Hospital ventilation simulation for the study of potential exposure to contaminants
- First Online:
- 395 Downloads
Airflow and ventilation are particularly important in healthcare rooms for controlling thermo-hygrometric conditions, providing anaesthetic gas removal, diluting airborne bacterial contamination and minimizing bacteria transfer airborne. An actual hospitalization room was the investigate case study. Transient simulations with computational fluid dynamics (CFD), based on the finite element method (FEM) were performed to investigate the efficiency of the existing heating, ventilation and air-conditioning (HVAC) plant with a variable air volume (VAV) primary air system. Solid modelling of the room, taking into account thermo-physical properties of building materials, architectural features (e.g., window and wall orientation) and furnishing (e.g., beds, tables and lamps) arrangement of the room, inlet turbulence high induction air diffuser, the return air diffusers and two patients lying on two parallel beds was carried out. Multiphysics modelling was used: a thermo-fluidynamic model (convection-conduction and incompressible Navier-Stokes) was combined with a convection-diffusion model. Three 3D models were elaborated considering different conditions/events of the patients (i.e., the first was considered coughing and/or the second breathing). A particle tracing and diffusion model, connected to cough events, was developed to simulate the dispersal of bacteria-carrying droplets in the isolation room equipped with the existing ventilation system. An analysis of the region of droplet fallout and the dilution time of bacteria diffusion of coughed gas in the isolation room was performed. The analysis of transient simulation results concerning particle path and distance, and then particle tracing combined with their concentration, provided evidence of the formation of zones that should be checked by microclimatic and contaminant control. The present study highlights the fact that the CFD-FEM application is useful for understanding the efficiency, adequacy and reliability of the ventilation system, but also provides important suggestions for controlling air quality, patients’ comfort and energy consumption in a hospital.
KeywordsCFD transient simulation ventilation HVAC VAV plant virus diffusion isolation rooms
Unable to display preview. Download preview PDF.
- ASHRAE (1995). ASHRAE Handbook: HVAC Applications, SI Edition. Atlanta, GA: The American Society of Heating, Refrigerating and Air-Conditioning Engineers.Google Scholar
- Batchelor GK (2000). An Introduction to Fluid Dynamics. Cambridge, UK: Cambridge University Press.Google Scholar
- Chen Q, Srebric J (2001). Simplified diffuser boundary conditions for numerical room airflow model: Final report of RP-1009. Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning Engineers.Google Scholar
- COMSOL (2009). www.comsol.com.
- Diekmann O, Heesterbeek JAP (2000). Mathematical Epidemiology of Infectious Diseases. Chichester, UK: John Wiley & Sons.Google Scholar
- Galson E, Guisbond J (1995). Hospital sepsis control and TB transmission. ASHRAE Journal. 37(5):48–52.Google Scholar
- ISO 7730 (2005). Moderate thermal environments—Determination of the PMV and PPD indices and specification of the conditions for thermal comfort.Google Scholar
- Jiang Y, Su M, Chen Q (2003). Using large eddy simulation to study airflows in and around buildings. ASHRAE Transactions, 109(2): 517–526.Google Scholar
- Kim S H, Augenbroe G (2009). Ventilation operation in hospital isolation room: a multi-criterion assessment considering organizational behaviour. In: Proceedings of the 11th IBSPSA Conference (pp. 1322–1329), Glasgow, Scotland.Google Scholar
- Li Y, Leung GM, Tang JW, Yang X, Chao C, Lin JH, Lu JW, Nielsen PV, Niu JL, Qian H, Sleigh AC, Su HJ, Sundell J, Wong TW, Yuen PL (2007). Role of ventilation in airborne transmission of infectious agents in the built environment—A multidisciplinary systematic review. Indoor Air, 17: 2–18.CrossRefGoogle Scholar
- Marianne T, Perini JM, Lafitte JJ, Houdret N, Pruvot FR, Lamblin G, Slayter HS, Roussel P (1987). Peptides of human bronchial mucus glycoproteins. Size determination by electron microscopy and by biosynthetic experiments. Biochemical Journal, 248: 189–195.Google Scholar
- Memarzadeh F, Manning AP (2002). Comparison of operating room ventilation systems in the protection of the surgical site. ASHRAE Transactions, 108(2): 3–15.Google Scholar
- Phillips DA, Sinclair RJ, Schuyler GD (2004). Isolation room ventilation. Design case studies. In: Proceedings of IAQ Conference, ASHRAE.Google Scholar
- Rygielski L, Uden D (2007). Creating comfort. Nine considerations for selecting the right hospital HVAC system. Health Facilities Management, 20(1): 19–23.Google Scholar
- Solidworks (2009). www.solidworks.com.
- Soper M (2008). Pandemic ready. HVAC systems for worst-case scenarios. Health Facilities Management, 21(10): 49–52.Google Scholar
- UNI 10339 (1995). Air-conditioning systems for thermal comfort in buildings. General, classification and requirements. Offer, order and supply specifications. Italian Standard.Google Scholar
- UNI EN 13779 (2005). Ventilation for non-residential buildings—Performance requirements for ventilation and room-conditioning systems. Italian Standard.Google Scholar
- Verdier O (2004). Benchmark of Femlab, Fluent and Ansys. Lund University.Google Scholar
- Zhao B, Yang C, Chen C, Yang CFX, Sun L, Gong W, Yu L (2009). How many airborne particles emitted from a nurse will reach the breathing zone/body surface of the patient in ISO Class-5 single-bed hospital protective environments? A numerical analysis. Aerosol Science and Technology, 43: 990–1005.CrossRefGoogle Scholar