# Uncertainty Analysis of Thermal Comfort Parameters

- 450 Downloads
- 2 Citations

## Abstract

International Standard ISO 7730:2005 defines thermal comfort as that condition of mind that expresses the degree of satisfaction with the thermal environment. Although this definition is inevitably subjective, the Standard gives formulae for two thermal comfort indices, predicted mean vote (*PMV*) and predicted percentage dissatisfied (*PPD*). The *PMV* formula is based on principles of heat balance and experimental data collected in a controlled climate chamber under steady-state conditions. The *PPD* formula depends only on *PMV*. Although these formulae are widely recognized and adopted, little has been done to establish measurement uncertainties associated with their use, bearing in mind that the formulae depend on measured values and tabulated values given to limited numerical accuracy. Knowledge of these uncertainties are invaluable when values provided by the formulae are used in making decisions in various health and civil engineering situations. This paper examines these formulae, giving a general mechanism for evaluating the uncertainties associated with values of the quantities on which the formulae depend. Further, consideration is given to the propagation of these uncertainties through the formulae to provide uncertainties associated with the values obtained for the indices. Current international guidance on uncertainty evaluation is utilized.

## Keywords

Thermal comfort Uncertainty evaluation GUM GUM supplement 1 Monte Carlo method## Notes

### Acknowledgments

The National Measurement Office, an Executive Agency of the UK Department for Business, Innovation and Skills, supported the work of the NPL authors through the Mathematics and Modelling for Metrology programme. Financial support of FCT (Portuguese Foundation for Science and Technology) in the context of Project Ref. Pest OE/MAT/UI0219/2014, and Project VALIMED, under the Madeira Regional Programme “Intervir+”, is grateful acknowledged.

## References

- 1.http://www.labeee.ufsc.br/antigo/arquivos/publicacoes/Thermal_Booklet.pdf. Innova AirTech Instruments A/S
- 2.F. Nicol, M. Humphreys, S. Roaf,
*Adaptive Thermal Comfort. Principles and Practice*(Routledge Taylor & Francis Group, London, 2012)Google Scholar - 3.ISO. ISO 7730:2005 Ergonomics of the Thermal Environment—Analytical Determination and Interpretation of the Thermal Comfort Using Calculation of the PMV and PPD Indices and Local Thermal Comfort Criteria (International Organization for Standardization, Geneva, Switzerland)Google Scholar
- 4.BIPM, Iec, IFCC, Ilac, ISO, Iupac, IUPAP, OIML. Evaluation of Measurement Data— Guide to the Expression of Uncertainty in Measurement. Joint Committee for Guides in Metrology, JCGM 100:2008. http://www.bipm.org/utils/common/documents/jcgm/JCGM_100_2008_E.pdf
- 5.BIPM, Iec, IFCC, Ilac, ISO, Iupac, IUPAP, OIML. Evaluation of Measurement Data—Supplement 1 to the “Guide to the Expression of Uncertainty in Measurement”—Propagation of Distributions Using a Monte Carlo Method. Joint Committee for Guides in Metrology, JCGM 101:2008. http://www.bipm.org/utils/common/documents/jcgm/JCGM_101_2008_E.pdf
- 6.M.G. Kendall, A. Stuart,
*The Advanced Theory of Statistics, Volume 1: Distribution Theory*(Charles Griffin, London, 1963)Google Scholar - 7.M.G. Cox, P.M. Harris, SS fM Best Practice Guide No. 6, Uncertainty evaluation. Tech. Rep. MS 6, National Physical Laboratory, Teddington, UK (2010). http://www.npl.co.uk/publications/software-suuport-for-metrology-best-practice-guide-no.-6.-uncertainty-evaluation
- 8.T.J. Dekker, in
*Constructive Aspects of the Fundamental Theorem of Algebra*, ed. by B. Dejon, P. Henrici (Wiley Interscience, London, 1969)Google Scholar - 9.P.E. Gill, W. Murray, M.H. Wright,
*Practical Optimization*(Academic Press, London, 1981)Google Scholar - 10.J.R. Rice,
*Mathematical Statistics and Data Analysis*, 2nd edn. (Duxbury Press, Belmont, 1995)Google Scholar - 11.M. Correia Guedes, L. Matias, C. Pina Santos, Renew. Energy
**34**(11), 2357 (2009)Google Scholar - 12.J. Nicol, M. Humphreys, Energy Build.
**34**(6), 563 (2002). doi: 10.1016/S0378-7788(02)00006-3. http://www.sciencedirect.com/science/article/pii/S0378778802000063. Special Issue on Thermal Comfort Standards - 13.M.G. Cox, A.B. Forbes, P.M. Harris, J.A. Sousa, in
*IMEKO World Congress*, September 18–22, 2006, Rio de Janeiro (206) (2006)Google Scholar - 14.ISO. ISO 9920:2007 Ergonomics of the Thermal Environment—Estimation of Thermal Insulation and Water Vapour Resistance of a Clothing Ensemble (International Organization for Standardization, Geneva, Switzerland)Google Scholar
- 15.J.N. Lyness, C.B. Moler, SIAM J. Numer. Anal.
**4**, 202 (1967)MathSciNetCrossRefADSMATHGoogle Scholar - 16.A.H. Al-Mohy, N.J. Higham, Numer. Algorithm
**53**, 133 (2010)MathSciNetCrossRefADSGoogle Scholar - 17.R. Boudjemaa, M.G. Cox, A.B. Forbes, P.M. Harris, in
*Advanced Mathematical and Computational Tools in Metrology VI*, ed. by P. Ciarlini, M.G. Cox, F. Pavese, G.B. Rossi (World Scientific, Singapore, 2004), pp. 170–179Google Scholar - 18.M. Cox, A. Forbes, P. Harris, C. Matthews,
*Uncertainty Quantification in Scientific Computing*(Springer, Berlin, 2012), pp. 180–194CrossRefGoogle Scholar