# Performance of tubular aluminum foam heat exchangers in multiple row bundles

- 41 Downloads
- 1 Citations

## Abstract

Two sets of aluminum foam cylinders, 5 and 15 mm thick, are being tested in two-row and three-row bundles for their thermo-hydraulic performance. The bundles are formed using fixed transversal and longitudinal pitch distances and subject to airflow between 0.5 and 5.0 at 0.5 m s^{−1} interval under cross-flow. The effects of foam layer thickness and the number of row under staggered configuration are investigated. Thermo-hydraulic results are benchmarking against those of a conventional finned tube bundle of similar dimensions with pre-determined number of fins and assembled using the same pitch distances.

## Keywords

Metal foams Heat exchangers Condensers Tube bank Tube bundle Cooling towers Cross-flow Geothermal## List of symbols

*A*Area (\(\hbox {m}^2\))

- \(\bar{c}_{\mathrm{p}}\)
Specific heat capacity at constant pressure (J kg

^{−1}K^{−1})- \(d_{\mathrm{f}}\)
Strut diameter (m)

- \(d_{\mathrm{i}}\)
Core tube internal diameter (m)

- \(d_{{\mathrm{o}}}\)
Core tube external diameter (m)

- \(D_{\mathrm{i}}\)
Foam or fin annulus internal diameter \(= d_{{\mathrm{o}}}\) (m)

- \(D_{\mathrm{o}}\)
Foam or fin annulus external diameter (m)

*f*Friction factor (–)

*H*Dimensional height (m)

*h*Convective heat transfer coefficient (W \(\hbox {m}^{-2}\) K

^{−1}])*Kp*Pressure loss coefficient (–)

*k*Thermal conductivity (W m

^{−1}K^{−1})*L*Dimensional length (m)

- \(\dot{m}\)
Mass flow rate (kg s

^{−1})*Nu*Nusselt number (–)

*P*Pressure (Pa)

- \(\dot{Q}\)
Heat transfer rate (W)

*R*Thermal resistance (K W

^{−1})*Re*Reynolds number (–)

- \(S_{\mathrm{L}}\)
Longitudinal pitch distance (m)

- \(S_{\mathrm{T}}\)
Transversal pitch distance (m)

- \(t_{\mathrm{f}}\)
Fin thickness (m)

- \(t_{\mathrm{p}}\)
Fin pitch (m)

*T*Temperature (K or \(^\circ\)C)

- \(\vec {u}\)
Air velocity (m s

^{−1})*U*Universal heat transfer coefficient (W \(\hbox {m}^{-2}\) K

^{−1})*W*Dimensional width (m)

- \(\hat{X}_{\mathrm{L}}\)
Ratio of longitudinal pitch to core diameter \(= S_{\mathrm{L}}/d_{\mathrm{o}}\) (–)

- \(\hat{X}_{\mathrm{T}}\)
Ratio of transversal pitch to core diameter \(= S_{\mathrm{T}}/d_{\mathrm{o}}\)(–)

## Abbreviations

- FS
Full scale

- HTC
Convective heat transfer coefficient (W \(\hbox {m}^{-2}\) K

^{−1})- LMTD
Log mean temperature difference (K or \(^\circ\)C)

- NTU
Number of transfer unit (–)

- PID
Proportional–integral–derivative feedback control

- PPI
Pores per inch [technically in\(^{-1}\), treated as (–)]

- RTD
Resistance temperature detector

- TCR
Thermal contact resistance (K/W)

## Greek symbols

- \(\Delta\)
Differential of

- \(\epsilon\)
Heat exchanger efficiency (–)

- \(\eta\)
Surface efficiency of aluminum foam (–)

- \(\mu\)
Dynamic viscosity (Pa s)

- \(\rho\)
Mass density (kg \(\hbox {m}^{-3}\))

- \(\phi\)
Porosity (–)

- \(\Omega ^*\)
Efficiency function of foam

## Common Subscripts

*a*Of the air

*c*Of the colder fluid taking up heat

*h*Of the hotter fluid losing heat

*i*Of inside surface

- max
The largest value

- min
The smallest value

*o*Of outside surface

*s*Of a surface

*t*Overall, total

- \(\infty\)
Of the bulk air free flow stream

## Notes

### Acknowledgements

The principal author is grateful to QGECE for its financial support to this study. Both authors also express their gratitude to the following individuals: Professor Thomas Rösgen for setting up the PIV facility, giving initial tutorials, and providing supervision on related works in his lab at the Institut Für Fluiddynamik, ETH-Zurich; Mostafa Odabaee for his help in sourcing test specimens; Dr Morteza Khashehchi, who helped process PIV data for velocity check; Joy Wang and Peter Bleakley for helping with data logging instrument; Douglas Malcolm for helping with wind tunnel operation and air velocity PID control program; and lastly Berto Di Pasquale for general fabrication of in-house parts and accessories.

## References

- 1.Chumpia A, Hooman K. Performance evaluation of single tubular aluminum foam heat exchangers. J. Appl. Therm. Eng. 2014;66:266–73.CrossRefGoogle Scholar
- 2.Chumpia A, Hooman K. Performance evaluation of tubular aluminum foam heat exchangers in single row arrays. J. Appl. Therm. Eng. 2015;83:121–30.CrossRefGoogle Scholar
- 3.Ashby MF. Metal foams : a design guide. Boston: Butter-worth-Heinemann; 2000.Google Scholar
- 4.T’Joen C, De Jaeger P, Huisseune H, Van Herzeele S, Vorst N, De Paepe M. Thermo-hydraulic study of a single row heat exchanger consisting of metal foam covered round tubes. Int. J. Heat Mass Transf. 2010;53:3262–74.CrossRefGoogle Scholar
- 5.Incropera FP, DeWitt DP, Bergman TL, Lavine AS. Fundamentals of Heat and Mass Transfer. 6th ed. Hoboken: Wiley; 2006.Google Scholar
- 6.Boyd B, Hooman K. Air-cooled micro-porous heat exchangers for thermal management of fuel cells. Int. Commun. Heat Mass Transf. 2012;39:363–7.CrossRefGoogle Scholar
- 7.Weclas M, Cypris J. Characterization of the Distribution-nozzle Operation for Mixture Homogenization by A Late-diesel-injection Strategy. In Proceedings of the Institute of Mechanical Engineers, Part D: J. Automobile Engineering. 2012; 226:529–546.Google Scholar
- 8.Ejlali A, Ejlali A, Hooman K, Gurgenci H. Application of high porosity metal foams as air cooled heat exchangers to high heat load removal systems. Int. Commun. Heat Mass Transf. 2009;36:674–9.CrossRefGoogle Scholar
- 9.Boomsma K, Poulikakos D, Zwick F. Metal foams as compact high performance heat exchangers. J. Mech. Mater. 2003;35:116–1176.CrossRefGoogle Scholar
- 10.Hsieh WH, Wu JY, Shih WH, Chiu WC. Experimental investigation of heat-transfer characteristics of aluminum-foam heat sinks. Int. J. Heat Mass Transf. 2004;47:5149–57.CrossRefGoogle Scholar
- 11.Kim SY, Paek JW, Kang BH. Flow and heat transfer correlations for Porous fin in a plate-fin heat exchanger. J. Heat Transf. Trans. ASME. 2000;122:572–8.CrossRefGoogle Scholar
- 12.Mahjoob S, Vafai K. A synthesis of fluid and thermal transport models for metal foam heat exchangers. Int. J. Heat Mass Transf. 2008;51:3701–11.CrossRefGoogle Scholar
- 13.Tadrist L, Miscevic M, Rahli O, Topin F. About the use of fibrous materials in compact heat exchangers. J. Exper. Therm. Fluid Sci. 2004;28:193–9.CrossRefGoogle Scholar
- 14.Bhattacharya A, Mahajan RL. Finned metal foam heat sinks for electronics cooling in forced convection. J. Electron. Packag. 2002;124:155–63.CrossRefGoogle Scholar
- 15.Moffat RJ, Eaton JK, Onstad A. A method for determining the heat transfer properties of foam-fins. J. Heat Transf. Trans. ASME. 2009;131:011603-1–7.CrossRefGoogle Scholar
- 16.De Jaeger P, T’Joen C, Huisseune H, Ameel B, De Schampheleirea S, De Paepe M. Assessing the influence of four bonding methods on the thermal contact resistance of open-cell aluminum foam. Int. J. Heat Mass Transf. 2012;55:6200–10.CrossRefGoogle Scholar
- 17.Kays WM, London AL. Compact heat exchangers. 3rd ed. Malabar: Krieger Publishing; 1984 (Reprinted with corrections, 1998).Google Scholar
- 18.Sparrow EM, Samie F. Heat transfer and pressure drop results for one- and two-row arrays of finned tubes. Int. J. Heat Mass Transf. 1985;28:2247–59.CrossRefGoogle Scholar
- 19.Chumpia A. Improving the performance of air-cooled condensers by using metal foams, PhD Thesis, School of Mechanical and Mining Engineering, The University of Queensland. 2016.Google Scholar
- 20.Hooman K, Haji-Sheikh A, Nield DA. Thermally developing Brinkman-Brinkman forced convection in rectangular ducts with isothermal walls. Int. J. Heat Mass Transf. 2007;50:3521–33.CrossRefGoogle Scholar
- 21.Tamayol A, Hooman K. Thermal assessment of forced convection through metal foam heat exchangers. J. Heat Transf. 2011;133:111801.CrossRefGoogle Scholar
- 22.Fiedler T, White N, Dahari M, Hooman K. On the electrical and thermal contact resistance of metal foam. Int. J. Heat Mass Transf. 2014;72:565–71.CrossRefGoogle Scholar
- 23.Hooman K, Dukhan N. A theoretical model with experimental verification to predict hydrodynamics of foams. Transp. Porous Media. 2013;100:393–406.CrossRefGoogle Scholar