In this paper, the optimization-simulation approach is proposed to investigate energy saving potential of an air-cooled direct expansion rooftop package air conditioning system by refining the model of the HVAC system components and deriving optimal configuration for evaporator coil subject to technical constraints. In this method the frontal area of the evaporator coil is maintained as constant and the variation of other geometrical parameters on the thermal and economical performance of the system is investigated. An actual air-cooled rooftop package of a real-world commercial building in hot and dry climate conditions is used for experimental data collection. Both inputs and outputs are measured from the field monitoring in two summer weeks. Based on the mathematical models and using collected data, modules incorporating the proposed optimal redesign procedure were embedded in a transient simulation tool. A mixed heuristic- deterministic optimization algorithm was implemented in the transient tool to determine the synthesis and design variables that influence the cost and energy efficiency of each configuration. Available experimental results were compared to predicted results to validate the model. Afterwards, the computer model was used to predict how changes in cooling coil geometry would affect the building thermal comfort, the cost and energy consumption of the system.
This is a preview of subscription content, access via your institution.
Buy single article
Instant access to the full article PDF.
Tax calculation will be finalised during checkout.
ANSI/ASHRAE Standard 140 (2007). Standard Method of Test for the Evaluation of Building Energy Analysis Computer Program. Atlanta, GA, USA: American Society of Heating, Refrigerating and Air-Conditioning.
Afonso CFA (2006). Recent advances in building air conditioning systems. Applied Thermal Engineering, 26: 1961–1971.
Arias J, Lundqvist P (2006). Heat recovery and floating condensing in supermarkets. Energy and Buildings, 38: 73–81.
ARI Standard 540 (2004). Performance rating of positive displacement refrigerant compressors and compressor units. Air Conditioning and Refrigeration Institute, Arlington, VA, USA.
ASHRAE (2004). ASHRAE Standard 55: Thermal Environment Conditions for Human Occupancy. Atlanta, GA, USA: American Society of Heating, Refrigerating and Air-Conditioning.
ASHRAE (2009). ASHRAE Handbook: Fundamentals. Atlanta, GA, USA: American Society of Heating, Refrigerating and Air-Conditioning Engineers.
Barreira EM, Negrao COR, Hermes CJL (2013). Thermoeconomic analysis and optimization of residential split-type air conditioners. Applied Thermal Engineering, 50: 629–636.
Bendaoud A, Ouzzane M, Aidoun Z, Galanis N (2010). A new modeling approach for the study of finned coils with CO2. International Journal of Thermal Sciences, 49: 1702–1711.
Council of Australian Governments (2012). Guide to Best Practice Maintenance and Operation of HVAC Systems for Energy Efficiency. Department of Climate Change and Energy Efficiency, Australia.
Huzayyin AS, Nada SA, Elattar HF (2007). Air-side performance of a wavy-finned-tube direct expansion cooling and dehumidifying air coil. International Journal of Refrigeration, 30: 230–244.
ISO Standard 7730 (1994). Moderate Thermal Environment, Determination of PMV and PPD Indices and Specifications of the Conditions for Thermal Comfort. Geneva: International Organization for Standardization.
Lee TS, Wu WC, Jiang JC (2012). Improved energy performance of air-cooled water chillers with innovative condenser coil configurations—Part II: Experimental validation. International Journal of Refrigeration, 35: 2212–2222.
Minitab (2010). Minitab User’s Guide Release 16. State College, PA, USA: Minitab Inc.
Nassif N (2012). The impact of air filter pressure drop on the performance of typical air-conditioning systems. Building Simulation, 5: 345–350.
Sarntichartsak P, Thepa S (2013). Modeling and experimental study on the performance of an inverter air conditioner using R410A with evaporatively cooled condenser. Applied Thermal Engineering, 51: 597–610.
Sanaye S, Malekmohammadi HR (2004). Thermal and economical optimization of air conditioning units with vapor compression refrigeration system. Applied Thermal Engineering, 24: 1807–1825.
Schmidt TE (1949). Heat transfer calculations for extended surfaces. Refrigeration Engineering, 1949(April): 351–357.
Sekhar SC, Tan LT (2009). Optimization of cooling coil performance during operation stages for improved humidity control. Energy and Building, 41: 229–233.
TRNSYS (2006). TRNSYS Software: A Transient System Simulation Program, version 16. Available: http://sel.me.wisc.edu/trnsys.
Vakiloroaya V (2013). Design optimization of the cooling coil for HVAC energy saving and comfort enhancement. Environmental Progress & Sustainable Energy, 32: 1209–1216.
Vakiloroaya V, Madadnia J, Samali B (2013a). Modeling and performance prediction of an integrated central cooling plant for HVAC energy efficiency improvement. Building Simulation, 6: 127–138.
Vakiloroaya V, Ha QP, Samali B (2013b). Energy-efficient HVAC systems: Simulation-empirical modeling and gradient optimization. Automation in Construction, 31: 176–185.
Wang B, Han L, Shi W, Li X (2012). Modeling method of scroll compressor based on suction gas bypass. Applied Thermal Engineering, 37: 183–189.
Wang CC, Chi KY, Chang CJ (2000). Heat transfer and friction characteristics plain fin-and-tube heat exchangers. Part II: Correlation. International Journal of Heat and Mass Transfer, 43: 2693–2700.
Yik FWH, Burnett J, Prescott I, (2001). Predicting air-conditioning energy consumption of group of buildings using different heat rejection methods. Energy and Buildings, 33: 151–166.
About this article
Cite this article
Vakiloroaya, V., Samali, B., Fakhar, A. et al. Thermo-economic optimization of rooftop unit’s evaporator coil for energy efficiency and thermal comfort. Build. Simul. 7, 345–359 (2014). https://doi.org/10.1007/s12273-013-0151-6
- direct expansion evaporator coil
- design optimization
- energy saving
- thermo-economic analysis