Cost–benefit analysis of retrofit of high-intensity discharge factory lighting with energy-saving alternatives
Purchase on Springer.com
$39.95 / €34.95 / £29.95*
Rent the article at a discountRent now
* Final gross prices may vary according to local VAT.
Due to increased concern about overall energy costs and the appearance of efficient and inexpensive lighting system alternatives, factories and plants with high-intensity discharge (HID) lighting are forced to consider retrofit with more modern, energy-efficient lighting. The decision is complicated from an economic perspective, and there is a lack of information readily available on the topic. This study provides an analysis of the replacement by retrofit of common probe-start metal halide and high-pressure sodium industrial lighting systems. Retrofit options considered include the more recent pulse-start metal halide lamps and a range of T5 high output and T8 fluorescent lamp configurations. Recent data on lighting system pricing, labor and energy costs, and time required for tasks are reported. The results generated include savings, payback period, and net present value for many retrofit options, as well as the change in energy consumption, carbon footprint, and lumen output for each retrofit. Effects of varying rate of return and daily duration of operation are considered. Based on change in lumen output, payback period, net present value, and comparison of lighting quality, one or two options are recommended from the overall retrofit options considered. A fluorescent retrofit is recommended for each of the HID initial scenarios considered. The payback period is no more than 3 years in any recommended case. The focus of this study is on the potential energy and cost savings, and some proposed solutions may, or may not, be acceptable due to lack of illuminance uniformity.
- Charles, J., & Lounsbury, F. (1915). Engineering economics. New York: McGraw-Hill.
- Cheung, S. L., Lam, T., Li, D., & Wong, S. L. (2009). An analysis of energy-efficient light fittings and lighting controls. Applied Energy, 87, 558–567.
- Chiang, J. H. (2010). Rsmeans electrical cost data 2010. Kingston, MA: Reed Construction Data.
- Chletsis, A., Pilavachi, P., & Nikolaidis, Y. (2009). Economic evaluation of energy saving measures in a common type of Greek building. Applied Energy, 86(12), 2550–2559. doi:10.1016/j.apenergy.2009.04.029. CrossRef
- Clinton, M. B. (2008). A fundamental study on current industrial lighting systems and analyses of retrofit options. MS thesis, The University of Alabama.
- Eley, C., Tolen, T. M., Benya, J. R., Rubinstein, F. & Verderber, R. (1993). Advanced lighting guidelines: 1993. Prepared for the U.S. Department of Energy, California Energy Commission, and Electric Power Research Institute: San Francisco, CA.
- Energy Information Administration (EIA), (2004). Electricity retail price fact sheet. Retrieved from http://www.eia.gov/cneaf/electricity/page/fact_sheets/retailprice.html
- Energy Information Administration (EIA). (2011, May). U.S. states: Alabama data. Retrieved from http://www.eia.gov/state/state-energy-profiles-data.cfm?sid=AL
- Hong, E., Conroy, L. A., & Scholand, M. J. (2005, September 30). U.S. lighting market characterization, volume II: Energy efficient lighting technology options. Retrieved from http://apps1.eere.energy.gov/buildings/publications/pdfs/ssl/ee_lighting_vol2.pdf
- Lam, J., & Li, D. (2002). An investigation of daylighting performance and energy saving in a daylit corridor. Energy and Buildings, 35, 365–373.
- National Electrical Manufacturers Association (NEMA). (2002). American national standard for lamp ballasts—definitions for fluorescent lamps and ballasts. Englewood, CO: Information Handling Services/Global Engineering Documents.
- National Electrical Manufacturers Association (NEMA), The Association of Electrical and Medical Imaging Equipment Manufacturers (2006). T5 and T5HO fluorescent lamps, high-bay: fluorescent vs. metal. Retrieved from www.lightingtaxdeduction.org
- NLPIP at Rensselaer Polytechnic Institute. (2011). Lighting answers. Retrieved from http://www.lrc.rpi.edu/programs/nlpip/lightingAnswers/lat5/pc1.asp
- Tyler, M. (2009). National electrical estimator 2010. Carlsbad, CA: Craftsman Book.
- US Department of Energy (DOE), Office of Energy Efficiency and Renewable Energy. (2004). Energy efficiency program for commercial and industrial equipment (EE-DET-03-001). Retrieved from http://www1.eere.energy.gov/buildings/appliance_standards/commercial/pdfs/hid_energy_savings_report.pdf
- US EPA, Clean Markets Division. (2007). egrid2010 version 1.1 year 2007 summary tables. Retrieved from http://www.epa.gov/cleanenergy/documents/egridzips/eGRID2010V1_1_year07_SummaryTables.pdf
- Cost–benefit analysis of retrofit of high-intensity discharge factory lighting with energy-saving alternatives
Volume 6, Issue 2 , pp 255-269
- Cover Date
- Print ISSN
- Online ISSN
- Springer Netherlands
- Additional Links
- Industrial lighting
- Lighting retrofit
- Metal halide
- Industrial lighting efficiency
- Author Affiliations
- 1. Alabama Industrial Assessment Center, The University of Alabama, 1530 W. Tremont St, Allentown, PA, 18102, USA
- 2. Alabama Industrial Assessment Center, The University of Alabama, 290 Hardaway Hall, Box 870276, Tuscaloosa, AL, 35487-0276, USA