GIS. In: International Conference on Ecological Environmental and Biological Sciences (ICEEBS’2012) Jan. 7–8, Dubai, pp 350–353Google Scholar
- Rossman LA (1999) Computer models/EPANET. Water distribution systems handbook. McGraw Hill, New YorkGoogle Scholar
- Rossman L (2000) Epanet 2 user’s manual. Environmental Protection Agency, CincinnatiGoogle Scholar
- Salomons E (2005) DXF2EPA—AutoCad DXF File Conversion Utility for EPANET. http://www.water-simulation.com/wsp/2005/06/03/dxf2epa-autocad-dxf-file-conversion-utility-for-epanet. Accessed 27 March 2013
- Tabesh M, Delavar MR (2003) Application of integrated GIS and hydraulic models for unaccounted for water studies in water distribution systems, Advances in Water Supply Management. In: Proceedings of the CCWI’03 Conference, London, 15–17 September, Edited by Cedo Maksimovic, Fayyaz Ali Memon, and David Butler, Taylor & Francis, Print ISBN: 978-90-5809-608-1, eBook ISBN: 978-0-203-83366-7Google Scholar
- Tatiétsé TT, Rodriguez M (2001) A method to improve population access to drinking water networks in cities of developing countries. J Water Supply Res Technol Aqua 50(1):47–60Google Scholar
- Tena-Chollet F, Sauvagnargues-Lesage S, Thierion V, Ayral PA (2010) Systèmes d’information géographique: mise en œuvre. Techniques de l’ingénieur, France H7416:1–22Google Scholar
- Udovyk O (2006) GIS for intergrated water resourses management. In: Hlavinek P, Kukharchyk T, Marsalek J, Mahrikova (eds) Integrated urban water resources management. Springer, The Netherlands, pp 35–42Google Scholar
- Valiron F (1994) Mémento du gestionnaire de l’alimentation en eau potable et de l’assainissement, Tome 1, 2, 3, Edition Lavoisier, Paris, France, pp 1262Google Scholar
- Yu T, Liya M, Xiaohui L, Yunzhong J (2010) Construction of water supply pipe network based on GIS and EPANET model in Fangcun District of Guangzhou. In: Geoscience and Remote Sensing (IITA-GRS), 28–31 August 2010, Second IITA International Conference on (vol 2, 268-271). IEEE. doi: 10.1109/IITA-GRS.2010.5604123
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.