Suppression of Weakly-Damped Torsional Oscillations in Autonomous Power Systems
- 9 Downloads
Variants are considered for suppression of weakly-damped vibration effects caused by the first critical frequency of torsional oscillations of a gas-turbine unit in the autonomous electric power system of an oil and gas field. It is shown that torsional oscillations can be suppressed with the aid both of a reactive power source installed at the field power system, consisting of a controlled shunt reactor (CSR) and a static capacitor battery, and of an auxiliary active RLC filter, when using in both cases auxiliary control loops of torsional deviation as well as its first and second derivatives. A methodology has been developed for simultaneous coordination of the settings of any regulation system based on a numerical optimization, which permits selecting the characteristics of control loops of the source of reactive power and active RLC filter that are optimal from the point of view of suppressing torsional oscillations.
Keywordsautonomous power system gas turbine unit synchronous generator induction motor automatic voltage regulator controlled shunt reactor steady-state stability transient stability variable frequency drive
Unable to display preview. Download preview PDF.
- 1.A. N. Belyaev, “Decreasing torsional moments in a gas-turbine system of generator drives of an autonomous power plant,” Izv. RAN. Énerget., No. 2, 124 – 132 (2010).Google Scholar
- 2.A. N. Belyaev and S. T. Andrus, “Controlled reactive power sources for ensuring stability of load sections of oil and gas extraction complexes,” Naucho-Tekhn. Vedom. SPbGTU, No. 1, 92 – 97 (2008).Google Scholar
- 3.A. N. Belyaev, A. A. Smirnov, and S. V. Smolovik, “Damping components of torsional oscillations in autonomous power systems with prevailing motive load due to ‘strong’ regulation of longitudinal capacitor compensation devices,” Izv. Vuzov. Probl. Énerget., No. 7 – 8, 71 – 82 (2011).Google Scholar
- 4.A. N. Belyaev, A. A. Smirnov, and S. V. Smolovik, “Study of the starting modes of induction motors in order to optimize the operation of oil pumping stations with hot gas reciprocating units with commensurate capacity,” Naucho-Tekhn. Vedom. SPbGTU, No. 1(117): Science and education, 80 – 88 (2011).Google Scholar
- 5.G. V. Rubisov and V. E. Sigaev, “Calculation method for analyzing torsional oscillations of a turbine-set shaft train,” Élektrotekhnika, No. 1, 27 – 31 (1986).Google Scholar
- 6.I. D. Urusov, “Modeling oscillatory processes in a turbine-set shaft train,” Élektrichestvo, No. 5, 8 – 11 (1983).Google Scholar
- 7.IEEE Subsynchronous ResonanceWorking Group, “Terms, definitions, and symbols for subsynchronous oscillations,” IEEE Trans. Power Apparat. Syst., PAS-104, No. 6, 1326 – 1334 (1985).Google Scholar
- 8.IEEE Recommended Practice for Excitation System Models for Power System Stability Studies: IEEE Std 3.421.5 (2005).Google Scholar
- 9.I. A. Gruzdev, V. A. Maslennikov, and S. M. Ustinov, “Development of methods and software for analysis of steady-state stability and damping properties of large power systems,” in: Methods and Software for Calculations of the Oscillatory Stability of Power Systems (Feasibility Study) [in Russian], 66 – 88, St. Petersburg (1992).Google Scholar