Corrosion of the inside surface of penstocks
- 19 Downloads
The corrosion rate of steel in flowing water of the Mingechaur reservoir is within 0.47–1.08 mm/yr, decreasing rapidly with exposure [3, 4].
Considerable initial values of the cathodic current density, equal to 1–1.5 mA/dm2, are needed for cathodic protection of steel in the same flowing water; however, they decrease rapidly both as a result of the formation of cathode deposits and as a result of the formation of natural films and deposits on the metal.
Anodic dissolution of metal in a freshwater flow occurs at the same rates as in nonflowing water.
KeywordsEnergy Source Flowing Water Corrosion Rate Power Generation Power Engineer
Unable to display preview. Download preview PDF.
- 1.A. G. Khanlarova et al., “Mechanism of corrosion of steel in fresh waters”, in: Protection of Hydraulic Structures in River Water from Corrosion [in Russian], Énergiya, Moscow (1968).Google Scholar
- 2.M. S. Trifel' et al., “Characteristcs of a device and monitoring of cathodic protection of hydraulic turbines from cavitation erosion”, Gidrotekh. Stroit., No. 8 (1969).Google Scholar
- 3.Yu. Z. Shikhaliev et al., “Investigation of the electrochemical behavior of steel St. 3 under operating conditions of underwater metal elements of hydraulic structures of the Mingechaur hydroelectric station, “Uch. Zap. Azineftekhima, IX Ser., No. 5, Baku (1971).Google Scholar
- 4.A. A. Spirin and Yu. Z. Shikhaliev, “Protection of the steelwork of structures of the Mingechaur hydroelectric station from corrosion,” Gidrotekh. Stroit., No. 8 (1974).Google Scholar