Review of automated fault detection and diagnostic tools in air handling units
- 876 Downloads
Studies have indicated that 20–30 % HVAC system energy savings are achievable by recommissioning air handling units (AHU) to rectify faulty operation. Studies have also demonstrated that on-going commissioning of building systems for optimum efficiency can yield savings of an average of over 20 % of total energy cost. Automated fault detection and diagnosis (AFDD) is a process concerned with automating the detection of faults and their causes in physical systems. AFDD can be used to assist the commissioning process at multiple stages. This article presents a review of the research work that has been carried out on the use of AFDD tools in improving the efficiency of AHUs. This updates and expands upon the most recent literature review in this area, published in 2005. The article offers a comparative analysis of the FDD techniques currently in use and offers an opinion as to which show most potential for widespread adoption as part of the on-going commissioning process. It then details the issues which have impeded the adoption of existing AFDD tools for AHUs to date before concluding with an appraisal of current and recommended areas for future research to overcome the barriers to the widespread adoption of AFDD tools in AHUs.
KeywordsHeating Ventilation and air conditioning (HVAC) Fault detection and diagnosis (FDD) Energy efficient buildings Commissioning Air handling unit (AHU)
This research was funded by Enterprise Ireland. The authors would like to thank the Innovation for Irelands Energy Efficiency (i2e2) Technology Centre.
- “BACnet Website.” (2011). Accessed December 6. http://www.bacnet.org/
- CEN. “IS EN 16001.” (2010). NSAI. http://www.cen.eu/cen/News/PressReleases/Pages/EN16001.aspx.
- “DABO.” http://adms-tech.com/ongoing-commissioning software. Accessed 27 May 2013.
- Choinière, D., Corsi, M. (2003). “A BEMS Assisted Commissioning Tool to Improve the Energy Performance of HVAC Systems.” In ICEBO. http://www.commissioning-hvac.org/files/doc/Choiniere__ICEBO.pdf
- EVO. “IPMVP.” http://www.evo-world.org/index.php?option=com_content&view=article&id=272&Itemid=504&lang=en/. Accessed 14 September 2011.
- Facility Dynamics. “PACRAT.” http://www.facilitydynamics.com/pacrat.html/. Accessed 13 September 2011
- House, J. M., Vaezi-Nejad, H., Whitcomb, J. M. (2001). “An Expert Rule Set for Fault Detection in Air Handling Units.” Ashrae Transactions Part 1 (107). http://www.nist.gov/manuscript-publication-search.cfm?pub_id=860823
- “HVAC Special Working Group – Spin III, 2009.” (2011). Accessed September 13. http://www.seai.ie/Your_Business/Large_Energy_Users/Special_Initiatives/Special_Working_Groups/HVAC_SWG_Spin3/
- “HVAC SWG - Spin I, 2007.” (2011). Accessed September 13. http://www.seai.ie/Your_Business/Large_Energy_Users/Special_Initiatives/Special_Working_Groups/HVAC_SWG_07/
- International Energy Agency. (1996). “Real-time HEVAC simulation”. 25Google Scholar
- International Energy Agency. (2002). “Computer-aided evaluation of HVAC system performance” 34Google Scholar
- International Energy Agency. (2006). “Commissioning of Building HVAC Systems for Improved Energy Performance”. 40.Google Scholar
- International Energy Agency. (2010). “Cost-effective commissioning of existing and low energy buildings” 47.Google Scholar
- ISO - International Organisation for Standardisation, and ISO - International Organisation for Standardisation. (2011). “ISO - International Organisation for Standardisation”. Text. Accessed September 13. http://www.iso.org/iso/catalogue_detail?csnumber=51297
- “ISO 13381–1:2004 - Condition Monitoring and Diagnostics of Machines -- Prognostics -- Part 1: General Guidelines.” 2011. Accessed December 6. http://www.iso.org/iso/iso_catalogue/catalogue_tc/catalogue_detail.htm?csnumber=21841
- Le, T. H., Knabe, G., & Henze, G. P. (2005). Fault Detection and Diagnosis for Control Strategies in Air Handling Units. Montreal: In IBPSA.Google Scholar
- Lee, S. Uk., Painter, F. L., Claridge, D. E. (2007) “Whole Building Commercial HVAC System Simulation for Use in Energy Consumption Fault Detection.” Ashrae Transactions 113 (Part 2).Google Scholar
- “LonMark International.” 2011. Accessed December 6. http://www.lonmark.org/
- Schein, J. (2006). “Results from Field Testing of Embedded Air Handling Unit and Variable Air Volume Box Fault Detection Tools”. NIST. http://fire.nist.gov/bfrlpubs/build06/art033.html
- West, S. R., Yinh Guo, X., Wang, R., & Wall, J. (2011). Automated Fault Detection and Diagnosis of HVAC Subsystems Using Statistical Machine Learning. Sydney: IBPSA.Google Scholar