Ventilation efficiency assessment according to the variation of opening position in L-shaped rooms
- 6 Downloads
Air change efficiency evaluates the ability of a system to achieve the change of the air contained in a confined interior space. It is conditioned by the geometry of the room, the different openings and the properties of the air among others. Rectangular rooms do not offer impediments when mixing the interior air; however, in rooms with non-regular shapes, stagnation phenomenon can occur in the corners. This paper proposes the study of the air change efficiency in an L-shaped room in which the position of the inlet and outlet openings is sequentially variated. This study is based on the execution of successive numerical simulations, validated by experimental studies. The results show that there are differences on the ventilation efficiency of up to 13.49% between the most dissimilar cases, which occur when one of the openings is located in a corner. If the other opening is placed nearby, the results are very poor; whereas if it is placed at the opposite corner, the efficiency value improves due to the circulation of the air through the room. When these openings are placed near the centre of the room, the efficiencies that are obtained are more similar and this analysis is less relevant.
Keywordsnatural ventilation indoor air quality (IAQ) ventilation efficiency computational fluid dynamics (CFD) air movement building geometry
Unable to display preview. Download preview PDF.
This study was funded by TCUE: Transferencia de Conocimiento Universidad-Empresa (No. TCUE.6-LANZADERA 067/157541).
- ANSYS (2017). ANSYS FLUENT 18.1 User’s Guide.Google Scholar
- Camino Olea MS, Feijó-Muñoz J, Basterra Otero A, Carbayo Baz FJ, García Barrero R (2005). Diseño y construcción de un laboratorio para el análisis de la ventilación. In: Proceedings of I Jornadas Investig. En Construcción. (in Spanish)Google Scholar
- European Committee for Standardization (2004). EN 13141-1. Ventilation for buildings-Performance testing of components/products for residential ventilation-Part 1: Externally and internally mounted air transfer devices. European Committee for Standardization.Google Scholar
- Eurostat (2015). Final energy consumption by sector and fuel. European Environment Agency.Google Scholar
- Li X, Wang X, Li X, Li Y (1999). Investigation on the relationship between flow pattern and air age. In: Proceedings of the 6th International IBPSA Building Simulation Conference, Kyoto, Japan.Google Scholar
- Liddament MW (1996). A Guide to Energy Efficient Ventilation, Coventry: Air Infiltration and Ventilation Centre.Google Scholar
- Ministry of Development (2017). Documento Básico HS - Salubridad. Ministerio de Fomento - Gobierno de España. (in Spanish)Google Scholar
- Mundt E, Martin Mathisen H, Nielsen P.V, Moser A (2004). Guidebook No.02: Ventilation Effectiveness. Federation of European Heating and Air-conditioning Associations (REHVA), Helsinki, Finland.Google Scholar
- Nielsen PV, Allard F, Awbi HB, Davidson L, Schälin A (2007). Guidebook No.10: Computational Fluid Dynamics in Ventilation Design. Federation of European Heating and Air-conditioning Associations (REHVA), Helsinki, Finland.Google Scholar
- SECH Project-SpaHousec (2011). Analyses of the energy consumption of the household sector in Spain. Final Report. El Instituto para la Diversificación y Ahorro de la Energía.Google Scholar
- Dijkstra HA (2015). Ventilation efficiency in an L-shaped room. Master Thesis, Eindhoven University of Technology, Netherlands.Google Scholar
- Von Kármán T (1930). Mechanische Ähnlichkeit und Turbulenz. Nachrichten von Der Gesellschaft Der Wissenschaften Zu Göttingen, Fachgruppe 1 (Mathematik), 5: 58–76.Google Scholar