Selecting and optimal sizing of hybridized energy storage systems for tidal energy integration into power grid
- 1.2k Downloads
- 5 Citations
Abstract
The high penetration of renewable energy systems with fluctuating power generation into the electric grids affects considerably the electric power quality and supply reliability. Therefore, energy storage resources are used to deal with the challenges imposed by power variability and demand-supply balance. The main focus of this paper is to investigate the appropriate storage technologies and the capacity needed for a successful tidal power integration. Therefore, a simplified sizing method, integrating an energy management strategy, is proposed. This method allows the selection of the adequate storage technologies and determines the required least-cost storage capacity by considering their technological limits associated with different power dynamics. The optimal solutions given by the multi-objective evolutionary algorithm are presented and analyzed.
Keywords
Tidal energy Energy storage system Optimal sizing Selection1 Introduction
The integration of renewable energies into the electrical grid is one of the most challenging tasks. In fact, the quality of the power delivered to the grid becomes very crucial when the penetration level of renewable energies is very high [1, 2]. Therefore, the use of energy storage systems (ESSs) can alleviate potential problems. ESS can provide a variety of application solutions along the entire electricity system value chain, from generation support to transmission and distribution support to end-customer uses [3]. Consequently, different ESS applications have been defined and analyzed according to their uses and value of benefits.
For renewable applications, it is common to use ESS for energy time-shift and capacity firming. The energy time shift increases the value of energy and so profits are increased. Indeed, most renewable energy resources produce a significant portion of electric energy at off-peak periods which has a low financial value. As a result, ESS can be charged and used when demand is high and supply is tight [4, 5]. By contrast, capacity firming allows the use of intermittent electric supply as a nearly constant source. Such use may reduce power-related charges and/or offset the need for equipment. Likewise, for effective renewable integration, some requirements are identified and classified in two categories. The first one is the short duration applications including the reduction of power volatility and the improvement of power quality. The second one concerns the long duration applications embracing the reduction of output variability, the transmission congestion relief, the back-up for unexpected power generation shortfalls and the minimization of load violations.
Satisfying all the earlier announced requirements makes the sizing task very complicated and depending on many parameters (e.g., resource variability, load fluctuation, technologies limitations, life time, costs, etc.). In this context, too many papers in literature deal with the optimal sizing of energy storage systems especially for renewable energy applications [6, 7, 8, 9, 10]. The ESS sizing problem was mainly studied either in the time domain [11, 12, 13] or in the frequency domain [14, 15, 16]. Moreover, it can be noticed that the common practice was the use of one or two preselected ESS and then try to find its optimal sizes according to some defined objectives [17, 18, 19].
In contrast, this paper proposes a new approach allowing the selection of the adequate storage technology and determines the required least-cost storage capacity by considering its technological limits associated to different power dynamics. Therefore, a simplified sizing method, integrating an energy management strategy, is proposed. To highlight its effectiveness, the proposed strategy is applied to a tidal energy system, but it can be employed with any other renewable energy such as photovoltaic (PV), wind turbine, etc. This paper is organized as follows. First, Section 2 recalls the particularities of the tidal energy and describes the power fluctuation dynamics. Subsequently, Section 3 announces the adopted energy management strategy. The approach to the selection of the appropriate ESS is defined in Section 4. Section 5 presents the sizing optimization algorithm. Lastly, Section 6 concludes the paper and provides directions for future research.
2 Power fluctuation dynamics
In order to model the whole system, multi-physics approach was adopted including the resource, the marine turbine, and the ESS. This simulator can evaluate marine current turbine performances and dynamic loads over different operating conditions. Throughout the paper, we will use \(\mathcal{P}=(T_0,T_P)\), with \(0\le T_0<T_P\), to denote the period of analysis.
From (3), \(P_{ss}\) is defined positive during the charging period and negative during the discharge period. In order to highlight the different dynamics of the storage power flow, a fast fourier transform (FFT) is established. Figure 2 shows three scales of dynamics which obviously need different types of storage system.
3 Energy management strategy based on a frequency approach
Technical and economical characteristics of electrical energy storage technologies
Technologies | Energy density (J/L) | Power density (W/L) | Power capital cost ($/kW) | Energy capital cost ($/kWh) | Charge/discharge efficiency (%) |
---|---|---|---|---|---|
PHS | \(2 10^3{-}5.5 10^3\) | \(0.5{-}1.5\) | \(2500{-}4300\) | \(5{-}100\) | 87 |
CAES | \(2 10^3{-}7 10^3\) | \(3{-}6\) | \(400{-}1000\) | \(2{-}120\) | \(70{-}79\) |
Flywheel | \(3.6 10^6{-}18 10^6\) | \(20{-}80\) | \(250{-}350\) | \(1000{-}5000\) | \(90{-}93\) |
Lead{-}acid | \(36 10^3{-} 1440 10^3\) | \(50{-}80\) | \(300{-}600\) | \(200{-}400\) | 85 |
Li{-}ion | \(5.4 10^6{-} 36 10^6\) | \(200{-}500\) | \(1200{-}4000\) | \(600{-}2500\) | 85 |
NaS | \(500 10^3{-}650 10^3\) | \(150{-}300\) | \(1000{-}3000\) | \(300{-}500\) | 85 |
NiCd | \(290 10^3{-}2 10^6\) | \(15{-}150\) | \(500{-}1500\) | \(800{-}1500\) | 85 |
VRFB | \(2 10^3{-}7 10^3\) | \(16{-}33\) | \(600{-}1500\) | \(150{-}1000\) | \(75{-}82\) |
ZnBr | \(3.6 10^3{-}90 10^3\) | \(30{-}60\) | \(700{-}2500\) | \(150{-}1000\) | \(60{-}70\) |
Capacitor | \(360 10^6+\) | \(2{-}10\) | \(200{-}400\) | \(500{-}1000\) | \(75{-}90\) |
Double-layer capacitor | \(360 10^6+\) | \(10{-}30\) | \(100{-}300\) | \(300{-}2000\) | \(95{-}98\) |
SMES | \(3.6 10^6{-}14 10^6\) | \(0.2{-}6.1\) | \(200{-}300\) | \(1000{-}10000\) | 95 |
Hydrogen fuel cell | \(2 10^6{-}3.6 10^6\) | \(500{-}3000\) | \(300{-}1500\) | \(2{-}15\) | 59 |
4 Selection of ESSs
Storage system performance characteristics for any power applications can be described in terms of two parameters, i.e., specific power and specific energy. Figure 4 shows different types of ESSs in the energy-power plane called “Ragone chart” and includes information about the suitable application time period for each element [26].
As it can be noticed, batteries are more suitable for applications with long term variations on the scale of minutes to several hours, while superconducting magnetic energy storage systems and ultra-capacitors are more adapted for applications on the time scale of several seconds.
5 Sizing optimization
5.1 Problem formulation
In this study, the sizing variables considered are the power grid \(P_{grid}\) and the two cut-off frequencies \(f_1\in \mathcal{F}_1\) and \(f_2\in \mathcal{F}_2\) shown in Fig. 10 where \(\mathcal{F}_1\) and \(\mathcal{F}_2\) denote the sets of all admissible frequencies.
It should be noted that the optimization problem stated by (17) is complex and in our knowledge it can not be solved explicitly. Besides, the number of possibility, depending on desired sampling accuracy and the technology types, can become very large. Hence, one must seek for a suitable strategy that solve the problem by respecting a balance between the accuracy and the computation time.
5.2 Strategy for solving problem
Algorithm 1 NSGA-II |
---|
/* It is assumed that technical and economical characteristics of electrical energy storage technologies are predefined*/ |
1: Get V_{tide} |
2: Calculate P_{MCT} /* Use (1)*/ |
3: For i:=1 To N_individuals |
Generate (P _{grid} ^{ i} , f _{1} ^{ i} , f _{2} ^{ i} ) |
EndFor |
4: Check_Constraint(1) /*The constraints are defined by (20) */ |
5: Calculate \(f_{ESS_{l}}^{i}\!,f_{ESS_{m}}^{i}\!,f_{ESS_{h}}^{i}\,\) /*Use (4), (6) and (10) */ |
6: Check_Constraint(2) /*The constraint is given in (21) */ |
7: Calculate \(OF_{E},OF_{\mathrm{\Delta} P},OF_{C}\, /*{\text Use}\) (17) \(*\,/\) |
8: P_{1}= Crossover(P) /*Use a predefined crossover function [30]*/ |
9: P_{2}= Mutate(P) /*Use a predefined mutate function [30]*/ |
10: P= New Generation(P,P_{1},P_{2}) /*Evaluate, group and sort (P,P_{1},P_{2}) by dominance and crowding and select N individuals by elitism [30] */ |
11: If j ≤ N_iterations Then Goto 4 |
Else Return(P) |
EndIf |
5.3 Results and discussion
Numerical values used for analysis and simulation
Constant | Value |
---|---|
\(C_p\) | 0.4 |
\(P_{MCT}\) | 1500 kW |
N_individuals | 50 |
N_iterations | 100 |
\(\rho\) | 1000 \(\mathrm {kg/m}^3\) |
\(f_1^{\mathrm {min}}\) | \(5 \times 10^{-6}\) Hz |
\(f_2^{\mathrm {min}}\) | \(5 \times 10^{-5}\) Hz |
\(f_1^{\mathrm {max}}\) | \(5 \times 10^{-5}\) Hz |
\(f_2^{\mathrm {max}}\) | \(5 \times 10^{-2}\) Hz |
\(P_{grid}^{\mathrm {min}}\) | 100 kW |
\(P_{grid}^{\mathrm {max}}\) | 1 MW |
\((P_{grid}^{real})_{\mathrm {avg}}\) | 210 kW |
The obtained results highlights the fact that only the medium and high dynamic must be considered for the ESS sizing problem in tidal energy applications. Indeed, the astronomic nature of the tidal energy resource makes it predictable for low dynamics. Therefore by filtering the power generated by the daily moon cycle, swell effect and turbulence, it is easier to integrate successfully the produced energy in the grid.
6 Conclusion
In this paper, an optimal sizing strategy for hybridized energy storage systems were presented. This approach is based on a simplified frequency energy management method. Optimal solutions are obtained using a multi-objective genetic algorithm. However, the procedure is highly time consuming, especially when using annual tidal speed data with one second as sampling time. Therefore, some simplifications were used to reduce computational time by excluding the estimation of the life span and considering a limited database of storage systems with average values of power and energy density related to average values of power capital and energy capital costs of the ESS. Nevertheless, the obtained results are very interesting and give a good idea about the optimal solutions to be considered according to their cost and performances.
References
- [1]Eltigani D, Masri S (2015) Challenges of integrating renewable energy sources to smart grids: a review. Renew Sustain Energy Rev 52:770–770CrossRefGoogle Scholar
- [2]Cifor A, Denholm P, Ela E et al (2015) The policy and institutional challenges of grid integration of renewable energy in the Western United States. Utilities Policy 33:34–41CrossRefGoogle Scholar
- [3]Hemmati R, Saboori H (2016) Emergence of hybrid energy storage systems in renewable energy and transport applications: a review. Renew Sustain Energy Rev 65:11–23CrossRefGoogle Scholar
- [4]Parra D, Gillott M, Norman SA et al (2015) Optimum community energy storage system for PV energy time-shift. Appl Energy 137:576–587CrossRefGoogle Scholar
- [5]Friis F, Christensen TH (2016) The challenge of time shifting energy demand practices: insights from Denmark. Energy Res Soc Sci 19(Supplement C):124–133CrossRefGoogle Scholar
- [6]Parra D, Norman SA, Walker GS et al (2017) Optimum community energy storage for renewable energy and demand load management. Appl Energy 200:358–369CrossRefGoogle Scholar
- [7]Hemmati R, Saboori H (2017) Stochastic optimal battery storage sizing and scheduling in home energy management systems equipped with solar photovoltaic panels. Energy Build 152:290–300CrossRefGoogle Scholar
- [8]Olaszi BD, Ladanyi J (2017) Comparison of different discharge strategies of grid-connected residential PV systems with energy storage in perspective of optimal battery energy storage system sizing. Renew Sustain Energy Rev 75:710–718CrossRefGoogle Scholar
- [9]Schneider M, Biel K, Pfaller S et al (2015) Optimal sizing of electrical energy storage systems using inventory models. Energy Procedia 73:48–58Google Scholar
- [10]Schneider M, Biel K, Pfaller S et al (2016) Using inventory models for sizing energy storage systems: an interdisciplinary approach. J Energy Storage 8:339–348CrossRefGoogle Scholar
- [11]Cardenas R, Pena R, Asher G et al (2001) Control strategies for enhanced power smoothing in wind energy systems using a flywheel driven by a vector-controlled induction machine. IEEE Trans Ind Electron 48(3):625–635CrossRefGoogle Scholar
- [12]Brekken TKA, Yokochi A, Jouanne AV et al (2011) Optimal energy storage sizing and control for wind power applications. IEEE Trans Sustain Energy 2(1):69–77Google Scholar
- [13]Cimuca GO, Saudemont C, Robyns B et al (2006) Control and performance evaluation of a flywheel energy-storage system associated to a variable-speed wind generator. IEEE Trans Ind Electron 53(4):1074–1085CrossRefGoogle Scholar
- [14]Xiao J, Bai L, Li F et al (2014) Sizing of energy storage and diesel generators in an isolated microgrid using discrete fourier transform (DFT). IEEE Trans Sustain Energy 5(3):907–916CrossRefGoogle Scholar
- [15]Makarov YV, Du P, Kintner-Meyer MCW et al (2012) Sizing energy storage to accommodate high penetration of variable energy resources. IEEE Trans Sustain Energy 3(1):34–40CrossRefGoogle Scholar
- [16]Liu Y, Du W, Xiao L et al (2016) A method for sizing energy storage system to increase wind penetration as limited by grid frequency deviations. IEEE Trans Power Syst 31(1):729–737CrossRefGoogle Scholar
- [17]Tani A, Camara MB, Dakyo B (2012) Energy management in the decentralized generation systems based on renewable energy. In: Proceedings of international conference on renewable energy research and applications, Nagasaki, Japan, 11–14 November 2012, 6 ppCrossRefGoogle Scholar
- [18]Belouda M, Jaafar A, Sareni B et al (2016) Design methodologies for sizing a battery bank devoted to a stand-alone and electronically passive wind turbine system. Renew Sustain Energy Rev 60:144–154CrossRefGoogle Scholar
- [19]Sarrias-Mena R, Fernndez-Ramrez LM, GarcaVzquez CA et al (2014) Improving grid integration of wind turbines by using secondary batteries. Renew Sustain Energy Rev 34:194–207CrossRefGoogle Scholar
- [20]Myers L, Bahaj A (2005) Simulated electrical power potential harnessed by marine current turbine arrays in the alderney race. Renew Energy 30(11):1713–1731CrossRefGoogle Scholar
- [21]Elghali SEB, Balme R, Saux KL et al (2007) A simulation model for the evaluation of the electrical power potential harnessed by a marine current turbine. IEEE J Ocean Eng 32(4):786–797CrossRefGoogle Scholar
- [22]Zhou Z, Scuiller F, Charpentier JF et al (2013) Power smoothing control in a grid-connected marine current turbine system for compensating swell effect. IEEE Trans Sustain Energy 4(3):816–826CrossRefGoogle Scholar
- [23]Zhou Z, Scuiller F, Charpentier JF et al (2012) Grid-connected marine current generation system power smoothing control using supercapacitors. In: Proceedings of 38th annual conference on IEEE industrial electronics society, Montreal, Canada, 25–28 October 2012, 6 ppGoogle Scholar
- [24]Jaafar A, Akli CR, Sareni B et al (2009) Sizing and energy management of a hybrid locomotive based on flywheel and accumulators. IEEE Trans Veh Technol 58(8):3947–3958CrossRefGoogle Scholar
- [25]Akli CR, Roboam X, Sareni B et al (2007) Energy management and sizing of a hybrid locomotive. In: Proceedings of 2007 European conference on power electronics and applications, Aalborg, Denmark, 2–5 September 2007, 10 ppGoogle Scholar
- [26]Christen T, Carlen MW (2000) Theory of ragone plots. J Power Sources 91(2):210–216CrossRefGoogle Scholar
- [27]Akli CR (2008) Conception systémique d’une locomotive hybride autonome: application à la locomotive hybride de démonstration et d’investigations en énergétique LhyDIE développée par la SNCF. Dissertation, ENSEEIHTGoogle Scholar
- [28]Luo X, Wang J, Dooner M et al (2015) Overview of current development in electrical energy storage technologies and the application potential in power system operation. Appl Energy 137:511–536CrossRefGoogle Scholar
- [29]Elghali SEB, Benbouzid MEH, Charpentier J (2010) Modelling and control of a marine current turbine-driven doubly fed induction generator. IET Renew Power Gener 4:1–11CrossRefGoogle Scholar
- [30]Deb K, Pratap A, Agarwal S et al (2002) A fast and elitist multiobjective genetic algorithm: Nsga-ii. IEEE Trans Evol Comput 6(2):182–197CrossRefGoogle Scholar
Copyright information
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.