A study on the evaluations of emission factors and uncertainty ranges for methane and nitrous oxide from combined-cycle power plant in Korea
- First Online:
- Cite this article as:
- Lee, S., Kim, J., Lee, J. et al. Environ Sci Pollut Res (2013) 20: 461. doi:10.1007/s11356-012-1144-1
- 575 Downloads
In this research, in order to develop technology/country-specific emission factors of methane (CH4) and nitrous oxide (N2O), a total of 585 samples from eight gas-fired turbine combined cycle (GTCC) power plants were measured and analyzed. The research found that the emission factor for CH4 stood at “0.82 kg/TJ”, which was an 18 % lower than the emission factor for liquefied natural gas (LNG) GTCC “1 kg/TJ” presented by Intergovernmental Panel on Climate Change (IPCC). The result was 8 % up when compared with the emission factor of Japan which stands at “0.75 kg/TJ”. The emission factor for N2O was “0.65 kg/TJ”, which is significantly lower than “3 kg/TJ” of the emission factor for LNG GTCC presented by IPCC, but over six times higher than the default N2O emission factor of LNG. The evaluation of uncertainty was conducted based on the estimated non-CO2 emission factors, and the ranges of uncertainty for CH4 and N2O were between −12.96 and +13.89 %, and −11.43 and +12.86 %, respectively, which is significantly lower than uncertainties presented by IPCC. These differences proved that non-CO2 emissions can change depending on combustion technologies; therefore, it is vital to establish country/technology-specific emission factors.
KeywordsGreenhouse gasMethaneNitrous oxideEmission factorNon-CO2Power plant
In 2009, Korea announced greenhouse gas mitigation commitment to release 30 % less greenhouse gas than the “Business As Usual” level by 2020 (The Ministry of Environment 2010). It also enacted the “Low Carbon Green Growth Act” in 2010, setting legal grounds for regulation of greenhouse gas emissions to achieve the reduction target. And through the enforcement ordinance of the law, it implemented “GHG Target Management” in April 2010, a system that sets and manages greenhouse gas reduction and energy saving targets in large-scale work sites. In August 2010, 460 companies were designated by the government under these circumstances, so that they fall under government control. As of 2007, the companies released 380 million tons of CO2, which accounts for 60 % of the total greenhouse gas emissions in the country. In addition, it established the guidelines for the GHG Target Management in March 2011 (The Ministry of Environment 2011).
Although there is no globally regulated measurable, reportable and verifiable (MRV) system, Annex Ι countries set a rigorous MRV system at the national level (KIIEP 2009). Also, at the 15th Conference of the Parties, the Copenhagen Accord agreed that Non-Annex Ι countries should be required to establish their own MRV system and submit a country report every 2 years (UNFCCC 2009). Thus, Non-Annex Ι countries do not necessarily have to build the same kind of MRV system on the level of Annex Ι countries, but without an MRV system at the international level, they are highly likely not to be recognized in terms of greenhouse gas emission performance among other countries. In that regard, it is meaningful that Korea established a greenhouse gas MRV system.
At this juncture, Korea is in urgent need to secure well-documented data for drawing up a greenhouse gas inventory. Greenhouse gas emissions are characterized by different kinds of emissions, fuel, types of boilers, antipollution facilities, load factors, and other inherent factors. Non-CO2, in particular, is affected by combustion conditions, operational conditions, technological factors, and several other unknown factors (IPCC 2006; WRI/WBCSD 2005). Therefore, the Intergovernmental Panel on Climate Change (IPCC) recommends that each country put a priority on country- or technology-specific emission factors over default emission factors provided by the IPCC in calculating the amount of greenhouse gas emissions (IPCC 2006; Quick and Glick 2000). Despite this, Korea uses the default emission factors provided by that IPCC since it lacks its own research findings. As of 2006, greenhouse gas emissions by the energy sector has taken up 84 % of the total greenhouse gas emissions, 30 % (about 35 % of the total energy sector) of which have gone to the power generation sector. Thus, the country is expected to be enormously affected if greenhouse gas reduction obligation is imposed (Young-sung et al. 2006). In addition, according to long-term emission prospects, greenhouse gas emissions by the power generation sector are expected to reach 35 % of the total greenhouse gas emissions by 2020. In Korea’s case, a standard and system to classify power generation methods, fuel, combined cycle power generation, cogeneration, etc. should first be established, and greenhouse gas emission factors calculated based on that system.
In this regard, this paper analyzed liquefied natural gas (LNG) gas used in combined cycle power plants in Korea, calculating CH4 and N2O emission factors by measuring non-CO2 greenhouse gasses.
We researched gas-fired combined cycle power plants in Korea using LNG as an energy source among energy industry, accounting for about 24 % of power generation capacity in Korea.
For CO2, emissions can be fairly estimated based on the amount of fuels combusted and the averaged carbon content of fuel because it mainly depend upon the carbon content of the fuel. However, emissions of non-CO2 are influenced by numerous additional factors such as combustion technology and operating conditions.
The combined cycle power plants investigated in this study (2007. 1. 1.–12. 31.)
Power plants (unit)
Generation capacity (kW)
Gross generation (MWh)
Average load (kW)
Peak load (kW)
Exhaust gas analysis method
The concentrations of non-CO2 in exhaust gasses were analyzed by taking samples of exhaust gasses using a Tedlar bag, then analyzing them by ingredient in the laboratory. The quantitative concentration of non-CO2 was measured with gas chromatography (Model CP-3800, Varian, USA). Flame ionization detector (FID) and electrochemical detectors (ECD) were used as a detector; FID for analyzing CH4 and ECD for N2O. We used 1 and 3 m long Porapack QX 80/100 mesh column (stainless steel, external diameter of 3.175 mm, produced by Restek). The temperature of the injector, oven, and detector on the FID was set at 120, 70, and 250 °C, respectively. Additionally, the temperature of the injector, oven, and detector on the ECD was set at 120, 70, and 320 °C, respectively. Ultrapure nitrogen (99.9999 %) was used as carrier gas. When injecting the sample, we used 10-, 6-, and 4-port gas-switching valves to eliminate oxygen and moisture.
In order to carry out quantitative analysis of CH4 and N2O, we drew up calibration curves of each ingredient in advance and used them in calculating concentrations. The CH4 calibration curve was drawn up by measuring five samples with different concentrations within the range of 0.25–5.0 μmol/mol. The N2O calibration curve was drawn up by measuring five samples of different concentrations within the range of 0.5–10.0 μmol/mol. As a result, the R2 value of CH4 and N2O was 0.9994 and 0.9992, respectively, showing high correlation.
Moisture measurement method
Moisture extracting equipment (M-5, Astek Korea) and an electronic scale (Ohaus Adventurer, USA) was used to measure the amount of moisture in the exhaust gas. The temperature of the sample extracting equipment was maintained at 120 °C, while heat rays were quipped in the sample extracting pipe as the moisture in the exhaust gas condensed inside. In order to measure amount of moisture, we filled a cylindrical absorption bottle with anhydrous calcium chloride (Duksan, Korea) and connected it to a sample extracting pipe designed to collect greenhouse gasses. The amount of gas collected was measured to two decimal places (EPA method 4) with an integrating flow meter attached to the moisture extracting equipment. After collecting the sample, we closed the bottle with a stopper and measured the weight. Then, we calculated the moisture amount in the exhaust gas by applying the weight difference of the bottle before and after collecting the sample, flux collected, and gas temperature.
Quality control of analyzing equipment (QA/AC)
Repeatability test of concentration analysis using CH4 and N2O standard gas
MDL values of GC/FID for CH4 and GC/ECD for N2O in this study
Calculation method of emission factor of non-CO2 emissions
Result and discussion
Non-CO2 emission characteristics
Non-CO2 concentration from stacks in the combined cycle power plants
Average of 90 samples
Average of 105 samples
Average of 30 samples
Average of 45 samples
Average of 45 samples
Average of 30 samples
Average of 120 samples
Average of 120 samples
The average CH4 concentration was 1.42–2.33 and 0.27–0.55 ppm for N2O. This is because each power plant has different operational conditions; the amount of fuel consumed per the amount of electricity generated and the emission flux of exhaust gas. For this paper, we researched the operational conditions, the amount of fuel consumed, and the emission flux at each time when samples were taken to calculate the non-CO2 emission factor of combined cycle power plants in Korea.
Results of non-CO2 emission factor calculations
Non-CO2 emission factors of combined cycle power plant in this study
Emission factor (kg/TJ)
Average of 8 facilities
2006 IPCC G/La
2006 IPCC G/Lb
Gas turbine (including GTCC)/>5 MW
Gas turbine (including GTCC)/<5 MW
Gas turbine (including GTCC)
Average of 12 facilities
The N2O emission factor of this study is 0.65 kg/TJ. This value is far lower than the technology-specific N2O emission factor of “combined cycle power plant using LNG as energy source”, as suggested by IPCC. However, the value is more than six times higher than the N2O basic emission factor of the first fuel-based (tier 1 method of calculating emission amount) LNG suggested by IPCC. The difference indicated that non-CO2 emissions change overwhelmingly by combustion technology, which is grounds for establishing country-specific or technology-specific emission factors. Japan researched 12 power plants to calculate the N2O emission factor of its GTCC power plants and uses 0.54 kg/TJ, the average value, as a country-specific emission factor. The value is 1/6 of the IPCC emission factor (combined cycle) and about 20 % lower than that of this study. In Finland’s case, the N2O emission factor of all GTCC power plants was 1 kg/TJ, which is 1/3 of the IPCC emission factor (combined cycle) and about 54 % higher than that of this study.
Analyzing the measurement uncertainty of the non-CO2 emission factor
Uncertainty range of non-CO2 emission factors estimated in this study (unit: percentage)
Combined cycle power plant
Oder of magnitude
−75 to 10
−11.43 to 12.86
The average value of the N2O emission factor is 0.65 kg/TJ and the lower and upper limits are 0.58 and 0.73 kg/TJ, respectively, at a 95 % confidence interval. The uncertainty of the N2O emission factor is −11.43 % to +12.86 %.
The results of the non-CO2 concentration in exhaust gas revealed that the average emission concentration of CH4 and N2O was 1.78 and 0.53 ppm, while the emission factors of CH4 and N2O calculated from non-CO2 concentration analysis were 0.82 and 0.65 kg/TJ, respectively.
The CH4 emission factor was 18 % lower than the technology-specific emission factor suggested by the IPCC. However, it was within the emission factor range (0.3–3 kg/TJ) of the fuel-based LNG. In comparison with other countries, the emission factor of this study was 8 % higher than that of Japan’s GTCC power plant and about 22 % lower than the emission factor of GTCC power plant in Finland with a capacity of more than 5 MW. On the other hand, the N2O emission factor was much lower than the technology-specific N2O emission factor suggested by the IPCC for combined cycle power plant using LNG as an energy source. But it was more than six times higher than the N2O emission factor of the fuel-based LNG suggested by the IPCC. In Japan’s case, the N2O emission factor of a GTCC power plant was 0.54 kg/TJ, and the emission factor of our study was 20 % higher than that. Meanwhile, the N2O emission factor of a GTCC power plant in Finland was 54 % higher than that of our research. And the ranges of uncertainty for CH4 and N2O were between −12.96 and +13.89 %, and −11.43 and +12.86 % respectively, which is significantly lower than uncertainties presented by IPCC. These differences of emission characteristics and precision of emission factors show us that non-CO2 emissions mainly depend on combustion technology, and there is a visible need for establishing country-specific or technology-specific emission factors. And these factors may lead to set up more reliable national greenhouse gas inventory following bottom up approach.
In order to calculate the exact amount of greenhouse gas emissions and set highly reliable greenhouse gas abatement goals, researches on various fuel and energy consuming facilities is needed to develop country-specific emission factors. Furthermore, for Korea to lead international negotiations (such as the Climate Change Convention), research should continue to set up accurate country-specific emission factors, which are used as an indicator in comparing and assessing the amount of greenhouse gas emissions and reduction.
This work was supported by the Human Resources Development of the Korea Institute of Energy Technology Evaluation and Planning (KETEP) grant funded by the Korea government Ministry of Knowledge Economy (no. 20100092).
This article is distributed under the terms of the Creative Commons Attribution License which permits any use, distribution, and reproduction in any medium, provided the original author(s) and the source are credited.