Pilot field test of intentional islanding in distribution network
- 184 Downloads
Power supply interruptions to final customers are mainly caused by failures in the distribution system. The increase of distributed generation connected to the distribution system offers a possibility to reduce the duration and frequency of such interruptions as local generation can be used to feed local demand. This paper presents results of an actual implementation of an islanding operation for a rural feeder in Rio de Janeiro State, Brazil. A MW-scale electrical islanding, so-called minigrid, is formed when the utility circuit-breaker is opened, leaving part of the utility customers supplied solely by a 5.55 MVA synchronous machine based small hydro power plant. Field measurements were compared to simulation results obtained from a digital simulator developed to evaluate active distribution networks.
KeywordsDistributed generation Islanded operation Small hydro power plant
The authors would like to acknowledge the personnel of Light S.E.S.A. that were involved in the field tests. This work was financially supported by CAPES, CNPq and FAPERJ.
- 1.Fan, N., Izraelevitz, Pan, F., Pardalos, P. M., Wang, J.: A mixed Integer Programming Approach for Optimal Power Grid Intentional Islanding. Energy Systems, vol. 3, no. 1, pp. 77–93 (2012)Google Scholar
- 2.Chowdhury, A., Koval, D.: Power Distribution System Reliability: Practical Methods and Applications, Series on Power Engineering. Wiley, New York (2005)Google Scholar
- 3.Pilo, F., Celli, G., Mocci, S.: Improvement of Reliability in Active Networks with Intentional Islanding. IEEE International Conference on Electric Utility Deregulation, Restructuring and Power Technologies, vol. 2, pp. 474–479 (2004)Google Scholar
- 4.Mahat, P., Chen, Z., Bak-Jensen, B.: Review on islanding operation of distribution system with distributed generation. In: Proceedings of the 2011 IEEE PES General Meeting, Detroit (2011)Google Scholar
- 5.Hatziargyriou, N., Asano, H., Iravani, R., Marnay, C.: Microgrids. IEEE Power and Energy Magazine, vol. 5, no. 4, pp. 78–94 (2007)Google Scholar
- 8.Chowdhury, S., Chowdhury, S. P., Crossley, P.: Microgrids and active distribution networks. IET Renewable Energy Series 6, The Institution of Engineering and Technology, IET, London (2009)Google Scholar
- 11.ANEEL. Distribution Grid Codes. National Agency of Electrical Energy. http://www.aneel.org.br. Accessed 22 Sept 2013 (in Portuguese)
- 13.IEEE Working Group Report: IEEE screening guide for planned steady-state switching operations to minimize harmful effects on steam turbine-generators. IEEE Transactions on Power Apparatus and Systems, vol. PAS-99, no. 4, pp. 1519–1521 (1980)Google Scholar
- 15.Kundur, P.: Power System Stability and Control, 1st edn. McGraw-Hill Inc., New York (1994)Google Scholar
- 17.Taranto, G.N., Marinho, J.M., Falcão, D.M., Assis, T.M.L., Escalante, S.L., Rodriguez, J.I.R., Pontes, C.E.V.: Active distribution networks simulator with sigle/three-phase modeling. http://www.coep.ufrj.br/~tarang/Simulight/SEPOPE_2012.pdf. Accessed 20 Sept 2013 (in Portuguese)