Heating energy performance and part load ratio characteristics of boiler staging in an office building
- 2 Downloads
Commercial buildings account for significant portions of the total building energy in South Korea and thus a variety of research on the boiler operation related to heating energy in office buildings has been carried out thus far. However, most of the researches have been conducted on the boiler itself, i.e., the part load ratio characteristics and the corresponding gas energy consumption patterns are not analyzed in the existing studies. In this study, the part load ratio and the operating characteristics of gas boiler have been analyzed within an office building equipped with the conventional variable air volume system. In addition, the gas consumption among different boiler staging schemes has been comparatively analyzed. As a result, significant portions of total operating hours, heating load and energy consumption has been found to be in a part load ratio range of 0 through 40% and thus energy consumption is significantly affected by boiler efficiency at low part load conditions. This suggests that boiler operation at the part load is an important factor in commercial buildings. In addition, utilizing sequential boiler staging scheme can save a gas usage of about 7%. For annual heating energy saving, applying the sequential control boiler with a 3:7 proportion staging is considered to be the optimal control algorithm for maximum efficiency of boilers.
KeywordsEnergyPlus boiler part load ratio gas consumption office building boiler staging
Unable to display preview. Download preview PDF.
This work was supported by the Korea Institute of Energy Technology Evaluation and Planning (KETEP) and the Ministry of Trade, Industry & Energy (MOTIE) of the Republic of Korea (No. 20163030111350), and the Human Resources Development of the Korea Institute of Energy Technology Evaluation and Planning (KETEP) grant funded by the Korea government Ministry of Trade, Industry & Energy (No. 20184030201900).
- 1.Kim T H, Jung Y S, Jung H G. A trend analysis of greenhouses gas reduction technique development for building sector in Korea. In: Proceedings of the fall conference of the Architectural Institute of Korea, Busan, Republic of Korea, 2016, 716–717Google Scholar
- 2.Pak J H. World energy market insight weekly. Korea Energy Economics Institute. 2016–5–16, http://188.8.131.52:8089/search/search_homepage/search.jspGoogle Scholar
- 3.Lee S J. Post 2020 types of greenhouse gas reduction contribution. Korea Energy Economics Institute, 2016Google Scholar
- 4.Seo J H. Energy saving in boiler. Journal of Korean Association of Air Conditioning Refrigerating and Sanitary Engineers, 2009, 26: 51–59Google Scholar
- 11.Yu B H, Seo B M, Moon J E, et al. Analysis of part load ratio characteristics and gas energy consumption of a hot water boiler in a residential building under Korean climatic conditions. Journal of The Society of Air-conditioning and Refrigerating Engineers of Korea, 2015, 27: 455–462CrossRefGoogle Scholar
- 14.Yoon Y B, Kim D S, Lee K H. Detailed heat balance analysis of the thermal load variations depending on the blind location and glazing type. Energy and Buildings, 75: 84–95Google Scholar
- 15.The US Department of Energy. EnergyPlus Engineering Reference. The Reference to EnergyPlus Calculations. 2014, http://www. energyplus.govGoogle Scholar
- 16.Lee D Y, Seo B M, Kwon H J, et al. Heating performance and partial load ratio characteristics of boiler staging in office building. In: Proceedings of the Summer Conference of The Society of Airconditioning and Refrigerating Engineers of Korea, Pyungchang, Republic of Korea, 2017, 321–324Google Scholar
- 17.American Society of Heating. Refrigerating and Air-conditioning Engineers. ASHRAE Standard 90.1. Energy Standard for Buildings Except Low-Rise Residential Buildings, 2004Google Scholar
- 18.Sohn J Y, Kim S H, Ahn B W, et al. Multiple units control of boiler and refrigerator HVAC system. Journal of the Society of Airconditioning and Refrigerating Engineers of Korea. 1992, http://www.auric.or.kr/User/Rdoc/DocRdoc.aspx?BrsDataBaseName = RDOC&PrimaryKey = 57473&DBNM = RDCR#.WbenzuQUmUkGoogle Scholar